Bravo
type: site
has tag: site
area: 78000
dis: Bravo
geo addr: 123 Some Rd, Fort Wayne, IN 46900
geo city: Fort Wayne
geo country: US
geo county: US
geo postal code: 46900
geo state: IN
geo street: 123 Some Rd
primary function: Hospital (General Medical & Surgical)
tz: Chicago
weather station ref: Fort Wayne, IN
year built: 2000
custom: {elecFreq:60Hz}
  elec freq: 60

Bravo BCU-1
type: thermostat
type: vav
has tag: chilledWaterCooling
has tag: equip
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
dis: Bravo BCU-1
site ref: Bravo
space ref: Bravo BCUs
custom: {tu, bcu}

Bravo BCU-1 Cooling Valve Output
type: cur-point
type: his-point
has tag: chilled
has tag: cool
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: valve
has tag: water
dis: Bravo BCU-1 Cooling Valve Output
equip ref: Bravo BCU-1
kind: Number
site ref: Bravo
space ref: Bravo BCUs
tz: Chicago
unit: %
custom: {predictionConf:0.31259757180034364, sourcePointName:ChwVlvOR_value, dataSyncRecovered:2020-07-10T01:00:10.249-04:00 New_York, inScope, backgroundPoint}
  prediction conf: 0.31259757180034364
  source point name: ChwVlvOR_value
  data sync recovered: 2020-07-10T01:00:10.249-04:00

Bravo BCU-1 Mixed Air Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: his
has tag: mixed
has tag: point
dis: Bravo BCU-1 Mixed Air Damper Output
equip ref: Bravo BCU-1
kind: Number
site ref: Bravo
space ref: Bravo BCUs
tz: Chicago
unit: %
custom: {predictionConf:0.28394372966813813, sourcePointName:MadOR_value, dataSyncRecovered:2020-07-10T01:00:09.879-04:00 New_York, inScope, backgroundPoint}
  prediction conf: 0.28394372966813813
  source point name: MadOR_value
  data sync recovered: 2020-07-10T01:00:09.879-04:00

Bravo BCU-1 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo BCU-1 Supply Air Temperature
equip ref: Bravo BCU-1
kind: Number
site ref: Bravo
space ref: Bravo BCUs
tz: Chicago
unit: °F
custom: {predictionConf:0.7893816782198223, sourcePointName:DAT, dataSyncRecovered:2020-07-10T01:00:09.879-04:00 New_York, inScope, backgroundPoint}
  prediction conf: 0.7893816782198223
  source point name: DAT
  data sync recovered: 2020-07-10T01:00:09.879-04:00

Bravo BCU-1 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo BCU-1 Zone Temperature
equip ref: Bravo BCU-1
kind: Number
site ref: Bravo
space ref: Bravo BCUs
tz: Chicago
unit: °F
custom: {predictionConf:0.6720981954640639, sourcePointName:SpaceTemp, dataSyncRecovered:2020-07-10T01:00:09.627-04:00 New_York, inScope, backgroundPoint}
  prediction conf: 0.6720981954640639
  source point name: SpaceTemp
  data sync recovered: 2020-07-10T01:00:09.627-04:00

Bravo BCU-1 Zone Temperature Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo BCU-1 Zone Temperature Setpoint
equip ref: Bravo BCU-1
kind: Number
max val: 327
min val: -273
site ref: Bravo
space ref: Bravo BCUs
tz: Chicago
unit: °F
custom: {precision:2, dataSyncRecovered:2020-07-10T01:00:11.125-04:00 New_York, backgroundPoint}
  precision: 2
  data sync recovered: 2020-07-10T01:00:11.125-04:00

Bravo BCU-2
type: thermostat
type: vav
has tag: chilledWaterCooling
has tag: equip
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
dis: Bravo BCU-2
site ref: Bravo
space ref: Bravo BCUs
custom: {tu, bcu}

Bravo BCU-2 Cooling Valve Output
type: cur-point
type: his-point
has tag: chilled
has tag: cool
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: valve
has tag: water
dis: Bravo BCU-2 Cooling Valve Output
equip ref: Bravo BCU-2
kind: Number
site ref: Bravo
space ref: Bravo BCUs
tz: Chicago
unit: %
custom: {sourcePointName:ChwVlvOR_value, dataSyncRecovered:2020-07-10T01:00:10.87-04:00 New_York, inScope, backgroundPoint}
  source point name: ChwVlvOR_value
  data sync recovered: 2020-07-10T01:00:10.87-04:00

Bravo BCU-2 Mixed Air Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: his
has tag: mixed
has tag: point
dis: Bravo BCU-2 Mixed Air Damper Output
equip ref: Bravo BCU-2
kind: Number
site ref: Bravo
space ref: Bravo BCUs
tz: Chicago
unit: %
custom: {sourcePointName:MadOR_value, dataSyncRecovered:2020-07-10T01:00:07.721-04:00 New_York, inScope, backgroundPoint}
  source point name: MadOR_value
  data sync recovered: 2020-07-10T01:00:07.721-04:00

Bravo BCU-2 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo BCU-2 Supply Air Temperature
equip ref: Bravo BCU-2
kind: Number
site ref: Bravo
space ref: Bravo BCUs
tz: Chicago
unit: °F
custom: {sourcePointName:DAT, dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, inScope, backgroundPoint}
  source point name: DAT
  data sync recovered: 2020-07-10T01:00:10.374-04:00

Bravo BCU-2 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo BCU-2 Zone Temperature
equip ref: Bravo BCU-2
kind: Number
site ref: Bravo
space ref: Bravo BCUs
tz: Chicago
unit: °F
custom: {sourcePointName:SpaceTemp, dataSyncRecovered:2020-07-10T01:00:07.598-04:00 New_York, inScope, backgroundPoint}
  source point name: SpaceTemp
  data sync recovered: 2020-07-10T01:00:07.598-04:00

Bravo BCU-2 Zone Temperature Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo BCU-2 Zone Temperature Setpoint
equip ref: Bravo BCU-2
kind: Number
max val: 327
min val: -273
site ref: Bravo
space ref: Bravo BCUs
tz: Chicago
unit: °F
custom: {precision:2, dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, backgroundPoint}
  precision: 2
  data sync recovered: 2020-07-10T01:00:10.374-04:00

Bravo BCUs
type: space
has tag: space
dis: Bravo BCUs
site ref: Bravo
custom: {equipType}

Bravo Boiler 1 Boiler Status
type: boiler
type: cur-point
type: his-point
has tag: boiler
has tag: cur
has tag: his
has tag: point
has tag: run
has tag: sensor
dis: Bravo Boiler 1 Boiler Status
equip ref: Bravo Boiler 1
  type: boiler
  has tag: boiler
  has tag: equip
  has tag: hvac
  dis: Bravo Boiler 1
  hot water ref: Bravo Boiler Plant
  site ref: Bravo
  space ref: Bravo HW System
  custom: {designSource:Drawings, designHotWaterPower:4200MMBTU/h, designMake:Bryan Boiler, designModel:RV-500W}
    design source: Drawings
    design hot water power: 4200
    design make: Bryan Boiler
    design model: RV-500W
kind: Bool
site ref: Bravo
space ref: Bravo HW System
tz: Chicago
custom: {sourcePointName:HwBlr1Sts, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
  source point name: HwBlr1Sts
  data sync recovered: 2020-07-10T01:00:10.745-04:00

Bravo Boiler 2 Boiler Status
type: boiler
type: cur-point
type: his-point
has tag: boiler
has tag: cur
has tag: his
has tag: point
has tag: run
has tag: sensor
dis: Bravo Boiler 2 Boiler Status
equip ref: Bravo Boiler 2
  type: boiler
  has tag: boiler
  has tag: equip
  has tag: hvac
  dis: Bravo Boiler 2
  hot water ref: Bravo Boiler Plant
  site ref: Bravo
  space ref: Bravo HW System
  custom: {designSource:Drawings, designHotWaterPower:4200MMBTU/h, designMake:Bryan Boiler, designModel:RV-500W}
    design source: Drawings
    design hot water power: 4200
    design make: Bryan Boiler
    design model: RV-500W
kind: Bool
site ref: Bravo
space ref: Bravo HW System
tz: Chicago
custom: {sourcePointName:HwBlr2Sts, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, inScope, backgroundPoint}
  source point name: HwBlr2Sts
  data sync recovered: 2020-07-10T01:00:10.62-04:00

Bravo Boiler Plant
type: hot-water-plant
has tag: equip
has tag: hot
has tag: hvac
has tag: plant
has tag: water
dis: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo HW System

Bravo Boiler Plant Domestic Hot Water Leaving Temperature Setpoint
type: cur-point
type: his-point
has tag: cur
has tag: domestic
has tag: his
has tag: hot
has tag: leaving
has tag: point
has tag: sp
has tag: temp
has tag: water
dis: Bravo Boiler Plant Domestic Hot Water Leaving Temperature Setpoint
equip ref: Bravo Boiler Plant
kind: Number
site ref: Bravo
space ref: Bravo HW System
tz: Chicago
unit: °F
custom: {sourcePointName:HwSp, dataSyncRecovered:2020-07-10T01:00:10.87-04:00 New_York, inScope, backgroundPoint}
  source point name: HwSp
  data sync recovered: 2020-07-10T01:00:10.87-04:00

Bravo Boiler Plant Heating Hot Water Differential Pressure Setpoint
type: cur-point
type: his-point
has tag: cur
has tag: delta
has tag: his
has tag: hot
has tag: point
has tag: pressure
has tag: sp
has tag: water
dis: Bravo Boiler Plant Heating Hot Water Differential Pressure Setpoint
equip ref: Bravo Boiler Plant
kind: Number
site ref: Bravo
space ref: Bravo HW System
tz: Chicago
unit: psi
custom: {sourcePointName:HWDifSP, dataSyncRecovered:2020-07-10T01:00:10.497-04:00 New_York, inScope, backgroundPoint}
  source point name: HWDifSP
  data sync recovered: 2020-07-10T01:00:10.497-04:00

Bravo Boiler Plant Heating Hot Water Return Temperature
type: cur-point
type: his-point
has tag: cur
has tag: heating
has tag: his
has tag: leaving
has tag: point
has tag: sensor
has tag: temp
has tag: water
dis: Bravo Boiler Plant Heating Hot Water Return Temperature
equip ref: Bravo Boiler Plant
kind: Number
site ref: Bravo
space ref: Bravo HW System
tz: Chicago
unit: °F
custom: {sourcePointName:HWRTEMP, dataSyncRecovered:2020-07-10T01:00:13.145-04:00 New_York, inScope, backgroundPoint}
  source point name: HWRTEMP
  data sync recovered: 2020-07-10T01:00:13.145-04:00

Bravo Boiler Plant Heating Hot Water Supply Temperature
type: cur-point
type: his-point
has tag: cur
has tag: his
has tag: hot
has tag: leaving
has tag: point
has tag: sensor
has tag: temp
has tag: water
dis: Bravo Boiler Plant Heating Hot Water Supply Temperature
equip ref: Bravo Boiler Plant
kind: Number
site ref: Bravo
space ref: Bravo HW System
tz: Chicago
unit: °F
custom: {sourcePointName:HWSTEMP, dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, inScope, backgroundPoint}
  source point name: HWSTEMP
  data sync recovered: 2020-07-10T01:00:10.374-04:00

Bravo CHW System
type: space
has tag: space
dis: Bravo CHW System
site ref: Bravo
custom: {equipType}

Bravo CHWP-1
type: equip
has tag: chilled
has tag: equip
has tag: hvac
has tag: pump
has tag: water
dis: Bravo CHWP-1
site ref: Bravo
space ref: Bravo CHW System

Bravo CHWP-1 Chilled Water Pump Enable
type: cur-point
type: his-point
has tag: chilled
has tag: cur
has tag: his
has tag: point
has tag: pump
has tag: sensor
has tag: water
dis: Bravo CHWP-1 Chilled Water Pump Enable
enum: Stop,Running
equip ref: Bravo CHWP-1
kind: Bool
site ref: Bravo
space ref: Bravo CHW System
tz: Chicago
custom: {poinTags:point and chilled and water and cmd and pump, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, backgroundPoint}
  poin tags: point and chilled and water and cmd and pump
  data sync recovered: 2020-07-10T01:00:10.62-04:00

Bravo CHWP-1 Chilled Water Pump VFD Speed
type: cur-point
type: his-point
has tag: chilled
has tag: cur
has tag: his
has tag: point
has tag: pump
has tag: sensor
has tag: speed
has tag: water
dis: Bravo CHWP-1 Chilled Water Pump VFD Speed
equip ref: Bravo CHWP-1
kind: Number
site ref: Bravo
space ref: Bravo CHW System
tz: Chicago
unit: %
custom: {dataSyncDownSince:2020-07-14T01:00:03.512-04:00 New_York, precision:2, dataSyncType:error, backgroundPoint}
  data sync down since: 2020-07-14T01:00:03.512-04:00
  precision: 2
  data sync type: error

Bravo CHWP-2
type: equip
has tag: chilled
has tag: equip
has tag: hvac
has tag: pump
has tag: water
dis: Bravo CHWP-2
site ref: Bravo
space ref: Bravo CHW System

Bravo CHWP-2 Chilled Water Pump Enable
type: cur-point
type: his-point
has tag: chilled
has tag: cur
has tag: his
has tag: point
has tag: pump
has tag: sensor
has tag: water
dis: Bravo CHWP-2 Chilled Water Pump Enable
enum: Stop,Running
equip ref: Bravo CHWP-2
kind: Bool
site ref: Bravo
space ref: Bravo CHW System
tz: Chicago
custom: {dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, backgroundPoint}
  data sync recovered: 2020-07-10T01:00:09.752-04:00

Bravo CHWP-2 Chilled Water Pump VFD Speed
type: cur-point
type: his-point
has tag: chilled
has tag: cur
has tag: his
has tag: point
has tag: pump
has tag: sensor
has tag: speed
has tag: water
dis: Bravo CHWP-2 Chilled Water Pump VFD Speed
equip ref: Bravo CHWP-2
kind: Number
site ref: Bravo
space ref: Bravo CHW System
tz: Chicago
unit: %
custom: {precision:2, dataSyncRecovered:2020-07-10T01:00:07.598-04:00 New_York, backgroundPoint}
  precision: 2
  data sync recovered: 2020-07-10T01:00:07.598-04:00

Bravo Chilled Water Plant
type: chilled-water-plant
has tag: chilled
has tag: equip
has tag: hvac
has tag: plant
has tag: water
dis: Bravo Chilled Water Plant
site ref: Bravo
space ref: Bravo CHW System

Bravo Chilled Water Plant AHU Cooling Enable
type: cur-point
type: his-point
has tag: cmd
has tag: cooling
has tag: cur
has tag: enable
has tag: his
has tag: point
dis: Bravo Chilled Water Plant AHU Cooling Enable
equip ref: Bravo Chilled Water Plant
kind: Bool
site ref: Bravo
space ref: Bravo CHW System
tz: Chicago
custom: {sourcePointName:AHUClgEnable, dataSyncRecovered:2020-07-10T01:00:11.125-04:00 New_York, backgroundPoint}
  source point name: AHUClgEnable
  data sync recovered: 2020-07-10T01:00:11.125-04:00

Bravo Chilled Water Plant AHU Heating Enable
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: enable
has tag: heating
has tag: his
has tag: point
dis: Bravo Chilled Water Plant AHU Heating Enable
equip ref: Bravo Chilled Water Plant
kind: Bool
site ref: Bravo
space ref: Bravo CHW System
tz: Chicago
custom: {sourcePointName:AHUHtgEnable, dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, backgroundPoint}
  source point name: AHUHtgEnable
  data sync recovered: 2020-07-10T01:00:10.374-04:00

Bravo Chilled Water Plant CV-1 Valve Signal (HHW)
type: cur-point
type: his-point
has tag: cur
has tag: his
has tag: hot
has tag: point
has tag: sensor
has tag: valve
has tag: water
dis: Bravo Chilled Water Plant CV-1 Valve Signal (HHW)
equip ref: Bravo Chilled Water Plant
kind: Number
max val: 100
min val: 0
site ref: Bravo
space ref: Bravo CHW System
tz: Chicago
unit: %
custom: {precision:2, dataSyncRecovered:2020-07-10T01:00:10.995-04:00 New_York, backgroundPoint}
  precision: 2
  data sync recovered: 2020-07-10T01:00:10.995-04:00

Bravo Chilled Water Plant CV-2 Valve Signal (Bypass Valve)
type: cur-point
type: his-point
has tag: bypass
has tag: chilled
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: valve
has tag: water
dis: Bravo Chilled Water Plant CV-2 Valve Signal (Bypass Valve)
equip ref: Bravo Chilled Water Plant
kind: Number
max val: 100
min val: 0
site ref: Bravo
space ref: Bravo CHW System
tz: Chicago
unit: %
custom: {precision:2, dataSyncRecovered:2020-07-10T01:00:10.126-04:00 New_York, signal, backgroundPoint}
  precision: 2
  data sync recovered: 2020-07-10T01:00:10.126-04:00

Bravo Chilled Water Plant CV-3 Valve Signal
type: cur-point
type: his-point
has tag: chilled
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: valve
has tag: water
dis: Bravo Chilled Water Plant CV-3 Valve Signal
equip ref: Bravo Chilled Water Plant
kind: Number
max val: 100
min val: 0
site ref: Bravo
space ref: Bravo CHW System
tz: Chicago
unit: %
custom: {precision:0, dataSyncRecovered:2020-07-10T01:00:07.473-04:00 New_York, signal, backgroundPoint}
  precision: 0
  data sync recovered: 2020-07-10T01:00:07.473-04:00

Bravo Chilled Water Plant CV-4 Valve Signal
type: cur-point
type: his-point
has tag: chilled
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: valve
has tag: water
dis: Bravo Chilled Water Plant CV-4 Valve Signal
equip ref: Bravo Chilled Water Plant
kind: Number
max val: 100
min val: 0
site ref: Bravo
space ref: Bravo CHW System
tz: Chicago
unit: %
custom: {precision:0, dataSyncRecovered:2020-07-10T01:00:10.126-04:00 New_York, signal, backgroundPoint}
  precision: 0
  data sync recovered: 2020-07-10T01:00:10.126-04:00

Bravo Chilled Water Plant Chilled Water Differential Pressure
type: cur-point
type: his-point
has tag: chilled
has tag: cur
has tag: delta
has tag: his
has tag: point
has tag: pressure
has tag: sensor
has tag: water
dis: Bravo Chilled Water Plant Chilled Water Differential Pressure
equip ref: Bravo Chilled Water Plant
kind: Number
site ref: Bravo
space ref: Bravo CHW System
tz: Chicago
unit: psi
custom: {precision:2, dataSyncRecovered:2020-07-10T01:00:10.249-04:00 New_York, pointType:, backgroundPoint}
  precision: 2
  data sync recovered: 2020-07-10T01:00:10.249-04:00

Bravo Chilled Water Plant Chilled Water Differential Pressure Setpoint
type: cur-point
type: his-point
has tag: chilled
has tag: cur
has tag: delta
has tag: his
has tag: primaryLoop
has tag: point
has tag: pressure
has tag: sensor
has tag: water
dis: Bravo Chilled Water Plant Chilled Water Differential Pressure Setpoint
equip ref: Bravo Chilled Water Plant
kind: Number
site ref: Bravo
space ref: Bravo CHW System
tz: Chicago
unit: psi
custom: {predictionConf:0.3397244142906628, sourcePointName:ChwDifSP, dataSyncRecovered:2020-07-10T01:00:09.627-04:00 New_York, inScope, backgroundPoint}
  prediction conf: 0.3397244142906628
  source point name: ChwDifSP
  data sync recovered: 2020-07-10T01:00:09.627-04:00

Bravo Chilled Water Plant Chilled Water Entering Temperature
type: cur-point
type: his-point
has tag: chilled
has tag: cur
has tag: entering
has tag: his
has tag: primaryLoop
has tag: point
has tag: sensor
has tag: temp
has tag: water
dis: Bravo Chilled Water Plant Chilled Water Entering Temperature
equip ref: Bravo Chilled Water Plant
kind: Number
site ref: Bravo
space ref: Bravo CHW System
tz: Chicago
unit: °F
custom: {predictionConf:0.787900067809321, sourcePointName:CHWRTEMP, dataSyncRecovered:2020-07-10T01:00:10.497-04:00 New_York, inScope, backgroundPoint}
  prediction conf: 0.787900067809321
  source point name: CHWRTEMP
  data sync recovered: 2020-07-10T01:00:10.497-04:00

Bravo Chilled Water Plant Chilled Water Leaving Temperature
type: cur-point
type: his-point
has tag: chilled
has tag: cur
has tag: his
has tag: leaving
has tag: primaryLoop
has tag: point
has tag: sensor
has tag: temp
has tag: water
dis: Bravo Chilled Water Plant Chilled Water Leaving Temperature
equip ref: Bravo Chilled Water Plant
kind: Number
site ref: Bravo
space ref: Bravo CHW System
tz: Chicago
unit: °F
custom: {predictionConf:0.787900067809321, sourcePointName:ChwsTemp, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
  prediction conf: 0.787900067809321
  source point name: ChwsTemp
  data sync recovered: 2020-07-10T01:00:10.003-04:00

Bravo Chilled Water Plant Chilled Water dT (Auto-computed)
type: his-point
has tag: his
has tag: point
has tag: sp
dis: Bravo Chilled Water Plant Chilled Water dT (Auto-computed)
equip ref: Bravo Chilled Water Plant
kind: Number
site ref: Bravo
space ref: Bravo CHW System
tz: Chicago
custom: {cache, dataSyncDownSince:2020-03-12T01:00:04.793-04:00 New_York, dataSyncType:error, backgroundPoint}
  data sync down since: 2020-03-12T01:00:04.793-04:00
  data sync type: error

Bravo Chilled Water Plant Chiller Status
type: chiller
type: cur-point
type: his-point
has tag: chiller
has tag: cur
has tag: his
has tag: point
has tag: run
has tag: sensor
dis: Bravo Chilled Water Plant Chiller Status
equip ref: Bravo Chilled Water Plant
kind: Bool
site ref: Bravo
space ref: Bravo CHW System
tz: Chicago
custom: {predictionConf:0.15013386549340826, sourcePointName:RunSTATUS, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
  prediction conf: 0.15013386549340826
  source point name: RunSTATUS
  data sync recovered: 2020-07-10T01:00:10.003-04:00

Bravo Chilled Water Plant Efficiency (Auto-computed)
type: his-point
has tag: his
has tag: point
has tag: sp
dis: Bravo Chilled Water Plant Efficiency (Auto-computed)
equip ref: Bravo Chilled Water Plant
kind: Number
site ref: Bravo
space ref: Bravo CHW System
tz: Chicago
unit: kW/ton
custom: {cache, dataSyncRecovered:2020-07-14T01:00:05.167-04:00 New_York, backgroundPoint}
  data sync recovered: 2020-07-14T01:00:05.167-04:00

Bravo Chiller 1
type: chiller
has tag: airCooling
has tag: chiller
has tag: equip
has tag: hvac
chilled water ref: Bravo Chilled Water Plant
dis: Bravo Chiller 1
site ref: Bravo
space ref: Bravo CHW System
custom:
  label: {designElecPower:180kW, designEfficiency:10.6EER, designSource:Drawings, designChilledWaterPower:160tonref, designChilledWaterLeavingTemp:44°F, designMake:Mcquay, designChilledWaterEnteringTemp:58°F, designChilledWaterDeltaPressure:18.61psi, designModel:AGS-160C, designChilledWaterFlow:275gal/min}
  design elec power: 180
  design efficiency: 10.6
  design source: Drawings
  design chilled water power: 160
  design chilled water leaving temp: 44
  design make: Mcquay
  design chilled water entering temp: 58
  design chilled water delta pressure: 18.61
  design model: AGS-160C
  design chilled water flow: 275

Bravo Chiller 1 Chilled Water Entering Temperature
type: cur-point
type: his-point
has tag: chilled
has tag: cur
has tag: entering
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: water
dis: Bravo Chiller 1 Chilled Water Entering Temperature
equip ref: Bravo Chiller 1
kind: Number
site ref: Bravo
space ref: Bravo CHW System
tz: Chicago
unit: °F
custom: {predictionConf:0.38428817764444545, sourcePointName:CH1_EntChwTemp, dataSyncRecovered:2020-07-10T01:00:10.87-04:00 New_York, inScope, backgroundPoint}
  prediction conf: 0.38428817764444545
  source point name: CH1_EntChwTemp
  data sync recovered: 2020-07-10T01:00:10.87-04:00

Bravo Chiller 1 Chilled Water Leaving Temperature
type: cur-point
type: his-point
has tag: chilled
has tag: cur
has tag: his
has tag: leaving
has tag: point
has tag: sensor
has tag: temp
has tag: water
dis: Bravo Chiller 1 Chilled Water Leaving Temperature
equip ref: Bravo Chiller 1
kind: Number
site ref: Bravo
space ref: Bravo CHW System
tz: Chicago
unit: °F
custom: {predictionConf:0.34916172794461753, sourcePointName:CH1_LeavChwTemp, dataSyncRecovered:2020-07-10T01:00:09.879-04:00 New_York, inScope, backgroundPoint}
  prediction conf: 0.34916172794461753
  source point name: CH1_LeavChwTemp
  data sync recovered: 2020-07-10T01:00:09.879-04:00

Bravo Chiller 1 Chilled Water dT (Auto-computed)
type: his-point
has tag: his
has tag: point
has tag: sp
dis: Bravo Chiller 1 Chilled Water dT (Auto-computed)
equip ref: Bravo Chiller 1
kind: Number
site ref: Bravo
space ref: Bravo CHW System
tz: Chicago
custom: {cache, dataSyncDownSince:2020-03-12T01:00:04.793-04:00 New_York, dataSyncType:error, backgroundPoint}
  data sync down since: 2020-03-12T01:00:04.793-04:00
  data sync type: error

Bravo Chiller 1 Chiller 1 Setpoint
type: chiller
type: cur-point
type: his-point
has tag: chilled
has tag: chiller
has tag: cur
has tag: his
has tag: leaving
has tag: point
has tag: sp
has tag: temp
has tag: water
dis: Bravo Chiller 1 Chiller 1 Setpoint
equip ref: Bravo Chiller 1
kind: Number
site ref: Bravo
space ref: Bravo CHW System
tz: Chicago
unit: °F
custom: {predictionConf:0.42372423437084655, sourcePointName:CH1_CHW_SP, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, pointType:, inScope, backgroundPoint}
  prediction conf: 0.42372423437084655
  source point name: CH1_CHW_SP
  data sync recovered: 2020-07-10T01:00:10.003-04:00

Bravo Chiller 1 Chiller Act. Capacity
type: chiller
type: cur-point
type: his-point
has tag: chiller
has tag: cur
has tag: his
has tag: point
has tag: sensor
dis: Bravo Chiller 1 Chiller Act. Capacity
equip ref: Bravo Chiller 1
kind: Number
site ref: Bravo
space ref: Bravo CHW System
tz: Chicago
unit: %
custom: {act, precision:2, dataSyncRecovered:2020-07-10T01:00:10.995-04:00 New_York, backgroundPoint, capacity}
  precision: 2
  data sync recovered: 2020-07-10T01:00:10.995-04:00

Bravo Chiller 1 Chiller Enable
type: chiller
type: cur-point
type: his-point
has tag: chiller
has tag: cmd
has tag: cur
has tag: his
has tag: point
has tag: run
dis: Bravo Chiller 1 Chiller Enable
equip ref: Bravo Chiller 1
kind: Bool
site ref: Bravo
space ref: Bravo CHW System
tz: Chicago
custom: {predictionConf:0.2769995097894551, sourcePointName:CH1_Clr1Cmd, dataSyncRecovered:2020-07-10T01:00:10.87-04:00 New_York, inScope, backgroundPoint}
  prediction conf: 0.2769995097894551
  source point name: CH1_Clr1Cmd
  data sync recovered: 2020-07-10T01:00:10.87-04:00

Bravo Chiller 1 Chiller Status
type: chiller
type: cur-point
type: his-point
has tag: chiller
has tag: cur
has tag: his
has tag: point
has tag: run
has tag: sensor
dis: Bravo Chiller 1 Chiller Status
equip ref: Bravo Chiller 1
kind: Bool
site ref: Bravo
space ref: Bravo CHW System
tz: Chicago
custom: {predictionConf:0.33026119584467384, sourcePointName:CH1_ChlrSts, dataSyncRecovered:2020-07-10T01:00:10.995-04:00 New_York, inScope, backgroundPoint}
  prediction conf: 0.33026119584467384
  source point name: CH1_ChlrSts
  data sync recovered: 2020-07-10T01:00:10.995-04:00

Bravo Chiller 2
type: chiller
has tag: airCooling
has tag: chiller
has tag: equip
has tag: hvac
chilled water ref: Bravo Chilled Water Plant
dis: Bravo Chiller 2
site ref: Bravo
space ref: Bravo CHW System
custom:
  label: {designElecPower:180kW, designEfficiency:10.6EER, designSource:Drawings, designChilledWaterPower:160tonref, designChilledWaterLeavingTemp:44°F, designMake:Mcquay, designChilledWaterEnteringTemp:58°F, designChilledWaterDeltaPressure:18.61psi, designModel:AGS-160C, designChilledWaterFlow:275gal/min}
  design elec power: 180
  design efficiency: 10.6
  design source: Drawings
  design chilled water power: 160
  design chilled water leaving temp: 44
  design make: Mcquay
  design chilled water entering temp: 58
  design chilled water delta pressure: 18.61
  design model: AGS-160C
  design chilled water flow: 275

Bravo Chiller 2 Chilled Water Entering Temperature
type: cur-point
type: his-point
has tag: chilled
has tag: cur
has tag: entering
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: water
dis: Bravo Chiller 2 Chilled Water Entering Temperature
equip ref: Bravo Chiller 2
kind: Number
site ref: Bravo
space ref: Bravo CHW System
tz: Chicago
unit: °F
custom: {predictionConf:0.38428817764444545, sourcePointName:CH2_EntChwTemp, dataSyncRecovered:2020-07-10T01:00:10.497-04:00 New_York, inScope, backgroundPoint}
  prediction conf: 0.38428817764444545
  source point name: CH2_EntChwTemp
  data sync recovered: 2020-07-10T01:00:10.497-04:00

Bravo Chiller 2 Chilled Water Leaving Temperature
type: cur-point
type: his-point
has tag: chilled
has tag: cur
has tag: his
has tag: leaving
has tag: point
has tag: sensor
has tag: temp
has tag: water
dis: Bravo Chiller 2 Chilled Water Leaving Temperature
equip ref: Bravo Chiller 2
kind: Number
site ref: Bravo
space ref: Bravo CHW System
tz: Chicago
unit: °F
custom: {predictionConf:0.34916172794461753, sourcePointName:CH2_LeavChwTemp, dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, inScope, backgroundPoint}
  prediction conf: 0.34916172794461753
  source point name: CH2_LeavChwTemp
  data sync recovered: 2020-07-10T01:00:09.752-04:00

Bravo Chiller 2 Chilled Water dT (Auto-computed)
type: his-point
has tag: his
has tag: point
has tag: sp
dis: Bravo Chiller 2 Chilled Water dT (Auto-computed)
equip ref: Bravo Chiller 2
kind: Number
site ref: Bravo
space ref: Bravo CHW System
tz: Chicago
custom: {cache, dataSyncDownSince:2020-03-12T01:00:04.793-04:00 New_York, dataSyncType:error, backgroundPoint}
  data sync down since: 2020-03-12T01:00:04.793-04:00
  data sync type: error

Bravo Chiller 2 Chiller 2 Setpoint
type: chiller
type: cur-point
type: his-point
has tag: chilled
has tag: chiller
has tag: cur
has tag: his
has tag: leaving
has tag: point
has tag: sp
has tag: temp
has tag: water
dis: Bravo Chiller 2 Chiller 2 Setpoint
equip ref: Bravo Chiller 2
kind: Number
site ref: Bravo
space ref: Bravo CHW System
tz: Chicago
unit: °F
custom: {predictionConf:0.42372423437084655, sourcePointName:CH2_CHW_SP, dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, pointType:, inScope, backgroundPoint}
  prediction conf: 0.42372423437084655
  source point name: CH2_CHW_SP
  data sync recovered: 2020-07-10T01:00:10.374-04:00

Bravo Chiller 2 Chiller Act. Capacity
type: chiller
type: cur-point
type: his-point
has tag: chiller
has tag: cur
has tag: his
has tag: point
has tag: sensor
dis: Bravo Chiller 2 Chiller Act. Capacity
equip ref: Bravo Chiller 2
kind: Number
site ref: Bravo
space ref: Bravo CHW System
tz: Chicago
unit: %
custom: {act, precision:2, dataSyncRecovered:2020-07-10T01:00:09.627-04:00 New_York, backgroundPoint, capacity}
  precision: 2
  data sync recovered: 2020-07-10T01:00:09.627-04:00

Bravo Chiller 2 Chiller Enable
type: chiller
type: cur-point
type: his-point
has tag: chiller
has tag: cmd
has tag: cur
has tag: his
has tag: point
has tag: run
dis: Bravo Chiller 2 Chiller Enable
equip ref: Bravo Chiller 2
kind: Bool
site ref: Bravo
space ref: Bravo CHW System
tz: Chicago
custom: {predictionConf:0.2769995097894551, sourcePointName:CH2_Clr1Cmd, dataSyncRecovered:2020-07-10T01:00:11.258-04:00 New_York, inScope, backgroundPoint}
  prediction conf: 0.2769995097894551
  source point name: CH2_Clr1Cmd
  data sync recovered: 2020-07-10T01:00:11.258-04:00

Bravo Chiller 2 Chiller Status
type: chiller
type: cur-point
type: his-point
has tag: chiller
has tag: cur
has tag: his
has tag: point
has tag: run
has tag: sensor
dis: Bravo Chiller 2 Chiller Status
equip ref: Bravo Chiller 2
kind: Bool
site ref: Bravo
space ref: Bravo CHW System
tz: Chicago
custom: {predictionConf:0.33026119584467384, sourcePointName:CH2_ChlrSts, dataSyncRecovered:2020-07-14T01:00:05.167-04:00 New_York, inScope, backgroundPoint}
  prediction conf: 0.33026119584467384
  source point name: CH2_ChlrSts
  data sync recovered: 2020-07-14T01:00:05.167-04:00

Bravo EF-1
type: equip
has tag: equip
has tag: fan
has tag: hvac
dis: Bravo EF-1
site ref: Bravo
space ref: Bravo Fans

Bravo EF-1 Exhaust Fan Enable
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: enable
has tag: exhaust
has tag: fan
has tag: his
has tag: point
dis: Bravo EF-1 Exhaust Fan Enable
equip ref: Bravo EF-1
kind: Bool
site ref: Bravo
space ref: Bravo Fans
tz: Chicago
custom: {sourcePointName:EFSS, dataSyncRecovered:2020-07-10T01:00:10.995-04:00 New_York, inScope, backgroundPoint}
  source point name: EFSS
  data sync recovered: 2020-07-10T01:00:10.995-04:00

Bravo EF-1 Exhaust Fan Status
type: cur-point
type: his-point
has tag: cur
has tag: exhaust
has tag: fan
has tag: his
has tag: point
has tag: run
has tag: sensor
dis: Bravo EF-1 Exhaust Fan Status
equip ref: Bravo EF-1
kind: Bool
site ref: Bravo
space ref: Bravo Fans
tz: Chicago
custom: {dataSyncDownSince:2020-03-11T13:56:25.929-04:00 New_York, sourcePointName:EFStatus, dataSyncType:error, pointType:, inScope, backgroundPoint}
  data sync down since: 2020-03-11T13:56:25.929-04:00
  source point name: EFStatus
  data sync type: error

Bravo EF-10
type: equip
has tag: equip
has tag: fan
has tag: hvac
dis: Bravo EF-10
site ref: Bravo
space ref: Bravo Fans

Bravo EF-10 Exhaust Fan Enable
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: enable
has tag: exhaust
has tag: fan
has tag: his
has tag: point
dis: Bravo EF-10 Exhaust Fan Enable
equip ref: Bravo EF-10
kind: Bool
site ref: Bravo
space ref: Bravo Fans
tz: Chicago
custom: {sourcePointName:EFSS, dataSyncRecovered:2020-07-10T01:00:13.145-04:00 New_York, inScope, backgroundPoint}
  source point name: EFSS
  data sync recovered: 2020-07-10T01:00:13.145-04:00

Bravo EF-10 Exhaust Fan Status
type: cur-point
type: his-point
has tag: cur
has tag: exhaust
has tag: fan
has tag: his
has tag: point
has tag: run
has tag: sensor
dis: Bravo EF-10 Exhaust Fan Status
equip ref: Bravo EF-10
kind: Bool
site ref: Bravo
space ref: Bravo Fans
tz: Chicago
custom: {dataSyncDownSince:2020-06-23T01:00:04.326-04:00 New_York, sourcePointName:EFStatus, dataSyncType:error, inScope, backgroundPoint}
  data sync down since: 2020-06-23T01:00:04.326-04:00
  source point name: EFStatus
  data sync type: error

Bravo EF-11
type: equip
has tag: equip
has tag: fan
has tag: hvac
dis: Bravo EF-11
site ref: Bravo
space ref: Bravo Fans

Bravo EF-11 Exhaust Fan Enable
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: enable
has tag: exhaust
has tag: fan
has tag: his
has tag: point
dis: Bravo EF-11 Exhaust Fan Enable
equip ref: Bravo EF-11
kind: Bool
site ref: Bravo
space ref: Bravo Fans
tz: Chicago
custom: {sourcePointName:EFSS, dataSyncRecovered:2020-07-10T01:00:11.258-04:00 New_York, inScope, backgroundPoint}
  source point name: EFSS
  data sync recovered: 2020-07-10T01:00:11.258-04:00

Bravo EF-11 Exhaust Fan Status
type: cur-point
type: his-point
has tag: cur
has tag: exhaust
has tag: fan
has tag: his
has tag: point
has tag: run
has tag: sensor
dis: Bravo EF-11 Exhaust Fan Status
equip ref: Bravo EF-11
kind: Bool
site ref: Bravo
space ref: Bravo Fans
tz: Chicago
custom: {dataSyncDownSince:2020-03-11T13:56:25.945-04:00 New_York, sourcePointName:EFStatus, dataSyncType:error, inScope, backgroundPoint}
  data sync down since: 2020-03-11T13:56:25.945-04:00
  source point name: EFStatus
  data sync type: error

Bravo EF-12
type: equip
has tag: equip
has tag: fan
has tag: hvac
dis: Bravo EF-12
site ref: Bravo
space ref: Bravo Fans

Bravo EF-12 Exhaust Fan Enable
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: enable
has tag: exhaust
has tag: fan
has tag: his
has tag: point
dis: Bravo EF-12 Exhaust Fan Enable
equip ref: Bravo EF-12
kind: Bool
site ref: Bravo
space ref: Bravo Fans
tz: Chicago
custom: {sourcePointName:EFSS, dataSyncRecovered:2020-07-10T01:00:07.473-04:00 New_York, inScope, backgroundPoint}
  source point name: EFSS
  data sync recovered: 2020-07-10T01:00:07.473-04:00

Bravo EF-12 Exhaust Fan Status
type: cur-point
type: his-point
has tag: cur
has tag: exhaust
has tag: fan
has tag: his
has tag: point
has tag: run
has tag: sensor
dis: Bravo EF-12 Exhaust Fan Status
equip ref: Bravo EF-12
kind: Bool
site ref: Bravo
space ref: Bravo Fans
tz: Chicago
custom: {dataSyncDownSince:2020-03-11T13:56:25.929-04:00 New_York, sourcePointName:EFStatus, dataSyncType:error, inScope, backgroundPoint}
  data sync down since: 2020-03-11T13:56:25.929-04:00
  source point name: EFStatus
  data sync type: error

Bravo EF-13
type: equip
has tag: equip
has tag: fan
has tag: hvac
dis: Bravo EF-13
site ref: Bravo
space ref: Bravo Fans

Bravo EF-13 Exhaust Fan Enable
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: enable
has tag: exhaust
has tag: fan
has tag: his
has tag: point
dis: Bravo EF-13 Exhaust Fan Enable
equip ref: Bravo EF-13
kind: Bool
site ref: Bravo
space ref: Bravo Fans
tz: Chicago
custom: {sourcePointName:EFSS, dataSyncRecovered:2020-07-10T01:00:10.497-04:00 New_York, inScope, backgroundPoint}
  source point name: EFSS
  data sync recovered: 2020-07-10T01:00:10.497-04:00

Bravo EF-13 Exhaust Fan Status
type: cur-point
type: his-point
has tag: cur
has tag: exhaust
has tag: fan
has tag: his
has tag: point
has tag: run
has tag: sensor
dis: Bravo EF-13 Exhaust Fan Status
equip ref: Bravo EF-13
kind: Bool
site ref: Bravo
space ref: Bravo Fans
tz: Chicago
custom: {dataSyncDownSince:2020-03-11T13:56:25.929-04:00 New_York, sourcePointName:EFStatus, dataSyncType:error, inScope, backgroundPoint}
  data sync down since: 2020-03-11T13:56:25.929-04:00
  source point name: EFStatus
  data sync type: error

Bravo EF-14
type: equip
has tag: equip
has tag: fan
has tag: hvac
dis: Bravo EF-14
site ref: Bravo
space ref: Bravo Fans

Bravo EF-14 Exhaust Fan Enable
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: enable
has tag: exhaust
has tag: fan
has tag: his
has tag: point
dis: Bravo EF-14 Exhaust Fan Enable
equip ref: Bravo EF-14
kind: Bool
site ref: Bravo
space ref: Bravo Fans
tz: Chicago
custom: {sourcePointName:EFSS, dataSyncRecovered:2020-07-10T01:00:10.497-04:00 New_York, inScope, backgroundPoint}
  source point name: EFSS
  data sync recovered: 2020-07-10T01:00:10.497-04:00

Bravo EF-14 Exhaust Fan Status
type: cur-point
type: his-point
has tag: cur
has tag: exhaust
has tag: fan
has tag: his
has tag: point
has tag: run
has tag: sensor
dis: Bravo EF-14 Exhaust Fan Status
equip ref: Bravo EF-14
kind: Bool
site ref: Bravo
space ref: Bravo Fans
tz: Chicago
custom: {dataSyncDownSince:2020-03-11T13:56:25.929-04:00 New_York, sourcePointName:EFStatus, dataSyncType:error, inScope, backgroundPoint}
  data sync down since: 2020-03-11T13:56:25.929-04:00
  source point name: EFStatus
  data sync type: error

Bravo EF-15
type: equip
has tag: equip
has tag: fan
has tag: hvac
dis: Bravo EF-15
site ref: Bravo
space ref: Bravo Fans

Bravo EF-15 Exhaust Fan Enable
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: enable
has tag: exhaust
has tag: fan
has tag: his
has tag: point
dis: Bravo EF-15 Exhaust Fan Enable
equip ref: Bravo EF-15
kind: Bool
site ref: Bravo
space ref: Bravo Fans
tz: Chicago
custom: {sourcePointName:EFSS, dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, inScope, backgroundPoint}
  source point name: EFSS
  data sync recovered: 2020-07-10T01:00:09.752-04:00

Bravo EF-15 Exhaust Fan Status
type: cur-point
type: his-point
has tag: cur
has tag: exhaust
has tag: fan
has tag: his
has tag: point
has tag: run
has tag: sensor
dis: Bravo EF-15 Exhaust Fan Status
equip ref: Bravo EF-15
kind: Bool
site ref: Bravo
space ref: Bravo Fans
tz: Chicago
custom: {dataSyncDownSince:2020-03-11T13:56:25.929-04:00 New_York, sourcePointName:EFStatus, dataSyncType:error, inScope, backgroundPoint}
  data sync down since: 2020-03-11T13:56:25.929-04:00
  source point name: EFStatus
  data sync type: error

Bravo EF-16
type: equip
has tag: equip
has tag: fan
has tag: hvac
dis: Bravo EF-16
site ref: Bravo
space ref: Bravo Fans

Bravo EF-16 Exhaust Fan Enable
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: enable
has tag: exhaust
has tag: fan
has tag: his
has tag: point
dis: Bravo EF-16 Exhaust Fan Enable
equip ref: Bravo EF-16
kind: Bool
site ref: Bravo
space ref: Bravo Fans
tz: Chicago
custom: {sourcePointName:EFSS, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
  source point name: EFSS
  data sync recovered: 2020-07-10T01:00:10.003-04:00

Bravo EF-16 Exhaust Fan Status
type: cur-point
type: his-point
has tag: cur
has tag: exhaust
has tag: fan
has tag: his
has tag: point
has tag: run
has tag: sensor
dis: Bravo EF-16 Exhaust Fan Status
equip ref: Bravo EF-16
kind: Bool
site ref: Bravo
space ref: Bravo Fans
tz: Chicago
custom: {dataSyncDownSince:2020-03-11T13:56:25.929-04:00 New_York, sourcePointName:EFStatus, dataSyncType:error, inScope, backgroundPoint}
  data sync down since: 2020-03-11T13:56:25.929-04:00
  source point name: EFStatus
  data sync type: error

Bravo EF-17
type: equip
has tag: equip
has tag: fan
has tag: hvac
dis: Bravo EF-17
site ref: Bravo
space ref: Bravo Fans

Bravo EF-17 Exhaust Fan Enable
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: enable
has tag: exhaust
has tag: fan
has tag: his
has tag: point
dis: Bravo EF-17 Exhaust Fan Enable
equip ref: Bravo EF-17
kind: Bool
site ref: Bravo
space ref: Bravo Fans
tz: Chicago
custom: {sourcePointName:EFSS, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
  source point name: EFSS
  data sync recovered: 2020-07-10T01:00:10.745-04:00

Bravo EF-17 Exhaust Fan Status
type: cur-point
type: his-point
has tag: cur
has tag: exhaust
has tag: fan
has tag: his
has tag: point
has tag: run
has tag: sensor
dis: Bravo EF-17 Exhaust Fan Status
equip ref: Bravo EF-17
kind: Bool
site ref: Bravo
space ref: Bravo Fans
tz: Chicago
custom: {dataSyncDownSince:2020-03-11T13:56:25.945-04:00 New_York, sourcePointName:EFStatus, dataSyncType:error, inScope, backgroundPoint}
  data sync down since: 2020-03-11T13:56:25.945-04:00
  source point name: EFStatus
  data sync type: error

Bravo EF-18
type: equip
has tag: equip
has tag: fan
has tag: hvac
dis: Bravo EF-18
site ref: Bravo
space ref: Bravo Fans

Bravo EF-18 Exhaust Fan Enable
type: cur-point
type: his-point
has tag: cur
has tag: enable
has tag: exhaust
has tag: fan
has tag: his
has tag: point
has tag: sensor
dis: Bravo EF-18 Exhaust Fan Enable
enum: STOP,On
equip ref: Bravo EF-18
kind: Bool
site ref: Bravo
space ref: Bravo Fans
tz: Chicago
custom: {dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, backgroundPoint}
  data sync recovered: 2020-07-10T01:00:10.745-04:00

Bravo EF-18 Exhaust Fan Status
type: cur-point
type: his-point
has tag: cur
has tag: exhaust
has tag: fan
has tag: his
has tag: point
has tag: run
has tag: sensor
dis: Bravo EF-18 Exhaust Fan Status
enum: stateNul,Off,RUNNING
equip ref: Bravo EF-18
kind: Str
site ref: Bravo
space ref: Bravo Fans
tz: Chicago
custom: {dataSyncRecovered:2020-07-10T01:00:10.497-04:00 New_York, backgroundPoint}
  data sync recovered: 2020-07-10T01:00:10.497-04:00

Bravo EF-19
type: equip
has tag: equip
has tag: fan
has tag: hvac
dis: Bravo EF-19
site ref: Bravo
space ref: Bravo Fans

Bravo EF-19 Exhaust Fan Enable
type: cur-point
type: his-point
has tag: cur
has tag: enable
has tag: exhaust
has tag: fan
has tag: his
has tag: point
has tag: sensor
dis: Bravo EF-19 Exhaust Fan Enable
enum: STOP,On
equip ref: Bravo EF-19
kind: Bool
site ref: Bravo
space ref: Bravo Fans
tz: Chicago
custom: {dataSyncRecovered:2020-07-10T01:00:13.145-04:00 New_York, backgroundPoint}
  data sync recovered: 2020-07-10T01:00:13.145-04:00

Bravo EF-19 Exhaust Fan Status
type: cur-point
type: his-point
has tag: cur
has tag: exhaust
has tag: fan
has tag: his
has tag: point
has tag: run
has tag: sensor
dis: Bravo EF-19 Exhaust Fan Status
enum: stateNul,Off,RUNNING
equip ref: Bravo EF-19
kind: Str
site ref: Bravo
space ref: Bravo Fans
tz: Chicago
custom: {dataSyncRecovered:2020-07-10T01:00:07.598-04:00 New_York, backgroundPoint}
  data sync recovered: 2020-07-10T01:00:07.598-04:00

Bravo EF-2
type: equip
has tag: equip
has tag: fan
has tag: hvac
dis: Bravo EF-2
site ref: Bravo
space ref: Bravo Fans

Bravo EF-2 Exhaust Fan Enable
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: enable
has tag: exhaust
has tag: fan
has tag: his
has tag: point
dis: Bravo EF-2 Exhaust Fan Enable
equip ref: Bravo EF-2
kind: Bool
site ref: Bravo
space ref: Bravo Fans
tz: Chicago
custom: {sourcePointName:EFSS, dataSyncRecovered:2020-07-10T01:00:09.627-04:00 New_York, inScope, backgroundPoint}
  source point name: EFSS
  data sync recovered: 2020-07-10T01:00:09.627-04:00

Bravo EF-2 Exhaust Fan Status
type: cur-point
type: his-point
has tag: cur
has tag: exhaust
has tag: fan
has tag: his
has tag: point
has tag: run
has tag: sensor
dis: Bravo EF-2 Exhaust Fan Status
equip ref: Bravo EF-2
kind: Bool
site ref: Bravo
space ref: Bravo Fans
tz: Chicago
custom: {dataSyncDownSince:2020-03-11T13:56:25.945-04:00 New_York, sourcePointName:EFStatus, dataSyncType:error, inScope, backgroundPoint}
  data sync down since: 2020-03-11T13:56:25.945-04:00
  source point name: EFStatus
  data sync type: error

Bravo EF-20
type: equip
has tag: equip
has tag: fan
has tag: hvac
dis: Bravo EF-20
site ref: Bravo
space ref: Bravo Fans

Bravo EF-20 Exhaust Fan Enable
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: enable
has tag: exhaust
has tag: fan
has tag: his
has tag: point
dis: Bravo EF-20 Exhaust Fan Enable
equip ref: Bravo EF-20
kind: Bool
site ref: Bravo
space ref: Bravo Fans
tz: Chicago
custom: {sourcePointName:EFSS, dataSyncRecovered:2020-07-10T01:00:10.497-04:00 New_York, inScope, backgroundPoint}
  source point name: EFSS
  data sync recovered: 2020-07-10T01:00:10.497-04:00

Bravo EF-20 Exhaust Fan Status
type: cur-point
type: his-point
has tag: cur
has tag: exhaust
has tag: fan
has tag: his
has tag: point
has tag: run
has tag: sensor
dis: Bravo EF-20 Exhaust Fan Status
equip ref: Bravo EF-20
kind: Bool
site ref: Bravo
space ref: Bravo Fans
tz: Chicago
custom: {dataSyncDownSince:2020-03-11T13:56:25.945-04:00 New_York, sourcePointName:EFStatus, dataSyncType:error, inScope, backgroundPoint}
  data sync down since: 2020-03-11T13:56:25.945-04:00
  source point name: EFStatus
  data sync type: error

Bravo EF-21
type: equip
has tag: equip
has tag: fan
has tag: hvac
dis: Bravo EF-21
site ref: Bravo
space ref: Bravo Fans

Bravo EF-21 Exhaust Fan Enable
type: cur-point
type: his-point
has tag: cur
has tag: enable
has tag: exhaust
has tag: fan
has tag: his
has tag: point
has tag: sensor
dis: Bravo EF-21 Exhaust Fan Enable
enum: STOP,On
equip ref: Bravo EF-21
kind: Bool
site ref: Bravo
space ref: Bravo Fans
tz: Chicago
custom: {dataSyncRecovered:2020-07-10T01:00:07.473-04:00 New_York, backgroundPoint}
  data sync recovered: 2020-07-10T01:00:07.473-04:00

Bravo EF-21 Exhaust Fan Status
type: cur-point
type: his-point
has tag: cur
has tag: exhaust
has tag: fan
has tag: his
has tag: point
has tag: run
has tag: sensor
dis: Bravo EF-21 Exhaust Fan Status
enum: stateNul,Off,RUNNING
equip ref: Bravo EF-21
kind: Str
site ref: Bravo
space ref: Bravo Fans
tz: Chicago
custom: {dataSyncRecovered:2020-07-10T01:00:11.258-04:00 New_York, backgroundPoint}
  data sync recovered: 2020-07-10T01:00:11.258-04:00

Bravo EF-22
type: equip
has tag: equip
has tag: fan
has tag: hvac
dis: Bravo EF-22
site ref: Bravo
space ref: Bravo Fans

Bravo EF-22 Exhaust Fan Enable
type: cur-point
type: his-point
has tag: cur
has tag: enable
has tag: exhaust
has tag: fan
has tag: his
has tag: point
has tag: sensor
dis: Bravo EF-22 Exhaust Fan Enable
enum: STOP,On
equip ref: Bravo EF-22
kind: Bool
site ref: Bravo
space ref: Bravo Fans
tz: Chicago
custom: {dataSyncRecovered:2020-07-10T01:00:07.598-04:00 New_York, backgroundPoint}
  data sync recovered: 2020-07-10T01:00:07.598-04:00

Bravo EF-22 Exhaust Fan Status
type: cur-point
type: his-point
has tag: cur
has tag: exhaust
has tag: fan
has tag: his
has tag: point
has tag: run
has tag: sensor
dis: Bravo EF-22 Exhaust Fan Status
enum: stateNul,Off,RUNNING
equip ref: Bravo EF-22
kind: Str
site ref: Bravo
space ref: Bravo Fans
tz: Chicago
custom: {dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, backgroundPoint}
  data sync recovered: 2020-07-10T01:00:10.374-04:00

Bravo EF-23
type: equip
has tag: equip
has tag: fan
has tag: hvac
dis: Bravo EF-23
site ref: Bravo
space ref: Bravo Fans

Bravo EF-23 Exhaust Fan Enable
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: enable
has tag: exhaust
has tag: fan
has tag: his
has tag: point
dis: Bravo EF-23 Exhaust Fan Enable
equip ref: Bravo EF-23
kind: Bool
site ref: Bravo
space ref: Bravo Fans
tz: Chicago
custom: {sourcePointName:EF23SS, dataSyncRecovered:2020-07-10T01:00:13.145-04:00 New_York, inScope, backgroundPoint}
  source point name: EF23SS
  data sync recovered: 2020-07-10T01:00:13.145-04:00

Bravo EF-23 Exhaust Fan Status
type: cur-point
type: his-point
has tag: cur
has tag: exhaust
has tag: fan
has tag: his
has tag: point
has tag: run
has tag: sensor
dis: Bravo EF-23 Exhaust Fan Status
equip ref: Bravo EF-23
kind: Bool
site ref: Bravo
space ref: Bravo Fans
tz: Chicago
custom: {sourcePointName:EF23Status, dataSyncRecovered:2020-07-10T01:00:09.879-04:00 New_York, inScope, backgroundPoint}
  source point name: EF23Status
  data sync recovered: 2020-07-10T01:00:09.879-04:00

Bravo EF-24
type: equip
has tag: equip
has tag: fan
has tag: hvac
dis: Bravo EF-24
site ref: Bravo
space ref: Bravo Fans

Bravo EF-24 Exhaust Fan Enable
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: enable
has tag: exhaust
has tag: fan
has tag: his
has tag: point
dis: Bravo EF-24 Exhaust Fan Enable
equip ref: Bravo EF-24
kind: Bool
site ref: Bravo
space ref: Bravo Fans
tz: Chicago
custom: {sourcePointName:EFSS, dataSyncRecovered:2020-07-10T01:00:09.879-04:00 New_York, inScope, backgroundPoint}
  source point name: EFSS
  data sync recovered: 2020-07-10T01:00:09.879-04:00

Bravo EF-24 Exhaust Fan Status
type: cur-point
type: his-point
has tag: cur
has tag: exhaust
has tag: fan
has tag: his
has tag: point
has tag: run
has tag: sensor
dis: Bravo EF-24 Exhaust Fan Status
equip ref: Bravo EF-24
kind: Bool
site ref: Bravo
space ref: Bravo Fans
tz: Chicago
custom: {dataSyncDownSince:2020-03-11T13:56:25.929-04:00 New_York, sourcePointName:EFStatus, dataSyncType:error, inScope, backgroundPoint}
  data sync down since: 2020-03-11T13:56:25.929-04:00
  source point name: EFStatus
  data sync type: error

Bravo EF-25
type: equip
has tag: equip
has tag: fan
has tag: hvac
dis: Bravo EF-25
site ref: Bravo
space ref: Bravo Fans

Bravo EF-25 Exhaust Fan Enable
type: cur-point
type: his-point
has tag: cur
has tag: enable
has tag: exhaust
has tag: fan
has tag: his
has tag: point
has tag: sensor
dis: Bravo EF-25 Exhaust Fan Enable
enum: STOP,On
equip ref: Bravo EF-25
kind: Bool
site ref: Bravo
space ref: Bravo Fans
tz: Chicago
custom: {dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, backgroundPoint}
  data sync recovered: 2020-07-10T01:00:10.003-04:00

Bravo EF-25 Exhaust Fan Status
type: cur-point
type: his-point
has tag: cur
has tag: exhaust
has tag: fan
has tag: his
has tag: point
has tag: run
has tag: sensor
dis: Bravo EF-25 Exhaust Fan Status
enum: stateNul,Off,RUNNING
equip ref: Bravo EF-25
kind: Str
site ref: Bravo
space ref: Bravo Fans
tz: Chicago
custom: {dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, backgroundPoint}
  data sync recovered: 2020-07-10T01:00:10.003-04:00

Bravo EF-26
type: equip
has tag: equip
has tag: fan
has tag: hvac
dis: Bravo EF-26
site ref: Bravo
space ref: Bravo Fans

Bravo EF-26 Exhaust Fan Enable
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: enable
has tag: exhaust
has tag: fan
has tag: his
has tag: point
dis: Bravo EF-26 Exhaust Fan Enable
equip ref: Bravo EF-26
kind: Bool
site ref: Bravo
space ref: Bravo Fans
tz: Chicago
custom: {sourcePointName:EFSS, dataSyncRecovered:2020-07-10T01:00:10.126-04:00 New_York, inScope, backgroundPoint}
  source point name: EFSS
  data sync recovered: 2020-07-10T01:00:10.126-04:00

Bravo EF-26 Exhaust Fan Status
type: cur-point
type: his-point
has tag: cur
has tag: exhaust
has tag: fan
has tag: his
has tag: point
has tag: run
has tag: sensor
dis: Bravo EF-26 Exhaust Fan Status
equip ref: Bravo EF-26
kind: Bool
site ref: Bravo
space ref: Bravo Fans
tz: Chicago
custom: {sourcePointName:EFStatus, dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, inScope, backgroundPoint}
  source point name: EFStatus
  data sync recovered: 2020-07-10T01:00:10.374-04:00

Bravo EF-27
type: equip
has tag: equip
has tag: fan
has tag: hvac
dis: Bravo EF-27
site ref: Bravo
space ref: Bravo Fans

Bravo EF-27 Exhaust Fan Enable
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: enable
has tag: exhaust
has tag: fan
has tag: his
has tag: point
dis: Bravo EF-27 Exhaust Fan Enable
equip ref: Bravo EF-27
kind: Bool
site ref: Bravo
space ref: Bravo Fans
tz: Chicago
custom: {sourcePointName:EFSS, dataSyncRecovered:2020-07-10T01:00:11.258-04:00 New_York, inScope, backgroundPoint}
  source point name: EFSS
  data sync recovered: 2020-07-10T01:00:11.258-04:00

Bravo EF-27 Exhaust Fan Status
type: cur-point
type: his-point
has tag: cur
has tag: exhaust
has tag: fan
has tag: his
has tag: point
has tag: run
has tag: sensor
dis: Bravo EF-27 Exhaust Fan Status
equip ref: Bravo EF-27
kind: Bool
site ref: Bravo
space ref: Bravo Fans
tz: Chicago
custom: {sourcePointName:EFStatus, dataSyncRecovered:2020-07-10T01:00:07.473-04:00 New_York, inScope, backgroundPoint}
  source point name: EFStatus
  data sync recovered: 2020-07-10T01:00:07.473-04:00

Bravo EF-28 Exhaust Fan Status
type: cur-point
type: his-point
has tag: cur
has tag: exhaust
has tag: fan
has tag: his
has tag: point
has tag: run
has tag: sensor
dis: Bravo EF-28 Exhaust Fan Status
equip ref: Bravo EF-28
  type: equip
  has tag: equip
  has tag: fan
  has tag: hvac
  dis: Bravo EF-28
  site ref: Bravo
  space ref: Bravo Fans
kind: Bool
site ref: Bravo
space ref: Bravo Fans
tz: Chicago
custom: {sourcePointName:EF28Status, dataSyncRecovered:2020-07-10T01:00:07.598-04:00 New_York, inScope, backgroundPoint}
  source point name: EF28Status
  data sync recovered: 2020-07-10T01:00:07.598-04:00

Bravo EF-3
type: equip
has tag: equip
has tag: fan
has tag: hvac
dis: Bravo EF-3
site ref: Bravo
space ref: Bravo Fans

Bravo EF-3 Exhaust Fan Enable
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: enable
has tag: exhaust
has tag: fan
has tag: his
has tag: point
dis: Bravo EF-3 Exhaust Fan Enable
equip ref: Bravo EF-3
kind: Bool
site ref: Bravo
space ref: Bravo Fans
tz: Chicago
custom: {sourcePointName:EFSS, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
  source point name: EFSS
  data sync recovered: 2020-07-10T01:00:10.745-04:00

Bravo EF-3 Exhaust Fan Status
type: cur-point
type: his-point
has tag: cur
has tag: exhaust
has tag: fan
has tag: his
has tag: point
has tag: run
has tag: sensor
dis: Bravo EF-3 Exhaust Fan Status
equip ref: Bravo EF-3
kind: Bool
site ref: Bravo
space ref: Bravo Fans
tz: Chicago
custom: {sourcePointName:EFStatus, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
  source point name: EFStatus
  data sync recovered: 2020-07-10T01:00:10.003-04:00

Bravo EF-4
type: equip
has tag: equip
has tag: fan
has tag: hvac
dis: Bravo EF-4
site ref: Bravo
space ref: Bravo Fans

Bravo EF-4 Exhaust Fan Enable
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: enable
has tag: exhaust
has tag: fan
has tag: his
has tag: point
dis: Bravo EF-4 Exhaust Fan Enable
equip ref: Bravo EF-4
kind: Bool
site ref: Bravo
space ref: Bravo Fans
tz: Chicago
custom: {sourcePointName:EFSS, dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, inScope, backgroundPoint}
  source point name: EFSS
  data sync recovered: 2020-07-10T01:00:10.374-04:00

Bravo EF-4 Exhaust Fan Status
type: cur-point
type: his-point
has tag: cur
has tag: exhaust
has tag: fan
has tag: his
has tag: point
has tag: run
has tag: sensor
dis: Bravo EF-4 Exhaust Fan Status
equip ref: Bravo EF-4
kind: Bool
site ref: Bravo
space ref: Bravo Fans
tz: Chicago
custom: {dataSyncDownSince:2020-03-11T13:56:25.945-04:00 New_York, sourcePointName:EFStatus, dataSyncType:error, inScope, backgroundPoint}
  data sync down since: 2020-03-11T13:56:25.945-04:00
  source point name: EFStatus
  data sync type: error

Bravo EF-5
type: equip
has tag: equip
has tag: fan
has tag: hvac
dis: Bravo EF-5
site ref: Bravo
space ref: Bravo Fans

Bravo EF-5 Exhaust Fan Enable
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: enable
has tag: exhaust
has tag: fan
has tag: his
has tag: point
dis: Bravo EF-5 Exhaust Fan Enable
equip ref: Bravo EF-5
kind: Bool
site ref: Bravo
space ref: Bravo Fans
tz: Chicago
custom: {sourcePointName:EFSS, dataSyncRecovered:2020-07-10T01:00:10.87-04:00 New_York, inScope, backgroundPoint}
  source point name: EFSS
  data sync recovered: 2020-07-10T01:00:10.87-04:00

Bravo EF-5 Exhaust Fan Status
type: cur-point
type: his-point
has tag: cur
has tag: exhaust
has tag: fan
has tag: his
has tag: point
has tag: run
has tag: sensor
dis: Bravo EF-5 Exhaust Fan Status
equip ref: Bravo EF-5
kind: Bool
site ref: Bravo
space ref: Bravo Fans
tz: Chicago
custom: {dataSyncDownSince:2020-03-11T13:56:25.929-04:00 New_York, sourcePointName:EFStatus, dataSyncType:error, inScope, backgroundPoint}
  data sync down since: 2020-03-11T13:56:25.929-04:00
  source point name: EFStatus
  data sync type: error

Bravo EF-6
type: equip
has tag: equip
has tag: fan
has tag: hvac
dis: Bravo EF-6
site ref: Bravo
space ref: Bravo Fans

Bravo EF-6 Exhaust Fan Enable
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: enable
has tag: exhaust
has tag: fan
has tag: his
has tag: point
dis: Bravo EF-6 Exhaust Fan Enable
equip ref: Bravo EF-6
kind: Bool
site ref: Bravo
space ref: Bravo Fans
tz: Chicago
custom: {sourcePointName:EFSS, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, inScope, backgroundPoint}
  source point name: EFSS
  data sync recovered: 2020-07-10T01:00:10.62-04:00

Bravo EF-6 Exhaust Fan Status
type: cur-point
type: his-point
has tag: cur
has tag: exhaust
has tag: fan
has tag: his
has tag: point
has tag: run
has tag: sensor
dis: Bravo EF-6 Exhaust Fan Status
equip ref: Bravo EF-6
kind: Bool
site ref: Bravo
space ref: Bravo Fans
tz: Chicago
custom: {dataSyncDownSince:2020-05-28T01:00:09.102-04:00 New_York, sourcePointName:EFStatus, dataSyncType:error, inScope, backgroundPoint}
  data sync down since: 2020-05-28T01:00:09.102-04:00
  source point name: EFStatus
  data sync type: error

Bravo EF-7
type: equip
has tag: equip
has tag: fan
has tag: hvac
dis: Bravo EF-7
site ref: Bravo
space ref: Bravo Fans

Bravo EF-7 Exhaust Fan Enable
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: enable
has tag: exhaust
has tag: fan
has tag: his
has tag: point
dis: Bravo EF-7 Exhaust Fan Enable
equip ref: Bravo EF-7
kind: Bool
site ref: Bravo
space ref: Bravo Fans
tz: Chicago
custom: {sourcePointName:EFSS, dataSyncRecovered:2020-07-10T01:00:07.598-04:00 New_York, inScope, backgroundPoint}
  source point name: EFSS
  data sync recovered: 2020-07-10T01:00:07.598-04:00

Bravo EF-7 Exhaust Fan Status
type: cur-point
type: his-point
has tag: cur
has tag: exhaust
has tag: fan
has tag: his
has tag: point
has tag: run
has tag: sensor
dis: Bravo EF-7 Exhaust Fan Status
equip ref: Bravo EF-7
kind: Bool
site ref: Bravo
space ref: Bravo Fans
tz: Chicago
custom: {dataSyncDownSince:2020-03-11T13:56:25.929-04:00 New_York, sourcePointName:EFStatus, dataSyncType:error, inScope, backgroundPoint}
  data sync down since: 2020-03-11T13:56:25.929-04:00
  source point name: EFStatus
  data sync type: error

Bravo EF-8
type: equip
has tag: equip
has tag: fan
has tag: hvac
dis: Bravo EF-8
site ref: Bravo
space ref: Bravo Fans

Bravo EF-8 Exhaust Fan Enable
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: enable
has tag: exhaust
has tag: fan
has tag: his
has tag: point
dis: Bravo EF-8 Exhaust Fan Enable
equip ref: Bravo EF-8
kind: Bool
site ref: Bravo
space ref: Bravo Fans
tz: Chicago
custom: {sourcePointName:EFSS, dataSyncRecovered:2020-07-10T01:00:11.258-04:00 New_York, inScope, backgroundPoint}
  source point name: EFSS
  data sync recovered: 2020-07-10T01:00:11.258-04:00

Bravo EF-8 Exhaust Fan Status
type: cur-point
type: his-point
has tag: cur
has tag: exhaust
has tag: fan
has tag: his
has tag: point
has tag: run
has tag: sensor
dis: Bravo EF-8 Exhaust Fan Status
equip ref: Bravo EF-8
kind: Bool
site ref: Bravo
space ref: Bravo Fans
tz: Chicago
custom: {dataSyncDownSince:2020-03-11T13:56:25.945-04:00 New_York, sourcePointName:EFStatus, dataSyncType:error, inScope, backgroundPoint}
  data sync down since: 2020-03-11T13:56:25.945-04:00
  source point name: EFStatus
  data sync type: error

Bravo EF-9
type: equip
has tag: equip
has tag: fan
has tag: hvac
dis: Bravo EF-9
site ref: Bravo
space ref: Bravo Fans

Bravo EF-9 Exhaust Fan Enable
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: enable
has tag: exhaust
has tag: fan
has tag: his
has tag: point
dis: Bravo EF-9 Exhaust Fan Enable
equip ref: Bravo EF-9
kind: Bool
site ref: Bravo
space ref: Bravo Fans
tz: Chicago
custom: {sourcePointName:EFSS, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
  source point name: EFSS
  data sync recovered: 2020-07-10T01:00:10.745-04:00

Bravo EF-9 Exhaust Fan Status
type: cur-point
type: his-point
has tag: cur
has tag: exhaust
has tag: fan
has tag: his
has tag: point
has tag: run
has tag: sensor
dis: Bravo EF-9 Exhaust Fan Status
equip ref: Bravo EF-9
kind: Bool
site ref: Bravo
space ref: Bravo Fans
tz: Chicago
custom: {dataSyncDownSince:2020-07-02T01:00:04.305-04:00 New_York, sourcePointName:EFStatus, dataSyncType:error, pointType:, inScope, backgroundPoint}
  data sync down since: 2020-07-02T01:00:04.305-04:00
  source point name: EFStatus
  data sync type: error

Bravo FCU-1
type: fcu
type: thermostat
has tag: chilledWaterCooling
has tag: directZone
has tag: elecHeating
has tag: equip
has tag: fcu
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: zone
chilled water ref: Bravo Chilled Water Plant
dis: Bravo FCU-1
site ref: Bravo
space ref: Bravo FCUs

Bravo FCU-1 Cooling Valve Output
type: cur-point
type: his-point
has tag: chilled
has tag: cool
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: valve
has tag: water
dis: Bravo FCU-1 Cooling Valve Output
equip ref: Bravo FCU-1
kind: Number
site ref: Bravo
space ref: Bravo FCUs
tz: Chicago
unit: %
custom: {sourcePointName:ChwVlv, dataSyncRecovered:2020-07-10T01:00:13.145-04:00 New_York, inScope, backgroundPoint}
  source point name: ChwVlv
  data sync recovered: 2020-07-10T01:00:13.145-04:00

Bravo FCU-1 Heating Valve Output
type: cur-point
type: his-point
has tag: cur
has tag: heat
has tag: his
has tag: point
has tag: sensor
has tag: valve
dis: Bravo FCU-1 Heating Valve Output
equip ref: Bravo FCU-1
kind: Number
site ref: Bravo
space ref: Bravo FCUs
tz: Chicago
unit: %
custom: {precision:0, dataSyncRecovered:2020-07-10T01:00:09.627-04:00 New_York, backgroundPoint}
  precision: 0
  data sync recovered: 2020-07-10T01:00:09.627-04:00

Bravo FCU-1 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo FCU-1 Zone Temperature
equip ref: Bravo FCU-1
kind: Number
site ref: Bravo
space ref: Bravo FCUs
tz: Chicago
unit: °F
custom: {sourcePointName:SpcTemp, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
  source point name: SpcTemp
  data sync recovered: 2020-07-10T01:00:10.003-04:00

Bravo FCU-1 Zone Temperature Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo FCU-1 Zone Temperature Setpoint
equip ref: Bravo FCU-1
kind: Number
max val: 327
min val: -273
site ref: Bravo
space ref: Bravo FCUs
tz: Chicago
unit: °F
custom: {precision:2, dataSyncRecovered:2020-07-10T01:00:10.87-04:00 New_York, backgroundPoint}
  precision: 2
  data sync recovered: 2020-07-10T01:00:10.87-04:00

Bravo FCU-2
type: fcu
type: thermostat
has tag: chilledWaterCooling
has tag: directZone
has tag: elecHeating
has tag: equip
has tag: fcu
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: zone
chilled water ref: Bravo Chilled Water Plant
dis: Bravo FCU-2
site ref: Bravo
space ref: Bravo FCUs

Bravo FCU-2 Cooling Valve Output
type: cur-point
type: his-point
has tag: chilled
has tag: cool
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: valve
has tag: water
dis: Bravo FCU-2 Cooling Valve Output
equip ref: Bravo FCU-2
kind: Number
site ref: Bravo
space ref: Bravo FCUs
tz: Chicago
unit: %
custom: {sourcePointName:ChwVlv, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
  source point name: ChwVlv
  data sync recovered: 2020-07-10T01:00:10.745-04:00

Bravo FCU-2 Heating Valve Output
type: cur-point
type: his-point
has tag: cur
has tag: heat
has tag: his
has tag: point
has tag: sensor
has tag: valve
dis: Bravo FCU-2 Heating Valve Output
equip ref: Bravo FCU-2
kind: Number
site ref: Bravo
space ref: Bravo FCUs
tz: Chicago
unit: %
custom: {precision:0, dataSyncRecovered:2020-07-10T01:00:11.258-04:00 New_York, backgroundPoint}
  precision: 0
  data sync recovered: 2020-07-10T01:00:11.258-04:00

Bravo FCU-2 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo FCU-2 Zone Temperature
equip ref: Bravo FCU-2
kind: Number
site ref: Bravo
space ref: Bravo FCUs
tz: Chicago
unit: °F
custom: {sourcePointName:SpcTemp, dataSyncRecovered:2020-07-10T01:00:10.995-04:00 New_York, inScope, backgroundPoint}
  source point name: SpcTemp
  data sync recovered: 2020-07-10T01:00:10.995-04:00

Bravo FCU-2 Zone Temperature Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo FCU-2 Zone Temperature Setpoint
equip ref: Bravo FCU-2
kind: Number
max val: 327
min val: -273
site ref: Bravo
space ref: Bravo FCUs
tz: Chicago
unit: °F
custom: {precision:2, dataSyncRecovered:2020-07-10T01:00:10.126-04:00 New_York, backgroundPoint}
  precision: 2
  data sync recovered: 2020-07-10T01:00:10.126-04:00

Bravo FCU-3
type: fcu
type: thermostat
has tag: chilledWaterCooling
has tag: directZone
has tag: elecHeating
has tag: equip
has tag: fcu
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: zone
chilled water ref: Bravo Chilled Water Plant
dis: Bravo FCU-3
site ref: Bravo
space ref: Bravo FCUs

Bravo FCU-3 Cooling Valve Output
type: cur-point
type: his-point
has tag: chilled
has tag: cool
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: valve
has tag: water
dis: Bravo FCU-3 Cooling Valve Output
equip ref: Bravo FCU-3
kind: Number
site ref: Bravo
space ref: Bravo FCUs
tz: Chicago
unit: %
custom: {sourcePointName:ChwVlv, dataSyncRecovered:2020-07-10T01:00:09.627-04:00 New_York, inScope, backgroundPoint}
  source point name: ChwVlv
  data sync recovered: 2020-07-10T01:00:09.627-04:00

Bravo FCU-3 Heating Valve Output
type: cur-point
type: his-point
has tag: cur
has tag: heat
has tag: his
has tag: point
has tag: sensor
has tag: valve
dis: Bravo FCU-3 Heating Valve Output
equip ref: Bravo FCU-3
kind: Number
site ref: Bravo
space ref: Bravo FCUs
tz: Chicago
unit: %
custom: {precision:0, dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, backgroundPoint}
  precision: 0
  data sync recovered: 2020-07-10T01:00:09.752-04:00

Bravo FCU-3 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo FCU-3 Zone Temperature
equip ref: Bravo FCU-3
kind: Number
site ref: Bravo
space ref: Bravo FCUs
tz: Chicago
unit: °F
custom: {sourcePointName:SpcTemp, dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, inScope, backgroundPoint}
  source point name: SpcTemp
  data sync recovered: 2020-07-10T01:00:09.752-04:00

Bravo FCU-3 Zone Temperature Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo FCU-3 Zone Temperature Setpoint
equip ref: Bravo FCU-3
kind: Number
max val: 327
min val: -273
site ref: Bravo
space ref: Bravo FCUs
tz: Chicago
unit: °F
custom: {precision:2, dataSyncRecovered:2020-07-10T01:00:10.995-04:00 New_York, backgroundPoint}
  precision: 2
  data sync recovered: 2020-07-10T01:00:10.995-04:00

Bravo FCU-4
type: fcu
type: thermostat
has tag: chilledWaterCooling
has tag: directZone
has tag: elecHeating
has tag: equip
has tag: fcu
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: zone
chilled water ref: Bravo Chilled Water Plant
dis: Bravo FCU-4
site ref: Bravo
space ref: Bravo FCUs

Bravo FCU-4 Cooling Valve Output
type: cur-point
type: his-point
has tag: chilled
has tag: cool
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: valve
has tag: water
dis: Bravo FCU-4 Cooling Valve Output
equip ref: Bravo FCU-4
kind: Number
site ref: Bravo
space ref: Bravo FCUs
tz: Chicago
unit: %
custom: {sourcePointName:ChwVlv, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, inScope, backgroundPoint}
  source point name: ChwVlv
  data sync recovered: 2020-07-10T01:00:10.62-04:00

Bravo FCU-4 Heating Valve Output
type: cur-point
type: his-point
has tag: cur
has tag: heat
has tag: his
has tag: point
has tag: sensor
has tag: valve
dis: Bravo FCU-4 Heating Valve Output
equip ref: Bravo FCU-4
kind: Number
site ref: Bravo
space ref: Bravo FCUs
tz: Chicago
unit: %
custom: {precision:0, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, backgroundPoint}
  precision: 0
  data sync recovered: 2020-07-10T01:00:10.62-04:00

Bravo FCU-4 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo FCU-4 Zone Temperature
equip ref: Bravo FCU-4
kind: Number
site ref: Bravo
space ref: Bravo FCUs
tz: Chicago
unit: °F
custom: {sourcePointName:SpcTemp, dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, inScope, backgroundPoint}
  source point name: SpcTemp
  data sync recovered: 2020-07-10T01:00:09.752-04:00

Bravo FCU-4 Zone Temperature Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo FCU-4 Zone Temperature Setpoint
equip ref: Bravo FCU-4
kind: Number
max val: 327
min val: -273
site ref: Bravo
space ref: Bravo FCUs
tz: Chicago
unit: °F
custom: {precision:2, dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, backgroundPoint}
  precision: 2
  data sync recovered: 2020-07-10T01:00:09.752-04:00

Bravo FCUs
type: space
has tag: space
dis: Bravo FCUs
site ref: Bravo
custom: {equipType}

Bravo Fans
type: space
has tag: space
dis: Bravo Fans
site ref: Bravo
custom: {equipType}

Bravo HHW Pump 1
type: equip
has tag: equip
has tag: hot
has tag: hvac
has tag: pump
has tag: water
dis: Bravo HHW Pump 1
site ref: Bravo
space ref: Bravo HW System

Bravo HHW Pump 1 HHW Pump Status
type: cur-point
type: his-point
has tag: cur
has tag: his
has tag: hot
has tag: point
has tag: pump
has tag: sensor
has tag: water
dis: Bravo HHW Pump 1 HHW Pump Status
enum: false,true
equip ref: Bravo HHW Pump 1
kind: Bool
site ref: Bravo
space ref: Bravo HW System
tz: Chicago
custom: {dataSyncRecovered:2020-07-10T01:00:10.995-04:00 New_York, backgroundPoint, status}
  data sync recovered: 2020-07-10T01:00:10.995-04:00

Bravo HHW Pump 1 HHW Pump VFD Speed
type: cur-point
type: his-point
has tag: cur
has tag: his
has tag: hot
has tag: point
has tag: pump
has tag: sensor
has tag: speed
has tag: water
dis: Bravo HHW Pump 1 HHW Pump VFD Speed
equip ref: Bravo HHW Pump 1
kind: Number
site ref: Bravo
space ref: Bravo HW System
tz: Chicago
custom: {precision:2, dataSyncRecovered:2020-07-10T01:00:10.497-04:00 New_York, backgroundPoint}
  precision: 2
  data sync recovered: 2020-07-10T01:00:10.497-04:00

Bravo HHW Pump 2
type: equip
has tag: equip
has tag: hot
has tag: hvac
has tag: pump
has tag: water
dis: Bravo HHW Pump 2
site ref: Bravo
space ref: Bravo HW System

Bravo HHW Pump 2 HHW Pump Status
type: cur-point
type: his-point
has tag: cur
has tag: his
has tag: hot
has tag: point
has tag: pump
has tag: sensor
has tag: water
dis: Bravo HHW Pump 2 HHW Pump Status
enum: false,true
equip ref: Bravo HHW Pump 2
kind: Bool
site ref: Bravo
space ref: Bravo HW System
tz: Chicago
custom: {dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, backgroundPoint, status}
  data sync recovered: 2020-07-10T01:00:10.374-04:00

Bravo HHW Pump 2 HHW Pump VFD Speed
type: cur-point
type: his-point
has tag: cur
has tag: his
has tag: hot
has tag: point
has tag: pump
has tag: sensor
has tag: speed
has tag: water
dis: Bravo HHW Pump 2 HHW Pump VFD Speed
equip ref: Bravo HHW Pump 2
kind: Number
site ref: Bravo
space ref: Bravo HW System
tz: Chicago
custom: {precision:2, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, backgroundPoint}
  precision: 2
  data sync recovered: 2020-07-10T01:00:10.62-04:00

Bravo HW System
type: space
has tag: space
dis: Bravo HW System
site ref: Bravo
custom: {equipType}

Bravo RTU-1
type: rtu
has tag: ahu
has tag: chilledWaterCooling
has tag: equip
has tag: hotWaterHeating
has tag: hvac
has tag: rtu
has tag: singleDuct
has tag: vavZone
dis: Bravo RTU-1
site ref: Bravo
space ref: Bravo RTUs
custom:
  label: {designDischargeAirFlow:15300cfm, steamHumidifier, designHotWaterLeavingTemp:65°F, designHotWaterPower:145MMBTU/h, designOutsideAirFlowMin:3500cfm, designDischargeFanAirDeltaPressure:7.04inH₂O, designSource:Drawings, designChilledWaterLeavingTemp:59°F, designChilledWaterPower:722.3MMBTU/h, designHotWaterFlow:24.1gal/min, designChilledWaterFlow:96.4gal/min, designReturnAirFlow:15300cfm, designHotWaterEnteringTemp:75°F, designOutsideAirFlow:15300cfm, designReturnFanPower:15hp, designChilledWaterEnteringTemp:44°F, designDischargeFanPower:40hp, designReturnFanAirDeltaPressure:1.66inH₂O}
  design discharge air flow: 15300
  design hot water leaving temp: 65
  design hot water power: 145
  design outside air flow min: 3500
  design discharge fan air delta pressure: 7.04
  design source: Drawings
  design chilled water leaving temp: 59
  design chilled water power: 722.3
  design hot water flow: 24.1
  design chilled water flow: 96.4
  design return air flow: 15300
  design hot water entering temp: 75
  design outside air flow: 15300
  design return fan power: 15
  design chilled water entering temp: 44
  design discharge fan power: 40
  design return fan air delta pressure: 1.66

Bravo RTU-1 AHU Operation Mode
type: computed-point
type: his-point
has tag: computed
has tag: his
has tag: point
has tag: sensor
dis: Bravo RTU-1 AHU Operation Mode
equip ref: Bravo RTU-1
kind: Str
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
custom: {mode, dataSyncRecovered:2020-07-14T01:00:05.167-04:00 New_York, backgroundPoint}
  data sync recovered: 2020-07-14T01:00:05.167-04:00

Bravo RTU-1 Cooling Valve Output
type: cur-point
type: his-point
has tag: chilled
has tag: cmd
has tag: cool
has tag: cur
has tag: his
has tag: point
has tag: valve
has tag: water
dis: Bravo RTU-1 Cooling Valve Output
equip ref: Bravo RTU-1
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: %
custom: {sourcePointName:CWV, dataSyncRecovered:2020-07-10T01:00:10.126-04:00 New_York, inScope, backgroundPoint}
  source point name: CWV
  data sync recovered: 2020-07-10T01:00:10.126-04:00

Bravo RTU-1 Exhaust Air Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: damper
has tag: exhaust
has tag: his
has tag: point
has tag: sensor
dis: Bravo RTU-1 Exhaust Air Damper Output
equip ref: Bravo RTU-1
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: %
custom: {sourcePointName:EAD, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
  source point name: EAD
  data sync recovered: 2020-07-10T01:00:10.745-04:00

Bravo RTU-1 Fan Power (Auto-computed)
type: his-point
has tag: his
has tag: point
has tag: sp
dis: Bravo RTU-1 Fan Power (Auto-computed)
equip ref: Bravo RTU-1
kind: Number
site ref: Bravo
tz: Chicago
custom: {cache, dataSyncDownSince:2020-04-09T01:00:02.664-04:00 New_York, dataSyncType:error, backgroundPoint}
  data sync down since: 2020-04-09T01:00:02.664-04:00
  data sync type: error

Bravo RTU-1 Heating/Cooling Load (Auto-computed)
type: his-point
has tag: his
has tag: point
has tag: sp
dis: Bravo RTU-1 Heating/Cooling Load (Auto-computed)
equip ref: Bravo RTU-1
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: BTU/h
custom: {cache, dataSyncRecovered:2020-07-14T01:00:05.167-04:00 New_York, backgroundPoint}
  data sync recovered: 2020-07-14T01:00:05.167-04:00

Bravo RTU-1 Humidifier Enable
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: enable
has tag: his
has tag: humidifier
has tag: point
dis: Bravo RTU-1 Humidifier Enable
equip ref: Bravo RTU-1
kind: Bool
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
custom: {sourcePointName:HUM_ENABLE, dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, inScope, backgroundPoint}
  source point name: HUM_ENABLE
  data sync recovered: 2020-07-10T01:00:10.374-04:00

Bravo RTU-1 Humidifier Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: his
has tag: humidifier
has tag: point
has tag: steam
has tag: valve
dis: Bravo RTU-1 Humidifier Output
equip ref: Bravo RTU-1
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: %
custom: {sourcePointName:HUM VLV, dataSyncRecovered:2020-07-10T01:00:10.87-04:00 New_York, inScope, backgroundPoint}
  source point name: HUM VLV
  data sync recovered: 2020-07-10T01:00:10.87-04:00

Bravo RTU-1 Max Damper Position
type: computed-point
type: his-point
has tag: cmd
has tag: computed
has tag: damper
has tag: his
has tag: point
dis: Bravo RTU-1 Max Damper Position
equip ref: Bravo RTU-1
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: %
custom: {max, dataSyncRecovered:2020-07-14T01:00:05.167-04:00 New_York, backgroundPoint}
  has tag: max
  data sync recovered: 2020-07-14T01:00:05.167-04:00

Bravo RTU-1 Min Outdoor Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: flow
has tag: his
has tag: outside
has tag: point
has tag: sp
dis: Bravo RTU-1 Min Outdoor Air Flow Setpoint
equip ref: Bravo RTU-1
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: %
custom: {min, sourcePointName:MinOA_SP, dataSyncRecovered:2020-07-10T01:00:10.249-04:00 New_York, pointType:, inScope, backgroundPoint}
  has tag: min
  source point name: MinOA_SP
  data sync recovered: 2020-07-10T01:00:10.249-04:00

Bravo RTU-1 Min Outdoor Air Flow/10
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: flow
has tag: his
has tag: outside
has tag: point
has tag: sensor
dis: Bravo RTU-1 Min Outdoor Air Flow/10
equip ref: Bravo RTU-1
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: cfm
custom: {min, sourcePointName:MIN OA CFM / 10, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
  has tag: min
  source point name: MIN OA CFM / 10
  data sync recovered: 2020-07-10T01:00:10.003-04:00

Bravo RTU-1 Minimum Outside Air Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: damper
has tag: his
has tag: point
has tag: sensor
dis: Bravo RTU-1 Minimum Outside Air Damper Output
equip ref: Bravo RTU-1
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: %
custom: {sourcePointName:Min OAD, dataSyncRecovered:2020-07-10T01:00:07.598-04:00 New_York, inScope, outsideMin, backgroundPoint}
  source point name: Min OAD
  data sync recovered: 2020-07-10T01:00:07.598-04:00

Bravo RTU-1 Mixed Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: mixed
has tag: point
has tag: sensor
has tag: temp
dis: Bravo RTU-1 Mixed Air Temperature
equip ref: Bravo RTU-1
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: °F
custom: {sourcePointName:MAT, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
  source point name: MAT
  data sync recovered: 2020-07-10T01:00:10.745-04:00

Bravo RTU-1 Mixed Air Temperature Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: mixed
has tag: point
has tag: sp
has tag: temp
dis: Bravo RTU-1 Mixed Air Temperature Setpoint
equip ref: Bravo RTU-1
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: °F
custom: {sourcePointName:MAT STPT, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
  source point name: MAT STPT
  data sync recovered: 2020-07-10T01:00:10.003-04:00

Bravo RTU-1 Outside Air Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: his
has tag: outside
has tag: point
dis: Bravo RTU-1 Outside Air Damper Output
equip ref: Bravo RTU-1
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: %
custom: {sourcePointName:OAD, dataSyncRecovered:2020-07-10T01:00:10.249-04:00 New_York, inScope, backgroundPoint}
  source point name: OAD
  data sync recovered: 2020-07-10T01:00:10.249-04:00

Bravo RTU-1 Outside Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: flow
has tag: his
has tag: outside
has tag: point
has tag: sensor
dis: Bravo RTU-1 Outside Air Flow
equip ref: Bravo RTU-1
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: cfm
custom: {sourcePointName:OA CFM, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
  source point name: OA CFM
  data sync recovered: 2020-07-10T01:00:10.745-04:00

Bravo RTU-1 Outside Air Percentage (Auto-computed)
type: his-point
has tag: his
has tag: point
has tag: sp
dis: Bravo RTU-1 Outside Air Percentage (Auto-computed)
equip ref: Bravo RTU-1
kind: Number
site ref: Bravo
tz: Chicago
custom: {cache, dataSyncDownSince:2020-04-09T01:00:02.656-04:00 New_York, dataSyncType:error, backgroundPoint}
  data sync down since: 2020-04-09T01:00:02.656-04:00
  data sync type: error

Bravo RTU-1 Percent Outside Air
type: computed-point
type: his-point
has tag: air
has tag: computed
has tag: his
has tag: outside
has tag: point
has tag: sensor
has tag: temp
dis: Bravo RTU-1 Percent Outside Air
equip ref: Bravo RTU-1
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: %
custom: {dataSyncRecovered:2020-07-14T01:00:05.167-04:00 New_York, backgroundPoint}
  data sync recovered: 2020-07-14T01:00:05.167-04:00

Bravo RTU-1 Return Air Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: damper
has tag: his
has tag: point
has tag: return
has tag: sensor
dis: Bravo RTU-1 Return Air Damper Output
equip ref: Bravo RTU-1
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: %
custom: {sourcePointName:RET/REL DAMPER, dataSyncRecovered:2020-07-10T01:00:11.125-04:00 New_York, inScope, backgroundPoint}
  source point name: RET/REL DAMPER
  data sync recovered: 2020-07-10T01:00:11.125-04:00

Bravo RTU-1 Return Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: flow
has tag: his
has tag: point
has tag: return
has tag: sensor
dis: Bravo RTU-1 Return Air Flow
equip ref: Bravo RTU-1
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: cfm
custom: {sourcePointName:RA CFM, dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, inScope, backgroundPoint}
  source point name: RA CFM
  data sync recovered: 2020-07-10T01:00:10.374-04:00

Bravo RTU-1 Return Air Humidity
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: humidity
has tag: point
has tag: return
has tag: sensor
dis: Bravo RTU-1 Return Air Humidity
equip ref: Bravo RTU-1
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: %
custom: {sourcePointName:RAH, dataSyncRecovered:2020-07-10T01:00:09.627-04:00 New_York, inScope, backgroundPoint}
  source point name: RAH
  data sync recovered: 2020-07-10T01:00:09.627-04:00

Bravo RTU-1 Return Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: return
has tag: sensor
has tag: temp
dis: Bravo RTU-1 Return Air Temperature
equip ref: Bravo RTU-1
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: °F
custom: {sourcePointName:RAT, dataSyncRecovered:2020-07-10T01:00:11.258-04:00 New_York, inScope, backgroundPoint}
  source point name: RAT
  data sync recovered: 2020-07-10T01:00:11.258-04:00

Bravo RTU-1 Return Fan Status
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: fan
has tag: his
has tag: point
has tag: return
has tag: run
has tag: sensor
dis: Bravo RTU-1 Return Fan Status
equip ref: Bravo RTU-1
kind: Bool
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
custom: {sourcePointName:RF FAN STATUS, dataSyncRecovered:2020-07-10T01:00:10.995-04:00 New_York, inScope, backgroundPoint}
  source point name: RF FAN STATUS
  data sync recovered: 2020-07-10T01:00:10.995-04:00

Bravo RTU-1 Return Fan VFD Speed
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: fan
has tag: his
has tag: point
has tag: return
has tag: sensor
has tag: speed
dis: Bravo RTU-1 Return Fan VFD Speed
equip ref: Bravo RTU-1
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: %
custom: {sourcePointName:ACT_OUTPUT_SPEED, dataSyncRecovered:2020-07-10T01:00:07.721-04:00 New_York, inScope, backgroundPoint}
  source point name: ACT_OUTPUT_SPEED
  data sync recovered: 2020-07-10T01:00:07.721-04:00

Bravo RTU-1 Supply Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo RTU-1 Supply Air Flow
equip ref: Bravo RTU-1
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: cfm
custom: {sourcePointName:SA CFM, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
  source point name: SA CFM
  data sync recovered: 2020-07-10T01:00:10.745-04:00

Bravo RTU-1 Supply Air Humidity
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: humidity
has tag: point
has tag: sensor
dis: Bravo RTU-1 Supply Air Humidity
equip ref: Bravo RTU-1
kind: Number
point function: sensor
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: %
custom: {sourcePointName:DAH, dataSyncRecovered:2020-07-10T01:00:09.879-04:00 New_York, inScope, backgroundPoint}
  source point name: DAH
  data sync recovered: 2020-07-10T01:00:09.879-04:00

Bravo RTU-1 Supply Air Humidity Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: humidity
has tag: point
has tag: sp
dis: Bravo RTU-1 Supply Air Humidity Setpoint
equip ref: Bravo RTU-1
kind: Number
point function: sp
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: %
custom: {sourcePointName:Humidity SP, dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, inScope, backgroundPoint}
  source point name: Humidity SP
  data sync recovered: 2020-07-10T01:00:09.752-04:00

Bravo RTU-1 Supply Air Pressure Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: pressure
has tag: sp
dis: Bravo RTU-1 Supply Air Pressure Setpoint
equip ref: Bravo RTU-1
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: inH₂O
custom: {static, sourcePointName:Static Stpt, dataSyncRecovered:2020-07-10T01:00:13.145-04:00 New_York, inScope, backgroundPoint}
  source point name: Static Stpt
  data sync recovered: 2020-07-10T01:00:13.145-04:00

Bravo RTU-1 Supply Air Static Pressure
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: pressure
has tag: sensor
dis: Bravo RTU-1 Supply Air Static Pressure
equip ref: Bravo RTU-1
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: inH₂O
custom: {sourcePointName:DISCH STATIC, dataSyncRecovered:2020-07-10T01:00:09.879-04:00 New_York, inScope, backgroundPoint}
  source point name: DISCH STATIC
  data sync recovered: 2020-07-10T01:00:09.879-04:00

Bravo RTU-1 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo RTU-1 Supply Air Temperature
equip ref: Bravo RTU-1
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: °F
custom: {sourcePointName:DAT, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
  source point name: DAT
  data sync recovered: 2020-07-10T01:00:10.745-04:00

Bravo RTU-1 Supply Air Temperature Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sp
has tag: temp
dis: Bravo RTU-1 Supply Air Temperature Setpoint
equip ref: Bravo RTU-1
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: °F
custom: {sourcePointName:DAT STPT, dataSyncRecovered:2020-07-10T01:00:11.258-04:00 New_York, inScope, backgroundPoint}
  source point name: DAT STPT
  data sync recovered: 2020-07-10T01:00:11.258-04:00

Bravo RTU-1 Supply Fan Status
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: fan
has tag: his
has tag: point
has tag: run
has tag: sensor
dis: Bravo RTU-1 Supply Fan Status
equip ref: Bravo RTU-1
kind: Bool
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
custom: {sourcePointName:SF FAN STATUS, dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, inScope, backgroundPoint}
  source point name: SF FAN STATUS
  data sync recovered: 2020-07-10T01:00:09.752-04:00

Bravo RTU-1 TU Air Flow (Auto-computed)
type: his-point
has tag: his
has tag: point
has tag: sp
dis: Bravo RTU-1 TU Air Flow (Auto-computed)
equip ref: Bravo RTU-1
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: cfm
custom: {cache, dataSyncRecovered:2020-07-14T01:00:05.167-04:00 New_York, backgroundPoint}
  data sync recovered: 2020-07-14T01:00:05.167-04:00

Bravo RTU-1 VAV Total Flow
type: computed-point
type: his-point
has tag: air
has tag: computed
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo RTU-1 VAV Total Flow
equip ref: Bravo RTU-1
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: cfm
custom: {dataSyncRecovered:2020-07-14T01:00:05.167-04:00 New_York, backgroundPoint}
  data sync recovered: 2020-07-14T01:00:05.167-04:00

Bravo RTU-2
type: rtu
has tag: ahu
has tag: chilledWaterCooling
has tag: equip
has tag: hotWaterHeating
has tag: hvac
has tag: rtu
has tag: singleDuct
has tag: vavZone
dis: Bravo RTU-2
site ref: Bravo
space ref: Bravo RTUs
custom:
  label: {designDischargeAirFlow:30000cfm, steamHumidifier, designHotWaterLeavingTemp:65°F, designHotWaterPower:288MMBTU/h, designOutsideAirFlowMin:6750cfm, designDischargeFanAirDeltaPressure:6.4inH₂O, designSource:Drawings, designChilledWaterLeavingTemp:59.2°F, designChilledWaterPower:1225.8MMBTU/h, designHotWaterFlow:48gal/min, designChilledWaterFlow:160.9gal/min, designReturnAirFlow:30000cfm, designHotWaterEnteringTemp:75°F, designOutsideAirFlow:30000cfm, designReturnFanPower:25hp, designChilledWaterEnteringTemp:44°F, designDischargeFanPower:50hp, designReturnFanAirDeltaPressure:1.62inH₂O}
  design discharge air flow: 30000
  design hot water leaving temp: 65
  design hot water power: 288
  design outside air flow min: 6750
  design discharge fan air delta pressure: 6.4
  design source: Drawings
  design chilled water leaving temp: 59.2
  design chilled water power: 1225.8
  design hot water flow: 48
  design chilled water flow: 160.9
  design return air flow: 30000
  design hot water entering temp: 75
  design outside air flow: 30000
  design return fan power: 25
  design chilled water entering temp: 44
  design discharge fan power: 50
  design return fan air delta pressure: 1.62

Bravo RTU-2 AHU Operation Mode
type: computed-point
type: his-point
has tag: computed
has tag: his
has tag: point
has tag: sensor
dis: Bravo RTU-2 AHU Operation Mode
equip ref: Bravo RTU-2
kind: Str
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
custom: {mode, dataSyncRecovered:2020-07-14T01:00:05.167-04:00 New_York, backgroundPoint}
  data sync recovered: 2020-07-14T01:00:05.167-04:00

Bravo RTU-2 Calculated Outdoor Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: flow
has tag: his
has tag: outside
has tag: point
has tag: sp
dis: Bravo RTU-2 Calculated Outdoor Air Flow Setpoint
equip ref: Bravo RTU-2
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: %
custom: {predictionConf:0.3970116854281743, sourcePointName:MinOA_SP, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
  prediction conf: 0.3970116854281743
  source point name: MinOA_SP
  data sync recovered: 2020-07-10T01:00:10.745-04:00

Bravo RTU-2 Cooling Valve Output
type: cur-point
type: his-point
has tag: chilled
has tag: cmd
has tag: cool
has tag: cur
has tag: his
has tag: point
has tag: valve
has tag: water
dis: Bravo RTU-2 Cooling Valve Output
equip ref: Bravo RTU-2
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: %
custom: {predictionConf:0.5846394026860828, sourcePointName:CWV, dataSyncRecovered:2020-07-10T01:00:10.995-04:00 New_York, inScope, backgroundPoint}
  prediction conf: 0.5846394026860828
  source point name: CWV
  data sync recovered: 2020-07-10T01:00:10.995-04:00

Bravo RTU-2 Exhaust Air Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: damper
has tag: exhaust
has tag: his
has tag: point
has tag: sensor
dis: Bravo RTU-2 Exhaust Air Damper Output
equip ref: Bravo RTU-2
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: %
custom: {predictionConf:0.6232903565384572, sourcePointName:EAD, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
  prediction conf: 0.6232903565384572
  source point name: EAD
  data sync recovered: 2020-07-10T01:00:10.745-04:00

Bravo RTU-2 Fan Power (Auto-computed)
type: his-point
has tag: his
has tag: point
has tag: sp
dis: Bravo RTU-2 Fan Power (Auto-computed)
equip ref: Bravo RTU-2
kind: Number
site ref: Bravo
tz: Chicago
custom: {cache, dataSyncDownSince:2020-04-09T01:00:02.664-04:00 New_York, dataSyncType:error, backgroundPoint}
  data sync down since: 2020-04-09T01:00:02.664-04:00
  data sync type: error

Bravo RTU-2 Heating/Cooling Load (Auto-computed)
type: his-point
has tag: his
has tag: point
has tag: sp
dis: Bravo RTU-2 Heating/Cooling Load (Auto-computed)
equip ref: Bravo RTU-2
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: BTU/h
custom: {cache, dataSyncRecovered:2020-07-14T01:00:05.167-04:00 New_York, backgroundPoint}
  data sync recovered: 2020-07-14T01:00:05.167-04:00

Bravo RTU-2 Humidifier Enable
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: enable
has tag: his
has tag: humidifier
has tag: point
dis: Bravo RTU-2 Humidifier Enable
equip ref: Bravo RTU-2
kind: Bool
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
custom: {predictionConf:0.2169429859073283, sourcePointName:HUM_ENABLE, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
  prediction conf: 0.2169429859073283
  source point name: HUM_ENABLE
  data sync recovered: 2020-07-10T01:00:10.745-04:00

Bravo RTU-2 Humidifier Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: his
has tag: humidifier
has tag: point
has tag: steam
has tag: valve
dis: Bravo RTU-2 Humidifier Output
equip ref: Bravo RTU-2
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: %
custom: {predictionConf:0.7439557600414519, sourcePointName:HUM VLV, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
  prediction conf: 0.7439557600414519
  source point name: HUM VLV
  data sync recovered: 2020-07-10T01:00:10.003-04:00

Bravo RTU-2 Max Damper Position
type: computed-point
type: his-point
has tag: cmd
has tag: computed
has tag: damper
has tag: his
has tag: point
dis: Bravo RTU-2 Max Damper Position
equip ref: Bravo RTU-2
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: %
custom: {max, dataSyncRecovered:2020-07-14T01:00:05.167-04:00 New_York, backgroundPoint}
  has tag: max
  data sync recovered: 2020-07-14T01:00:05.167-04:00

Bravo RTU-2 Min OA Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo RTU-2 Min OA Flow Setpoint
equip ref: Bravo RTU-2
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: cfm
custom: {predictionConf:0.2305698711556413, sourcePointName:MINOASTPT, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, inScope, outsideMin, backgroundPoint}
  prediction conf: 0.2305698711556413
  source point name: MINOASTPT
  data sync recovered: 2020-07-10T01:00:10.62-04:00

Bravo RTU-2 Min Outdoor Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: flow
has tag: his
has tag: outside
has tag: point
has tag: sensor
dis: Bravo RTU-2 Min Outdoor Air Flow
equip ref: Bravo RTU-2
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: cfm
custom: {predictionConf:0.5591032698291575, min, sourcePointName:MIN OA CFM / 10, dataSyncRecovered:2020-07-10T01:00:10.126-04:00 New_York, inScope, backgroundPoint}
  has tag: min
  prediction conf: 0.5591032698291575
  source point name: MIN OA CFM / 10
  data sync recovered: 2020-07-10T01:00:10.126-04:00

Bravo RTU-2 Minimum Outside Air Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: damper
has tag: his
has tag: point
has tag: sensor
dis: Bravo RTU-2 Minimum Outside Air Damper Output
equip ref: Bravo RTU-2
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: %
custom: {predictionConf:0.7226466689139898, sourcePointName:Min OAD, dataSyncRecovered:2020-07-10T01:00:10.497-04:00 New_York, inScope, outsideMin, backgroundPoint}
  prediction conf: 0.7226466689139898
  source point name: Min OAD
  data sync recovered: 2020-07-10T01:00:10.497-04:00

Bravo RTU-2 Mixed Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: mixed
has tag: point
has tag: sensor
has tag: temp
dis: Bravo RTU-2 Mixed Air Temperature
equip ref: Bravo RTU-2
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: °F
custom: {predictionConf:0.5092275130999935, sourcePointName:MAT, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
  prediction conf: 0.5092275130999935
  source point name: MAT
  data sync recovered: 2020-07-10T01:00:10.003-04:00

Bravo RTU-2 Mixed Air Temperature Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: mixed
has tag: point
has tag: sp
has tag: temp
dis: Bravo RTU-2 Mixed Air Temperature Setpoint
equip ref: Bravo RTU-2
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: °F
custom: {predictionConf:0.41409123546331406, sourcePointName:MAT STPT, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
  prediction conf: 0.41409123546331406
  source point name: MAT STPT
  data sync recovered: 2020-07-10T01:00:10.003-04:00

Bravo RTU-2 Outside Air Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: his
has tag: outside
has tag: point
dis: Bravo RTU-2 Outside Air Damper Output
equip ref: Bravo RTU-2
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: %
custom: {predictionConf:0.7395401248861597, sourcePointName:OAD, dataSyncRecovered:2020-07-10T01:00:10.249-04:00 New_York, inScope, backgroundPoint}
  prediction conf: 0.7395401248861597
  source point name: OAD
  data sync recovered: 2020-07-10T01:00:10.249-04:00

Bravo RTU-2 Outside Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: flow
has tag: his
has tag: outside
has tag: point
has tag: sensor
dis: Bravo RTU-2 Outside Air Flow
equip ref: Bravo RTU-2
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: cfm
custom: {predictionConf:0.7870789837941534, sourcePointName:OA CFM, dataSyncRecovered:2020-07-10T01:00:11.125-04:00 New_York, inScope, backgroundPoint}
  prediction conf: 0.7870789837941534
  source point name: OA CFM
  data sync recovered: 2020-07-10T01:00:11.125-04:00

Bravo RTU-2 Outside Air Percentage (Auto-computed)
type: his-point
has tag: his
has tag: point
has tag: sp
dis: Bravo RTU-2 Outside Air Percentage (Auto-computed)
equip ref: Bravo RTU-2
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
custom: {cache, dataSyncDownSince:2020-03-12T01:00:04.793-04:00 New_York, dataSyncType:error, backgroundPoint}
  data sync down since: 2020-03-12T01:00:04.793-04:00
  data sync type: error

Bravo RTU-2 Percent Outside Air
type: computed-point
type: his-point
has tag: air
has tag: computed
has tag: his
has tag: outside
has tag: point
has tag: sensor
has tag: temp
dis: Bravo RTU-2 Percent Outside Air
equip ref: Bravo RTU-2
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: %
custom: {dataSyncRecovered:2020-07-14T01:00:05.167-04:00 New_York, backgroundPoint}
  data sync recovered: 2020-07-14T01:00:05.167-04:00

Bravo RTU-2 Return Air Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: damper
has tag: his
has tag: point
has tag: return
has tag: sensor
dis: Bravo RTU-2 Return Air Damper Output
equip ref: Bravo RTU-2
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: %
custom: {predictionConf:0.3561100767369028, sourcePointName:RET/REL DAMPER, dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, inScope, backgroundPoint}
  prediction conf: 0.3561100767369028
  source point name: RET/REL DAMPER
  data sync recovered: 2020-07-10T01:00:10.374-04:00

Bravo RTU-2 Return Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: flow
has tag: his
has tag: point
has tag: return
has tag: sensor
dis: Bravo RTU-2 Return Air Flow
equip ref: Bravo RTU-2
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: cfm
custom: {predictionConf:0.8263008623409421, sourcePointName:RA CFM, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
  prediction conf: 0.8263008623409421
  source point name: RA CFM
  data sync recovered: 2020-07-10T01:00:10.003-04:00

Bravo RTU-2 Return Air Humidity
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: humidity
has tag: point
has tag: return
has tag: sensor
dis: Bravo RTU-2 Return Air Humidity
equip ref: Bravo RTU-2
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: %
custom: {predictionConf:0.7016271134196499, sourcePointName:RAH, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
  prediction conf: 0.7016271134196499
  source point name: RAH
  data sync recovered: 2020-07-10T01:00:10.003-04:00

Bravo RTU-2 Return Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: return
has tag: sensor
has tag: temp
dis: Bravo RTU-2 Return Air Temperature
equip ref: Bravo RTU-2
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: °F
custom: {predictionConf:0.5745623242771728, sourcePointName:RAT, dataSyncRecovered:2020-07-10T01:00:10.497-04:00 New_York, inScope, backgroundPoint}
  prediction conf: 0.5745623242771728
  source point name: RAT
  data sync recovered: 2020-07-10T01:00:10.497-04:00

Bravo RTU-2 Return Fan Status
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: fan
has tag: his
has tag: point
has tag: return
has tag: run
has tag: sensor
dis: Bravo RTU-2 Return Fan Status
equip ref: Bravo RTU-2
kind: Bool
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
custom: {predictionConf:0.5721715629985896, sourcePointName:RF FAN STATUS, dataSyncRecovered:2020-07-10T01:00:10.497-04:00 New_York, inScope, backgroundPoint}
  prediction conf: 0.5721715629985896
  source point name: RF FAN STATUS
  data sync recovered: 2020-07-10T01:00:10.497-04:00

Bravo RTU-2 Return Fan VFD Speed
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: fan
has tag: his
has tag: point
has tag: return
has tag: sensor
has tag: speed
dis: Bravo RTU-2 Return Fan VFD Speed
equip ref: Bravo RTU-2
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: %
custom: {predictionConf:0.13813130060214382, sourcePointName:ACT_OUTPUT_SPEED, dataSyncRecovered:2020-07-10T01:00:07.721-04:00 New_York, inScope, backgroundPoint}
  prediction conf: 0.13813130060214382
  source point name: ACT_OUTPUT_SPEED
  data sync recovered: 2020-07-10T01:00:07.721-04:00

Bravo RTU-2 Supply Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo RTU-2 Supply Air Flow
equip ref: Bravo RTU-2
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: cfm
custom: {predictionConf:0.7841375570046363, sourcePointName:SA CFM, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
  prediction conf: 0.7841375570046363
  source point name: SA CFM
  data sync recovered: 2020-07-10T01:00:10.003-04:00

Bravo RTU-2 Supply Air Humidity
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: humidity
has tag: point
has tag: sensor
dis: Bravo RTU-2 Supply Air Humidity
equip ref: Bravo RTU-2
kind: Number
point function: sensor
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: %
custom: {predictionConf:0.7933659564917551, sourcePointName:DAH, dataSyncRecovered:2020-07-10T01:00:10.995-04:00 New_York, inScope, backgroundPoint}
  prediction conf: 0.7933659564917551
  source point name: DAH
  data sync recovered: 2020-07-10T01:00:10.995-04:00

Bravo RTU-2 Supply Air Humidity Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: humidity
has tag: point
has tag: sp
dis: Bravo RTU-2 Supply Air Humidity Setpoint
equip ref: Bravo RTU-2
kind: Number
point function: sp
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: %
custom: {predictionConf:0.7045004074770955, sourcePointName:Humidity SP, dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, inScope, backgroundPoint}
  prediction conf: 0.7045004074770955
  source point name: Humidity SP
  data sync recovered: 2020-07-10T01:00:09.752-04:00

Bravo RTU-2 Supply Air Static Pressure
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: pressure
has tag: sensor
dis: Bravo RTU-2 Supply Air Static Pressure
equip ref: Bravo RTU-2
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: inH₂O
custom: {predictionConf:0.3539915786588711, sourcePointName:DISCH STATIC, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, inScope, backgroundPoint}
  prediction conf: 0.3539915786588711
  source point name: DISCH STATIC
  data sync recovered: 2020-07-10T01:00:10.62-04:00

Bravo RTU-2 Supply Air Static Pressure Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: pressure
has tag: sp
dis: Bravo RTU-2 Supply Air Static Pressure Setpoint
equip ref: Bravo RTU-2
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: inH₂O
custom: {predictionConf:0.48636472322277824, sourcePointName:Static Stpt, dataSyncRecovered:2020-07-10T01:00:13.145-04:00 New_York, inScope, backgroundPoint}
  prediction conf: 0.48636472322277824
  source point name: Static Stpt
  data sync recovered: 2020-07-10T01:00:13.145-04:00

Bravo RTU-2 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo RTU-2 Supply Air Temperature
equip ref: Bravo RTU-2
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: °F
custom: {predictionConf:0.5598774100147106, sourcePointName:DAT, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
  prediction conf: 0.5598774100147106
  source point name: DAT
  data sync recovered: 2020-07-10T01:00:10.745-04:00

Bravo RTU-2 Supply Air Temperature Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sp
has tag: temp
dis: Bravo RTU-2 Supply Air Temperature Setpoint
equip ref: Bravo RTU-2
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: °F
custom: {predictionConf:0.6936845307741977, sourcePointName:DAT STPT, dataSyncRecovered:2020-07-10T01:00:09.879-04:00 New_York, inScope, backgroundPoint}
  prediction conf: 0.6936845307741977
  source point name: DAT STPT
  data sync recovered: 2020-07-10T01:00:09.879-04:00

Bravo RTU-2 Supply Fan Status
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: fan
has tag: his
has tag: point
has tag: run
has tag: sensor
dis: Bravo RTU-2 Supply Fan Status
equip ref: Bravo RTU-2
kind: Bool
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
custom: {predictionConf:0.6818756457191736, sourcePointName:SF FAN STATUS, dataSyncRecovered:2020-07-10T01:00:11.258-04:00 New_York, inScope, backgroundPoint}
  prediction conf: 0.6818756457191736
  source point name: SF FAN STATUS
  data sync recovered: 2020-07-10T01:00:11.258-04:00

Bravo RTU-2 Supply Fan VFD Speed
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: fan
has tag: his
has tag: point
has tag: return
has tag: sensor
has tag: speed
dis: Bravo RTU-2 Supply Fan VFD Speed
equip ref: Bravo RTU-2
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: %
custom: {predictionConf:0.13813130060214382, sourcePointName:ACT_OUTPUT_SPEED, dataSyncRecovered:2020-07-10T01:00:10.87-04:00 New_York, inScope, backgroundPoint}
  prediction conf: 0.13813130060214382
  source point name: ACT_OUTPUT_SPEED
  data sync recovered: 2020-07-10T01:00:10.87-04:00

Bravo RTU-2 TU Air Flow (Auto-computed)
type: his-point
has tag: his
has tag: point
has tag: sp
dis: Bravo RTU-2 TU Air Flow (Auto-computed)
equip ref: Bravo RTU-2
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: cfm
custom: {cache, dataSyncRecovered:2020-07-14T01:00:05.167-04:00 New_York, backgroundPoint}
  data sync recovered: 2020-07-14T01:00:05.167-04:00

Bravo RTU-2 VAV Total Flow
type: computed-point
type: his-point
has tag: air
has tag: computed
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo RTU-2 VAV Total Flow
equip ref: Bravo RTU-2
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: cfm
custom: {dataSyncRecovered:2020-07-14T01:00:05.167-04:00 New_York, backgroundPoint}
  data sync recovered: 2020-07-14T01:00:05.167-04:00

Bravo RTU-3
type: rtu
has tag: ahu
has tag: chilledWaterCooling
has tag: equip
has tag: hotWaterHeating
has tag: hvac
has tag: rtu
has tag: singleDuct
has tag: vavZone
dis: Bravo RTU-3
site ref: Bravo
space ref: Bravo RTUs
custom:
  label: {designDischargeAirFlow:33600cfm, steamHumidifier, designHotWaterLeavingTemp:65°F, designHotWaterPower:318MMBTU/h, designOutsideAirFlowMin:7125cfm, designDischargeFanAirDeltaPressure:6.7inH₂O, designSource:Drawings, designChilledWaterLeavingTemp:58.9°F, designChilledWaterPower:1346.1MMBTU/h, designHotWaterFlow:53gal/min, designChilledWaterFlow:180.2gal/min, designReturnAirFlow:33600cfm, designHotWaterEnteringTemp:75°F, designOutsideAirFlow:33600cfm, designReturnFanPower:25hp, designChilledWaterEnteringTemp:44°F, designDischargeFanPower:60hp, designReturnFanAirDeltaPressure:1.63inH₂O}
  design discharge air flow: 33600
  design hot water leaving temp: 65
  design hot water power: 318
  design outside air flow min: 7125
  design discharge fan air delta pressure: 6.7
  design source: Drawings
  design chilled water leaving temp: 58.9
  design chilled water power: 1346.1
  design hot water flow: 53
  design chilled water flow: 180.2
  design return air flow: 33600
  design hot water entering temp: 75
  design outside air flow: 33600
  design return fan power: 25
  design chilled water entering temp: 44
  design discharge fan power: 60
  design return fan air delta pressure: 1.63

Bravo RTU-3 AHU Operation Mode
type: computed-point
type: his-point
has tag: computed
has tag: his
has tag: point
has tag: sensor
dis: Bravo RTU-3 AHU Operation Mode
equip ref: Bravo RTU-3
kind: Str
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
custom: {mode, dataSyncRecovered:2020-07-14T01:00:05.167-04:00 New_York, backgroundPoint}
  data sync recovered: 2020-07-14T01:00:05.167-04:00

Bravo RTU-3 Cooling Valve Output
type: cur-point
type: his-point
has tag: chilled
has tag: cmd
has tag: cool
has tag: cur
has tag: his
has tag: point
has tag: valve
has tag: water
dis: Bravo RTU-3 Cooling Valve Output
equip ref: Bravo RTU-3
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: %
custom: {predictionConf:0.5846394026860828, sourcePointName:CWV, dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, inScope, backgroundPoint}
  prediction conf: 0.5846394026860828
  source point name: CWV
  data sync recovered: 2020-07-10T01:00:10.374-04:00

Bravo RTU-3 Exhaust Air Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: damper
has tag: exhaust
has tag: his
has tag: point
has tag: sensor
dis: Bravo RTU-3 Exhaust Air Damper Output
equip ref: Bravo RTU-3
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: %
custom: {predictionConf:0.6232903565384572, sourcePointName:EAD, dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, inScope, backgroundPoint}
  prediction conf: 0.6232903565384572
  source point name: EAD
  data sync recovered: 2020-07-10T01:00:10.374-04:00

Bravo RTU-3 Fan Power (Auto-computed)
type: his-point
has tag: his
has tag: point
has tag: sp
dis: Bravo RTU-3 Fan Power (Auto-computed)
equip ref: Bravo RTU-3
kind: Number
site ref: Bravo
tz: Chicago
custom: {cache, dataSyncDownSince:2020-04-09T01:00:02.664-04:00 New_York, dataSyncType:error, backgroundPoint}
  data sync down since: 2020-04-09T01:00:02.664-04:00
  data sync type: error

Bravo RTU-3 Heating/Cooling Load (Auto-computed)
type: his-point
has tag: his
has tag: point
has tag: sp
dis: Bravo RTU-3 Heating/Cooling Load (Auto-computed)
equip ref: Bravo RTU-3
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: BTU/h
custom: {cache, dataSyncRecovered:2020-07-14T01:00:05.167-04:00 New_York, backgroundPoint}
  data sync recovered: 2020-07-14T01:00:05.167-04:00

Bravo RTU-3 Humidifier Enable
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: enable
has tag: his
has tag: humidifier
has tag: point
dis: Bravo RTU-3 Humidifier Enable
equip ref: Bravo RTU-3
kind: Bool
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
custom: {predictionConf:0.2169429859073283, sourcePointName:HUM_ENABLE, dataSyncRecovered:2020-07-10T01:00:07.598-04:00 New_York, inScope, backgroundPoint}
  prediction conf: 0.2169429859073283
  source point name: HUM_ENABLE
  data sync recovered: 2020-07-10T01:00:07.598-04:00

Bravo RTU-3 Humidifier Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: his
has tag: humidifier
has tag: point
has tag: steam
has tag: valve
dis: Bravo RTU-3 Humidifier Output
equip ref: Bravo RTU-3
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: %
custom: {predictionConf:0.7439557600414519, sourcePointName:HUM VLV, dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, inScope, backgroundPoint}
  prediction conf: 0.7439557600414519
  source point name: HUM VLV
  data sync recovered: 2020-07-10T01:00:10.374-04:00

Bravo RTU-3 Max Damper Position
type: computed-point
type: his-point
has tag: cmd
has tag: computed
has tag: damper
has tag: his
has tag: point
dis: Bravo RTU-3 Max Damper Position
equip ref: Bravo RTU-3
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: %
custom: {max, dataSyncRecovered:2020-07-14T01:00:05.167-04:00 New_York, backgroundPoint}
  has tag: max
  data sync recovered: 2020-07-14T01:00:05.167-04:00

Bravo RTU-3 Min OA Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo RTU-3 Min OA Flow Setpoint
equip ref: Bravo RTU-3
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: cfm
custom: {predictionConf:0.2305698711556413, sourcePointName:MINOASTPT, dataSyncRecovered:2020-07-10T01:00:10.126-04:00 New_York, inScope, outsideMin, backgroundPoint}
  prediction conf: 0.2305698711556413
  source point name: MINOASTPT
  data sync recovered: 2020-07-10T01:00:10.126-04:00

Bravo RTU-3 Minimum Outside Air Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: damper
has tag: his
has tag: point
has tag: sensor
dis: Bravo RTU-3 Minimum Outside Air Damper Output
equip ref: Bravo RTU-3
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: %
custom: {predictionConf:0.7226466689139898, sourcePointName:Min OAD, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, outsideMin, backgroundPoint}
  prediction conf: 0.7226466689139898
  source point name: Min OAD
  data sync recovered: 2020-07-10T01:00:10.745-04:00

Bravo RTU-3 Mixed Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: mixed
has tag: point
has tag: sensor
has tag: temp
dis: Bravo RTU-3 Mixed Air Temperature
equip ref: Bravo RTU-3
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: °F
custom: {predictionConf:0.5092275130999935, sourcePointName:MAT, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
  prediction conf: 0.5092275130999935
  source point name: MAT
  data sync recovered: 2020-07-10T01:00:10.003-04:00

Bravo RTU-3 Mixed Air Temperature Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: mixed
has tag: point
has tag: sp
has tag: temp
dis: Bravo RTU-3 Mixed Air Temperature Setpoint
equip ref: Bravo RTU-3
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: °F
custom: {predictionConf:0.41409123546331406, sourcePointName:MAT STPT, dataSyncRecovered:2020-07-10T01:00:11.125-04:00 New_York, inScope, backgroundPoint}
  prediction conf: 0.41409123546331406
  source point name: MAT STPT
  data sync recovered: 2020-07-10T01:00:11.125-04:00

Bravo RTU-3 Outside Air Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: his
has tag: outside
has tag: point
dis: Bravo RTU-3 Outside Air Damper Output
equip ref: Bravo RTU-3
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: %
custom: {predictionConf:0.7395401248861597, sourcePointName:OAD, dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, inScope, backgroundPoint}
  prediction conf: 0.7395401248861597
  source point name: OAD
  data sync recovered: 2020-07-10T01:00:09.752-04:00

Bravo RTU-3 Outside Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: flow
has tag: his
has tag: outside
has tag: point
has tag: sensor
dis: Bravo RTU-3 Outside Air Flow
equip ref: Bravo RTU-3
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: cfm
custom: {predictionConf:0.7870789837941534, sourcePointName:OA CFM, dataSyncRecovered:2020-07-10T01:00:07.473-04:00 New_York, inScope, backgroundPoint}
  prediction conf: 0.7870789837941534
  source point name: OA CFM
  data sync recovered: 2020-07-10T01:00:07.473-04:00

Bravo RTU-3 Outside Air Percentage (Auto-computed)
type: his-point
has tag: his
has tag: point
has tag: sp
dis: Bravo RTU-3 Outside Air Percentage (Auto-computed)
equip ref: Bravo RTU-3
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
custom: {cache, dataSyncDownSince:2020-03-12T01:00:04.793-04:00 New_York, dataSyncType:error, backgroundPoint}
  data sync down since: 2020-03-12T01:00:04.793-04:00
  data sync type: error

Bravo RTU-3 Percent Outside Air
type: computed-point
type: his-point
has tag: air
has tag: computed
has tag: his
has tag: outside
has tag: point
has tag: sensor
has tag: temp
dis: Bravo RTU-3 Percent Outside Air
equip ref: Bravo RTU-3
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: %
custom: {dataSyncRecovered:2020-07-14T01:00:05.167-04:00 New_York, backgroundPoint}
  data sync recovered: 2020-07-14T01:00:05.167-04:00

Bravo RTU-3 Return Air Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: his
has tag: point
has tag: return
dis: Bravo RTU-3 Return Air Damper Output
equip ref: Bravo RTU-3
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: %
custom: {predictionConf:0.3561100767369028, sourcePointName:RET/REL DAMPER, dataSyncRecovered:2020-07-10T01:00:09.879-04:00 New_York, inScope, backgroundPoint}
  prediction conf: 0.3561100767369028
  source point name: RET/REL DAMPER
  data sync recovered: 2020-07-10T01:00:09.879-04:00

Bravo RTU-3 Return Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: flow
has tag: his
has tag: point
has tag: return
has tag: sensor
dis: Bravo RTU-3 Return Air Flow
equip ref: Bravo RTU-3
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: cfm
custom: {predictionConf:0.8263008623409421, sourcePointName:RA CFM, dataSyncRecovered:2020-07-10T01:00:13.145-04:00 New_York, inScope, backgroundPoint}
  prediction conf: 0.8263008623409421
  source point name: RA CFM
  data sync recovered: 2020-07-10T01:00:13.145-04:00

Bravo RTU-3 Return Air Humidity
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: humidity
has tag: point
has tag: return
has tag: sensor
dis: Bravo RTU-3 Return Air Humidity
equip ref: Bravo RTU-3
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: %
custom: {predictionConf:0.7016271134196499, sourcePointName:RAH, dataSyncRecovered:2020-07-10T01:00:09.879-04:00 New_York, inScope, backgroundPoint}
  prediction conf: 0.7016271134196499
  source point name: RAH
  data sync recovered: 2020-07-10T01:00:09.879-04:00

Bravo RTU-3 Return Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: return
has tag: sensor
has tag: temp
dis: Bravo RTU-3 Return Air Temperature
equip ref: Bravo RTU-3
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: °F
custom: {predictionConf:0.5745623242771728, sourcePointName:RAT, dataSyncRecovered:2020-07-10T01:00:10.126-04:00 New_York, inScope, backgroundPoint}
  prediction conf: 0.5745623242771728
  source point name: RAT
  data sync recovered: 2020-07-10T01:00:10.126-04:00

Bravo RTU-3 Return Fan Status
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: fan
has tag: his
has tag: point
has tag: return
has tag: run
has tag: sensor
dis: Bravo RTU-3 Return Fan Status
equip ref: Bravo RTU-3
kind: Bool
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
custom: {predictionConf:0.5721715629985896, sourcePointName:RF FAN STATUS, dataSyncRecovered:2020-07-10T01:00:10.497-04:00 New_York, inScope, backgroundPoint}
  prediction conf: 0.5721715629985896
  source point name: RF FAN STATUS
  data sync recovered: 2020-07-10T01:00:10.497-04:00

Bravo RTU-3 Return Fan VFD Speed
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: fan
has tag: his
has tag: point
has tag: return
has tag: sensor
has tag: speed
dis: Bravo RTU-3 Return Fan VFD Speed
equip ref: Bravo RTU-3
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: %
custom: {predictionConf:0.3324288739189246, sourcePointName:RTDrvSpd, dataSyncRecovered:2020-07-10T01:00:07.721-04:00 New_York, inScope, backgroundPoint}
  prediction conf: 0.3324288739189246
  source point name: RTDrvSpd
  data sync recovered: 2020-07-10T01:00:07.721-04:00

Bravo RTU-3 Supply Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo RTU-3 Supply Air Flow
equip ref: Bravo RTU-3
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: cfm
custom: {predictionConf:0.7841375570046363, sourcePointName:SA CFM, dataSyncRecovered:2020-07-10T01:00:07.473-04:00 New_York, inScope, backgroundPoint}
  prediction conf: 0.7841375570046363
  source point name: SA CFM
  data sync recovered: 2020-07-10T01:00:07.473-04:00

Bravo RTU-3 Supply Air Humidity
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: humidity
has tag: point
has tag: sensor
dis: Bravo RTU-3 Supply Air Humidity
equip ref: Bravo RTU-3
kind: Number
point function: sensor
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: %
custom: {predictionConf:0.7933659564917551, sourcePointName:DAH, dataSyncRecovered:2020-07-10T01:00:07.598-04:00 New_York, inScope, backgroundPoint}
  prediction conf: 0.7933659564917551
  source point name: DAH
  data sync recovered: 2020-07-10T01:00:07.598-04:00

Bravo RTU-3 Supply Air Pressure Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: pressure
has tag: sp
dis: Bravo RTU-3 Supply Air Pressure Setpoint
equip ref: Bravo RTU-3
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: inH₂O
custom: {predictionConf:0.48636472322277824, static, sourcePointName:Static Stpt, dataSyncRecovered:2020-07-10T01:00:13.145-04:00 New_York, inScope, backgroundPoint}
  prediction conf: 0.48636472322277824
  source point name: Static Stpt
  data sync recovered: 2020-07-10T01:00:13.145-04:00

Bravo RTU-3 Supply Air Static Pressure
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: pressure
has tag: sensor
dis: Bravo RTU-3 Supply Air Static Pressure
equip ref: Bravo RTU-3
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: inH₂O
custom: {predictionConf:0.3539915786588711, sourcePointName:DISCH STATIC, dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, inScope, backgroundPoint}
  prediction conf: 0.3539915786588711
  source point name: DISCH STATIC
  data sync recovered: 2020-07-10T01:00:10.374-04:00

Bravo RTU-3 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo RTU-3 Supply Air Temperature
equip ref: Bravo RTU-3
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: °F
custom: {predictionConf:0.5598774100147106, sourcePointName:DAT, dataSyncRecovered:2020-07-10T01:00:10.87-04:00 New_York, inScope, backgroundPoint}
  prediction conf: 0.5598774100147106
  source point name: DAT
  data sync recovered: 2020-07-10T01:00:10.87-04:00

Bravo RTU-3 Supply Air Temperature Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sp
has tag: temp
dis: Bravo RTU-3 Supply Air Temperature Setpoint
equip ref: Bravo RTU-3
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: °F
custom: {predictionConf:0.6936845307741977, sourcePointName:DAT STPT, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, inScope, backgroundPoint}
  prediction conf: 0.6936845307741977
  source point name: DAT STPT
  data sync recovered: 2020-07-10T01:00:10.62-04:00

Bravo RTU-3 Supply Fan Status
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: fan
has tag: his
has tag: point
has tag: run
has tag: sensor
dis: Bravo RTU-3 Supply Fan Status
equip ref: Bravo RTU-3
kind: Bool
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
custom: {predictionConf:0.6818756457191736, sourcePointName:SF FAN STATUS, dataSyncRecovered:2020-07-10T01:00:10.995-04:00 New_York, inScope, backgroundPoint}
  prediction conf: 0.6818756457191736
  source point name: SF FAN STATUS
  data sync recovered: 2020-07-10T01:00:10.995-04:00

Bravo RTU-3 Supply Fan VFD Speed
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: fan
has tag: his
has tag: point
has tag: sensor
has tag: speed
dis: Bravo RTU-3 Supply Fan VFD Speed
equip ref: Bravo RTU-3
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: %
custom: {predictionConf:0.32036669663302475, sourcePointName:SPDrvSpd, dataSyncRecovered:2020-07-10T01:00:09.879-04:00 New_York, inScope, backgroundPoint}
  prediction conf: 0.32036669663302475
  source point name: SPDrvSpd
  data sync recovered: 2020-07-10T01:00:09.879-04:00

Bravo RTU-3 TU Air Flow (Auto-computed)
type: his-point
has tag: his
has tag: point
has tag: sp
dis: Bravo RTU-3 TU Air Flow (Auto-computed)
equip ref: Bravo RTU-3
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: cfm
custom: {cache, dataSyncRecovered:2020-07-14T01:00:05.167-04:00 New_York, backgroundPoint}
  data sync recovered: 2020-07-14T01:00:05.167-04:00

Bravo RTU-3 VAV Total Flow
type: computed-point
type: his-point
has tag: air
has tag: computed
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo RTU-3 VAV Total Flow
equip ref: Bravo RTU-3
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: cfm
custom: {dataSyncRecovered:2020-07-14T01:00:05.167-04:00 New_York, backgroundPoint}
  data sync recovered: 2020-07-14T01:00:05.167-04:00

Bravo RTU-4
type: rtu
has tag: ahu
has tag: chilledWaterCooling
has tag: equip
has tag: hotWaterHeating
has tag: hvac
has tag: rtu
has tag: singleDuct
has tag: vavZone
dis: Bravo RTU-4
site ref: Bravo
space ref: Bravo RTUs
custom:
  label: {designDischargeAirFlow:15700cfm, steamHumidifier, designHotWaterLeavingTemp:65°F, designHotWaterPower:243MMBTU/h, designOutsideAirFlowMin:7125cfm, designDischargeFanAirDeltaPressure:4.76inH₂O, designSource:Drawings, designChilledWaterLeavingTemp:58.9°F, designChilledWaterPower:1028.7MMBTU/h, designHotWaterFlow:41gal/min, designChilledWaterFlow:137.8gal/min, designReturnAirFlow:25700cfm, designHotWaterEnteringTemp:75°F, designOutsideAirFlow:25700cfm, designReturnFanPower:20hp, designChilledWaterEnteringTemp:44°F, designDischargeFanPower:40hp, designReturnFanAirDeltaPressure:1.64inH₂O}
  design discharge air flow: 15700
  design hot water leaving temp: 65
  design hot water power: 243
  design outside air flow min: 7125
  design discharge fan air delta pressure: 4.76
  design source: Drawings
  design chilled water leaving temp: 58.9
  design chilled water power: 1028.7
  design hot water flow: 41
  design chilled water flow: 137.8
  design return air flow: 25700
  design hot water entering temp: 75
  design outside air flow: 25700
  design return fan power: 20
  design chilled water entering temp: 44
  design discharge fan power: 40
  design return fan air delta pressure: 1.64

Bravo RTU-4 AHU Operation Mode
type: computed-point
type: his-point
has tag: computed
has tag: his
has tag: point
has tag: sensor
dis: Bravo RTU-4 AHU Operation Mode
equip ref: Bravo RTU-4
kind: Str
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
custom: {mode, dataSyncRecovered:2020-07-14T01:00:05.167-04:00 New_York, backgroundPoint}
  data sync recovered: 2020-07-14T01:00:05.167-04:00

Bravo RTU-4 Cooling Valve Output
type: cur-point
type: his-point
has tag: chilled
has tag: cmd
has tag: cool
has tag: cur
has tag: his
has tag: point
has tag: valve
has tag: water
dis: Bravo RTU-4 Cooling Valve Output
equip ref: Bravo RTU-4
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: %
custom: {sourcePointName:CWV, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, inScope, backgroundPoint}
  source point name: CWV
  data sync recovered: 2020-07-10T01:00:10.62-04:00

Bravo RTU-4 Exhaust Air Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: damper
has tag: exhaust
has tag: his
has tag: point
has tag: sensor
dis: Bravo RTU-4 Exhaust Air Damper Output
equip ref: Bravo RTU-4
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: %
custom: {sourcePointName:EAD, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
  source point name: EAD
  data sync recovered: 2020-07-10T01:00:10.745-04:00

Bravo RTU-4 Fan Power (Auto-computed)
type: his-point
has tag: his
has tag: point
has tag: sp
dis: Bravo RTU-4 Fan Power (Auto-computed)
equip ref: Bravo RTU-4
kind: Number
site ref: Bravo
tz: Chicago
custom: {cache, dataSyncDownSince:2020-04-09T01:00:02.664-04:00 New_York, dataSyncType:error, backgroundPoint}
  data sync down since: 2020-04-09T01:00:02.664-04:00
  data sync type: error

Bravo RTU-4 Heating/Cooling Load (Auto-computed)
type: his-point
has tag: his
has tag: point
has tag: sp
dis: Bravo RTU-4 Heating/Cooling Load (Auto-computed)
equip ref: Bravo RTU-4
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: BTU/h
custom: {cache, dataSyncRecovered:2020-07-14T01:00:05.167-04:00 New_York, backgroundPoint}
  data sync recovered: 2020-07-14T01:00:05.167-04:00

Bravo RTU-4 Humidifier Enable
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: enable
has tag: his
has tag: humidifier
has tag: point
dis: Bravo RTU-4 Humidifier Enable
equip ref: Bravo RTU-4
kind: Bool
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
custom: {sourcePointName:HUM_ENABLE, dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, inScope, backgroundPoint}
  source point name: HUM_ENABLE
  data sync recovered: 2020-07-10T01:00:10.374-04:00

Bravo RTU-4 Humidifier Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: his
has tag: humidifier
has tag: point
has tag: steam
has tag: valve
dis: Bravo RTU-4 Humidifier Output
equip ref: Bravo RTU-4
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: %
custom: {sourcePointName:HUM VLV, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, inScope, backgroundPoint}
  source point name: HUM VLV
  data sync recovered: 2020-07-10T01:00:10.62-04:00

Bravo RTU-4 Max Damper Position
type: computed-point
type: his-point
has tag: cmd
has tag: computed
has tag: damper
has tag: his
has tag: point
dis: Bravo RTU-4 Max Damper Position
equip ref: Bravo RTU-4
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: %
custom: {max, dataSyncRecovered:2020-07-14T01:00:05.167-04:00 New_York, backgroundPoint}
  has tag: max
  data sync recovered: 2020-07-14T01:00:05.167-04:00

Bravo RTU-4 Min Outdoor Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: flow
has tag: his
has tag: outside
has tag: point
has tag: sp
dis: Bravo RTU-4 Min Outdoor Air Flow Setpoint
equip ref: Bravo RTU-4
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: %
custom: {min, sourcePointName:MinOA_SP, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, pointType:, inScope, backgroundPoint}
  has tag: min
  source point name: MinOA_SP
  data sync recovered: 2020-07-10T01:00:10.62-04:00

Bravo RTU-4 Min Outdoor Air Flow/10
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: flow
has tag: his
has tag: outside
has tag: point
has tag: sensor
dis: Bravo RTU-4 Min Outdoor Air Flow/10
equip ref: Bravo RTU-4
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: cfm
custom: {min, sourcePointName:MIN OA CFM / 10, dataSyncRecovered:2020-07-10T01:00:10.87-04:00 New_York, inScope, backgroundPoint}
  has tag: min
  source point name: MIN OA CFM / 10
  data sync recovered: 2020-07-10T01:00:10.87-04:00

Bravo RTU-4 Minimum Outside Air Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: damper
has tag: his
has tag: point
has tag: sensor
dis: Bravo RTU-4 Minimum Outside Air Damper Output
equip ref: Bravo RTU-4
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: %
custom: {sourcePointName:Min OAD, dataSyncRecovered:2020-07-10T01:00:09.879-04:00 New_York, inScope, outsideMin, backgroundPoint}
  source point name: Min OAD
  data sync recovered: 2020-07-10T01:00:09.879-04:00

Bravo RTU-4 Mixed Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: mixed
has tag: point
has tag: sensor
has tag: temp
dis: Bravo RTU-4 Mixed Air Temperature
equip ref: Bravo RTU-4
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: °F
custom: {sourcePointName:MAT, dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, inScope, backgroundPoint}
  source point name: MAT
  data sync recovered: 2020-07-10T01:00:09.752-04:00

Bravo RTU-4 Mixed Air Temperature Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: mixed
has tag: point
has tag: sp
has tag: temp
dis: Bravo RTU-4 Mixed Air Temperature Setpoint
equip ref: Bravo RTU-4
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: °F
custom: {sourcePointName:MAT STPT, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
  source point name: MAT STPT
  data sync recovered: 2020-07-10T01:00:10.745-04:00

Bravo RTU-4 Outside Air Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: his
has tag: outside
has tag: point
dis: Bravo RTU-4 Outside Air Damper Output
equip ref: Bravo RTU-4
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: %
custom: {sourcePointName:OAD, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
  source point name: OAD
  data sync recovered: 2020-07-10T01:00:10.745-04:00

Bravo RTU-4 Outside Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: flow
has tag: his
has tag: outside
has tag: point
has tag: sensor
dis: Bravo RTU-4 Outside Air Flow
equip ref: Bravo RTU-4
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: cfm
custom: {sourcePointName:OA CFM, dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, inScope, backgroundPoint}
  source point name: OA CFM
  data sync recovered: 2020-07-10T01:00:10.374-04:00

Bravo RTU-4 Outside Air Percentage (Auto-computed)
type: his-point
has tag: his
has tag: point
has tag: sp
dis: Bravo RTU-4 Outside Air Percentage (Auto-computed)
equip ref: Bravo RTU-4
kind: Number
site ref: Bravo
tz: Chicago
custom: {cache, dataSyncDownSince:2020-04-09T01:00:02.664-04:00 New_York, dataSyncType:error, backgroundPoint}
  data sync down since: 2020-04-09T01:00:02.664-04:00
  data sync type: error

Bravo RTU-4 Percent Outside Air
type: computed-point
type: his-point
has tag: air
has tag: computed
has tag: his
has tag: outside
has tag: point
has tag: sensor
has tag: temp
dis: Bravo RTU-4 Percent Outside Air
equip ref: Bravo RTU-4
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: %
custom: {dataSyncRecovered:2020-07-14T01:00:05.167-04:00 New_York, backgroundPoint}
  data sync recovered: 2020-07-14T01:00:05.167-04:00

Bravo RTU-4 Return Air Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: damper
has tag: his
has tag: point
has tag: return
has tag: sensor
dis: Bravo RTU-4 Return Air Damper Output
equip ref: Bravo RTU-4
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: %
custom: {sourcePointName:RET/REL DAMPER, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, pointType:, inScope, backgroundPoint}
  source point name: RET/REL DAMPER
  data sync recovered: 2020-07-10T01:00:10.003-04:00

Bravo RTU-4 Return Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: flow
has tag: his
has tag: point
has tag: return
has tag: sensor
dis: Bravo RTU-4 Return Air Flow
equip ref: Bravo RTU-4
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: cfm
custom: {sourcePointName:RA CFM, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
  source point name: RA CFM
  data sync recovered: 2020-07-10T01:00:10.745-04:00

Bravo RTU-4 Return Air Humidity
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: humidity
has tag: point
has tag: return
has tag: sensor
dis: Bravo RTU-4 Return Air Humidity
equip ref: Bravo RTU-4
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: %
custom: {sourcePointName:RAH, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, inScope, backgroundPoint}
  source point name: RAH
  data sync recovered: 2020-07-10T01:00:10.62-04:00

Bravo RTU-4 Return Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: return
has tag: sensor
has tag: temp
dis: Bravo RTU-4 Return Air Temperature
equip ref: Bravo RTU-4
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: °F
custom: {sourcePointName:RAT, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, inScope, backgroundPoint}
  source point name: RAT
  data sync recovered: 2020-07-10T01:00:10.62-04:00

Bravo RTU-4 Return Fan Status
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: fan
has tag: his
has tag: point
has tag: return
has tag: run
has tag: sensor
dis: Bravo RTU-4 Return Fan Status
equip ref: Bravo RTU-4
kind: Bool
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
custom: {sourcePointName:RF FAN STATUS, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, inScope, backgroundPoint}
  source point name: RF FAN STATUS
  data sync recovered: 2020-07-10T01:00:10.62-04:00

Bravo RTU-4 Return Fan VFD Speed
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: fan
has tag: his
has tag: point
has tag: return
has tag: sensor
has tag: speed
dis: Bravo RTU-4 Return Fan VFD Speed
equip ref: Bravo RTU-4
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: %
custom: {sourcePointName:ACT_OUTPUT_SPEED, dataSyncRecovered:2020-07-10T01:00:10.126-04:00 New_York, inScope, backgroundPoint}
  source point name: ACT_OUTPUT_SPEED
  data sync recovered: 2020-07-10T01:00:10.126-04:00

Bravo RTU-4 Supply Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo RTU-4 Supply Air Flow
equip ref: Bravo RTU-4
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: cfm
custom: {sourcePointName:SA CFM, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, inScope, backgroundPoint}
  source point name: SA CFM
  data sync recovered: 2020-07-10T01:00:10.62-04:00

Bravo RTU-4 Supply Air Humidity
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: humidity
has tag: point
has tag: sensor
dis: Bravo RTU-4 Supply Air Humidity
equip ref: Bravo RTU-4
kind: Number
point function: sensor
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: %
custom: {sourcePointName:DAH, dataSyncRecovered:2020-07-10T01:00:07.598-04:00 New_York, inScope, backgroundPoint}
  source point name: DAH
  data sync recovered: 2020-07-10T01:00:07.598-04:00

Bravo RTU-4 Supply Air Humidity Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: humidity
has tag: point
has tag: sp
dis: Bravo RTU-4 Supply Air Humidity Setpoint
equip ref: Bravo RTU-4
kind: Number
point function: sp
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: %
custom: {sourcePointName:Humidity SP, dataSyncRecovered:2020-07-10T01:00:13.145-04:00 New_York, inScope, backgroundPoint}
  source point name: Humidity SP
  data sync recovered: 2020-07-10T01:00:13.145-04:00

Bravo RTU-4 Supply Air Pressure Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: pressure
has tag: sp
dis: Bravo RTU-4 Supply Air Pressure Setpoint
equip ref: Bravo RTU-4
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: inH₂O
custom: {static, sourcePointName:Static Stpt, dataSyncRecovered:2020-07-10T01:00:07.598-04:00 New_York, inScope, backgroundPoint}
  source point name: Static Stpt
  data sync recovered: 2020-07-10T01:00:07.598-04:00

Bravo RTU-4 Supply Air Static Pressure
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: pressure
has tag: sensor
dis: Bravo RTU-4 Supply Air Static Pressure
equip ref: Bravo RTU-4
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: inH₂O
custom: {sourcePointName:DISCH STATIC, dataSyncRecovered:2020-07-10T01:00:07.473-04:00 New_York, inScope, backgroundPoint}
  source point name: DISCH STATIC
  data sync recovered: 2020-07-10T01:00:07.473-04:00

Bravo RTU-4 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo RTU-4 Supply Air Temperature
equip ref: Bravo RTU-4
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: °F
custom: {sourcePointName:DAT, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
  source point name: DAT
  data sync recovered: 2020-07-10T01:00:10.745-04:00

Bravo RTU-4 Supply Air Temperature Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sp
has tag: temp
dis: Bravo RTU-4 Supply Air Temperature Setpoint
equip ref: Bravo RTU-4
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: °F
custom: {sourcePointName:DAT STPT, dataSyncRecovered:2020-07-10T01:00:11.125-04:00 New_York, inScope, backgroundPoint}
  source point name: DAT STPT
  data sync recovered: 2020-07-10T01:00:11.125-04:00

Bravo RTU-4 Supply Fan Status
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: fan
has tag: his
has tag: point
has tag: run
has tag: sensor
dis: Bravo RTU-4 Supply Fan Status
equip ref: Bravo RTU-4
kind: Bool
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
custom: {sourcePointName:SF FAN STATUS, dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, inScope, backgroundPoint}
  source point name: SF FAN STATUS
  data sync recovered: 2020-07-10T01:00:10.374-04:00

Bravo RTU-4 TU Air Flow (Auto-computed)
type: his-point
has tag: his
has tag: point
has tag: sp
dis: Bravo RTU-4 TU Air Flow (Auto-computed)
equip ref: Bravo RTU-4
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: cfm
custom: {cache, dataSyncDownSince:2020-03-12T01:00:04.793-04:00 New_York, dataSyncType:error, backgroundPoint}
  data sync down since: 2020-03-12T01:00:04.793-04:00
  data sync type: error

Bravo RTU-4 VAV Total Flow
type: computed-point
type: his-point
has tag: air
has tag: computed
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo RTU-4 VAV Total Flow
equip ref: Bravo RTU-4
kind: Number
site ref: Bravo
space ref: Bravo RTUs
tz: Chicago
unit: cfm
custom: {dataSyncRecovered:2020-07-14T01:00:05.167-04:00 New_York, backgroundPoint}
  data sync recovered: 2020-07-14T01:00:05.167-04:00

Bravo RTUs
type: space
has tag: space
dis: Bravo RTUs
site ref: Bravo
custom: {equipType}

Bravo Steam Boiler A Boiler Status
type: boiler
type: cur-point
type: his-point
has tag: boiler
has tag: cur
has tag: his
has tag: point
has tag: run
has tag: sensor
dis: Bravo Steam Boiler A Boiler Status
equip ref: Bravo Steam Boiler A
  type: boiler
  has tag: boiler
  has tag: equip
  has tag: hvac
  dis: Bravo Steam Boiler A
  site ref: Bravo
  space ref: Bravo Steam System
  custom: {designSource:Drawings, designMake:Lattner, designSteamPower:1350MMBTU/h, designModel:WLF-40}
    design source: Drawings
    design make: Lattner
    design steam power: 1350
    design model: WLF-40
kind: Bool
site ref: Bravo
space ref: Bravo Steam System
tz: Chicago
custom: {sourcePointName:StmBlrAsts, dataSyncRecovered:2020-07-10T01:00:10.126-04:00 New_York, inScope, backgroundPoint}
  source point name: StmBlrAsts
  data sync recovered: 2020-07-10T01:00:10.126-04:00

Bravo Steam Boiler B Boiler Status
type: boiler
type: cur-point
type: his-point
has tag: boiler
has tag: cur
has tag: his
has tag: point
has tag: run
has tag: sensor
dis: Bravo Steam Boiler B Boiler Status
equip ref: Bravo Steam Boiler B
  type: boiler
  has tag: boiler
  has tag: equip
  has tag: hvac
  dis: Bravo Steam Boiler B
  site ref: Bravo
  space ref: Bravo Steam System
  custom: {designSource:Drawings, designMake:Lattner, designSteamPower:1350MMBTU/h, designModel:WLF-40}
    design source: Drawings
    design make: Lattner
    design steam power: 1350
    design model: WLF-40
kind: Bool
site ref: Bravo
space ref: Bravo Steam System
tz: Chicago
custom: {sourcePointName:StmBlrBsts, dataSyncRecovered:2020-07-10T01:00:09.627-04:00 New_York, inScope, backgroundPoint}
  source point name: StmBlrBsts
  data sync recovered: 2020-07-10T01:00:09.627-04:00

Bravo Steam Boiler C Boiler Status
type: boiler
type: cur-point
type: his-point
has tag: boiler
has tag: cur
has tag: his
has tag: point
has tag: run
has tag: sensor
dis: Bravo Steam Boiler C Boiler Status
equip ref: Bravo Steam Boiler C
  type: boiler
  has tag: boiler
  has tag: equip
  has tag: hvac
  dis: Bravo Steam Boiler C
  site ref: Bravo
  space ref: Bravo Steam System
  custom: {designSource:Drawings, designMake:Lattner, designSteamPower:1350MMBTU/h, designModel:WLF-40}
    design source: Drawings
    design make: Lattner
    design steam power: 1350
    design model: WLF-40
kind: Bool
site ref: Bravo
space ref: Bravo Steam System
tz: Chicago
custom: {sourcePointName:StmBlrCsts, dataSyncRecovered:2020-07-10T01:00:10.995-04:00 New_York, inScope, backgroundPoint}
  source point name: StmBlrCsts
  data sync recovered: 2020-07-10T01:00:10.995-04:00

Bravo Steam System
type: space
has tag: space
dis: Bravo Steam System
site ref: Bravo
custom: {equipType}

Bravo VAV 1-1
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-1
dis: Bravo VAV 1-1
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:152°F, designHotWaterPower:9.7MMBTU/h, designHotWaterFlow:1gal/min, designAirFlow:400cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 152
  design hot water power: 9.7
  design hot water flow: 1
  design air flow: 400

Bravo VAV 1-1 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 1-1 Damper Output
equip ref: Bravo VAV 1-1
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:07.598-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:07.598-04:00

Bravo VAV 1-1 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 1-1 Discharge Air Flow
equip ref: Bravo VAV 1-1
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:09.752-04:00

Bravo VAV 1-1 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 1-1 Discharge Air Flow Setpoint
equip ref: Bravo VAV 1-1
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:10.003-04:00

Bravo VAV 1-1 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 1-1 Heating Valve Output
equip ref: Bravo VAV 1-1
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:07.473-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:07.473-04:00

Bravo VAV 1-1 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 1-1 Zone Air Temp Setpoint
equip ref: Bravo VAV 1-1
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:11.125-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:11.125-04:00

Bravo VAV 1-1 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 1-1 Zone Temperature
equip ref: Bravo VAV 1-1
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:11.258-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:11.258-04:00

Bravo VAV 1-10
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-1
dis: Bravo VAV 1-10
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:149°F, designHotWaterPower:6.5MMBTU/h, designHotWaterFlow:0.75gal/min, designAirFlow:375cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 149
  design hot water power: 6.5
  design hot water flow: 0.75
  design air flow: 375

Bravo VAV 1-10 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 1-10 Damper Output
equip ref: Bravo VAV 1-10
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:11.125-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:11.125-04:00

Bravo VAV 1-10 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 1-10 Discharge Air Flow
equip ref: Bravo VAV 1-10
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:13.145-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:13.145-04:00

Bravo VAV 1-10 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 1-10 Discharge Air Flow Setpoint
equip ref: Bravo VAV 1-10
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:07.598-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:07.598-04:00

Bravo VAV 1-10 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 1-10 Heating Valve Output
equip ref: Bravo VAV 1-10
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:11.125-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:11.125-04:00

Bravo VAV 1-10 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 1-10 Supply Air Temperature
equip ref: Bravo VAV 1-10
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:10.87-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:10.87-04:00

Bravo VAV 1-10 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 1-10 Zone Air Temp Setpoint
equip ref: Bravo VAV 1-10
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:11.258-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:11.258-04:00

Bravo VAV 1-10 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 1-10 Zone Temperature
equip ref: Bravo VAV 1-10
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:10.126-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:10.126-04:00

Bravo VAV 1-11
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-1
dis: Bravo VAV 1-11
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:152°F, designHotWaterPower:10.2MMBTU/h, designHotWaterFlow:1gal/min, designAirFlow:300cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 152
  design hot water power: 10.2
  design hot water flow: 1
  design air flow: 300

Bravo VAV 1-11 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 1-11 Damper Output
equip ref: Bravo VAV 1-11
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:13.145-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:13.145-04:00

Bravo VAV 1-11 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 1-11 Discharge Air Flow
equip ref: Bravo VAV 1-11
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:10.87-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:10.87-04:00

Bravo VAV 1-11 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 1-11 Discharge Air Flow Setpoint
equip ref: Bravo VAV 1-11
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:10.249-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:10.249-04:00

Bravo VAV 1-11 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 1-11 Heating Valve Output
equip ref: Bravo VAV 1-11
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:10.126-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:10.126-04:00

Bravo VAV 1-11 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 1-11 Supply Air Temperature
equip ref: Bravo VAV 1-11
kind: Str
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:13.145-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:13.145-04:00

Bravo VAV 1-11 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 1-11 Zone Air Temp Setpoint
equip ref: Bravo VAV 1-11
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:10.497-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:10.497-04:00

Bravo VAV 1-11 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 1-11 Zone Temperature
equip ref: Bravo VAV 1-11
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:07.473-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:07.473-04:00

Bravo VAV 1-12
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-1
dis: Bravo VAV 1-12
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:152°F, designHotWaterPower:10.2MMBTU/h, designHotWaterFlow:1gal/min, designAirFlow:500cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 152
  design hot water power: 10.2
  design hot water flow: 1
  design air flow: 500

Bravo VAV 1-12 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 1-12 Damper Output
equip ref: Bravo VAV 1-12
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:11.258-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:11.258-04:00

Bravo VAV 1-12 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 1-12 Discharge Air Flow
equip ref: Bravo VAV 1-12
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:10.126-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:10.126-04:00

Bravo VAV 1-12 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 1-12 Discharge Air Flow Setpoint
equip ref: Bravo VAV 1-12
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:09.752-04:00

Bravo VAV 1-12 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 1-12 Heating Valve Output
equip ref: Bravo VAV 1-12
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:13.145-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:13.145-04:00

Bravo VAV 1-12 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 1-12 Supply Air Temperature
equip ref: Bravo VAV 1-12
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:10.003-04:00

Bravo VAV 1-12 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 1-12 Zone Air Temp Setpoint
equip ref: Bravo VAV 1-12
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:13.145-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:13.145-04:00

Bravo VAV 1-12 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 1-12 Zone Temperature
equip ref: Bravo VAV 1-12
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:10.126-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:10.126-04:00

Bravo VAV 1-13
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-1
dis: Bravo VAV 1-13
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:149°F, designHotWaterPower:27MMBTU/h, designHotWaterFlow:3gal/min, designAirFlow:1000cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 149
  design hot water power: 27
  design hot water flow: 3
  design air flow: 1000

Bravo VAV 1-13 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 1-13 Damper Output
equip ref: Bravo VAV 1-13
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:09.752-04:00

Bravo VAV 1-13 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 1-13 Discharge Air Flow
equip ref: Bravo VAV 1-13
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:13.145-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:13.145-04:00

Bravo VAV 1-13 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 1-13 Discharge Air Flow Setpoint
equip ref: Bravo VAV 1-13
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:07.473-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:07.473-04:00

Bravo VAV 1-13 Heating Valve
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 1-13 Heating Valve
equip ref: Bravo VAV 1-13
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:07.598-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:07.598-04:00

Bravo VAV 1-13 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 1-13 Supply Air Temperature
equip ref: Bravo VAV 1-13
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:10.003-04:00

Bravo VAV 1-13 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 1-13 Zone Air Temp Setpoint
equip ref: Bravo VAV 1-13
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:10.62-04:00

Bravo VAV 1-13 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 1-13 Zone Temperature
equip ref: Bravo VAV 1-13
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:10.87-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:10.87-04:00

Bravo VAV 1-14
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-1
dis: Bravo VAV 1-14
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:152°F, designHotWaterPower:4.5MMBTU/h, designHotWaterFlow:0.75gal/min, designAirFlow:250cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 152
  design hot water power: 4.5
  design hot water flow: 0.75
  design air flow: 250

Bravo VAV 1-14 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 1-14 Damper Output
equip ref: Bravo VAV 1-14
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:09.879-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:09.879-04:00

Bravo VAV 1-14 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 1-14 Discharge Air Flow
equip ref: Bravo VAV 1-14
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:13.145-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:13.145-04:00

Bravo VAV 1-14 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 1-14 Discharge Air Flow Setpoint
equip ref: Bravo VAV 1-14
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:10.995-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:10.995-04:00

Bravo VAV 1-14 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 1-14 Heating Valve Output
equip ref: Bravo VAV 1-14
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:10.745-04:00

Bravo VAV 1-14 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 1-14 Supply Air Temperature
equip ref: Bravo VAV 1-14
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:07.721-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:07.721-04:00

Bravo VAV 1-14 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 1-14 Zone Air Temp Setpoint
equip ref: Bravo VAV 1-14
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:10.249-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:10.249-04:00

Bravo VAV 1-14 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 1-14 Zone Temperature
equip ref: Bravo VAV 1-14
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:10.374-04:00

Bravo VAV 1-15
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-1
dis: Bravo VAV 1-15
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:150°F, designHotWaterPower:6MMBTU/h, designHotWaterFlow:1gal/min, designAirFlow:400cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 150
  design hot water power: 6
  design hot water flow: 1
  design air flow: 400

Bravo VAV 1-15 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 1-15 Damper Output
equip ref: Bravo VAV 1-15
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:10.745-04:00

Bravo VAV 1-15 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 1-15 Discharge Air Flow
equip ref: Bravo VAV 1-15
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:10.87-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:10.87-04:00

Bravo VAV 1-15 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 1-15 Discharge Air Flow Setpoint
equip ref: Bravo VAV 1-15
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:07.721-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:07.721-04:00

Bravo VAV 1-15 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 1-15 Heating Valve Output
equip ref: Bravo VAV 1-15
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:10.374-04:00

Bravo VAV 1-15 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 1-15 Supply Air Temperature
equip ref: Bravo VAV 1-15
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, pointType:, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:10.003-04:00

Bravo VAV 1-15 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 1-15 Zone Air Temp Setpoint
equip ref: Bravo VAV 1-15
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:11.258-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:11.258-04:00

Bravo VAV 1-15 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 1-15 Zone Temperature
equip ref: Bravo VAV 1-15
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:10.003-04:00

Bravo VAV 1-16
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-1
dis: Bravo VAV 1-16
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:152°F, designHotWaterPower:4.1MMBTU/h, designHotWaterFlow:0.75gal/min, designAirFlow:300cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 152
  design hot water power: 4.1
  design hot water flow: 0.75
  design air flow: 300

Bravo VAV 1-16 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 1-16 Damper Output
equip ref: Bravo VAV 1-16
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:10.003-04:00

Bravo VAV 1-16 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 1-16 Discharge Air Flow
equip ref: Bravo VAV 1-16
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:10.497-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:10.497-04:00

Bravo VAV 1-16 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 1-16 Discharge Air Flow Setpoint
equip ref: Bravo VAV 1-16
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:10.003-04:00

Bravo VAV 1-16 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 1-16 Heating Valve Output
equip ref: Bravo VAV 1-16
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:10.374-04:00

Bravo VAV 1-16 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 1-16 Supply Air Temperature
equip ref: Bravo VAV 1-16
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:10.249-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:10.249-04:00

Bravo VAV 1-16 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 1-16 Zone Air Temp Setpoint
equip ref: Bravo VAV 1-16
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:07.598-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:07.598-04:00

Bravo VAV 1-16 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 1-16 Zone Temperature
equip ref: Bravo VAV 1-16
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:10.87-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:10.87-04:00

Bravo VAV 1-17
type: thermostat
type: vav
has tag: equip
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-1
dis: Bravo VAV 1-17
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:150°F, designHotWaterPower:6MMBTU/h, designHotWaterFlow:1gal/min, designAirFlow:400cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 150
  design hot water power: 6
  design hot water flow: 1
  design air flow: 400

Bravo VAV 1-17 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 1-17 Damper Output
equip ref: Bravo VAV 1-17
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:10.249-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:10.249-04:00

Bravo VAV 1-17 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 1-17 Discharge Air Flow
equip ref: Bravo VAV 1-17
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:10.249-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:10.249-04:00

Bravo VAV 1-17 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 1-17 Discharge Air Flow Setpoint
equip ref: Bravo VAV 1-17
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:10.995-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:10.995-04:00

Bravo VAV 1-17 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 1-17 Heating Valve Output
equip ref: Bravo VAV 1-17
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:11.258-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:11.258-04:00

Bravo VAV 1-17 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 1-17 Supply Air Temperature
equip ref: Bravo VAV 1-17
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:10.497-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:10.497-04:00

Bravo VAV 1-17 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 1-17 Zone Air Temp Setpoint
equip ref: Bravo VAV 1-17
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:10.249-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:10.249-04:00

Bravo VAV 1-17 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 1-17 Zone Temperature
equip ref: Bravo VAV 1-17
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:13.145-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:13.145-04:00

Bravo VAV 1-18
type: thermostat
type: vav
has tag: equip
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-1
dis: Bravo VAV 1-18
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:152°F, designHotWaterPower:4.1MMBTU/h, designHotWaterFlow:0.75gal/min, designAirFlow:300cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 152
  design hot water power: 4.1
  design hot water flow: 0.75
  design air flow: 300

Bravo VAV 1-18 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 1-18 Damper Output
equip ref: Bravo VAV 1-18
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:10.249-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:10.249-04:00

Bravo VAV 1-18 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 1-18 Discharge Air Flow
equip ref: Bravo VAV 1-18
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:07.721-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:07.721-04:00

Bravo VAV 1-18 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 1-18 Discharge Air Flow Setpoint
equip ref: Bravo VAV 1-18
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:10.126-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:10.126-04:00

Bravo VAV 1-18 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 1-18 Heating Valve Output
equip ref: Bravo VAV 1-18
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:09.752-04:00

Bravo VAV 1-18 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 1-18 Supply Air Temperature
equip ref: Bravo VAV 1-18
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:10.249-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:10.249-04:00

Bravo VAV 1-18 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 1-18 Zone Air Temp Setpoint
equip ref: Bravo VAV 1-18
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:10.126-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:10.126-04:00

Bravo VAV 1-18 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 1-18 Zone Temperature
equip ref: Bravo VAV 1-18
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:10.745-04:00

Bravo VAV 1-19
type: thermostat
type: vav
has tag: equip
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-1
dis: Bravo VAV 1-19
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:150°F, designHotWaterPower:30.9MMBTU/h, designHotWaterFlow:1.45gal/min, designAirFlow:2400cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 150
  design hot water power: 30.9
  design hot water flow: 1.45
  design air flow: 2400

Bravo VAV 1-19 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 1-19 Damper Output
equip ref: Bravo VAV 1-19
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:09.879-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:09.879-04:00

Bravo VAV 1-19 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 1-19 Discharge Air Flow
equip ref: Bravo VAV 1-19
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:09.879-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:09.879-04:00

Bravo VAV 1-19 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 1-19 Discharge Air Flow Setpoint
equip ref: Bravo VAV 1-19
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:10.249-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:10.249-04:00

Bravo VAV 1-19 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 1-19 Heating Valve Output
equip ref: Bravo VAV 1-19
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:09.627-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:09.627-04:00

Bravo VAV 1-19 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 1-19 Supply Air Temperature
equip ref: Bravo VAV 1-19
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:11.258-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:11.258-04:00

Bravo VAV 1-19 Zone Air Humidity
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: humidity
has tag: point
has tag: sensor
has tag: zone
dis: Bravo VAV 1-19 Zone Air Humidity
equip ref: Bravo VAV 1-19
kind: Number
point function: sensor
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {predictionConf:0.6984488664169048, sourcePointName:Humidity, dataSyncRecovered:2020-07-10T01:00:10.87-04:00 New_York, inScope, backgroundPoint}
  prediction conf: 0.6984488664169048
  source point name: Humidity
  data sync recovered: 2020-07-10T01:00:10.87-04:00

Bravo VAV 1-19 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 1-19 Zone Air Temp Setpoint
equip ref: Bravo VAV 1-19
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:10.87-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:10.87-04:00

Bravo VAV 1-19 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 1-19 Zone Temperature
equip ref: Bravo VAV 1-19
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:09.627-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:09.627-04:00

Bravo VAV 1-2
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-1
dis: Bravo VAV 1-2
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:150°F, designHotWaterPower:17.5MMBTU/h, designHotWaterFlow:2gal/min, designAirFlow:500cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 150
  design hot water power: 17.5
  design hot water flow: 2
  design air flow: 500

Bravo VAV 1-2 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 1-2 Damper Output
equip ref: Bravo VAV 1-2
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:10.62-04:00

Bravo VAV 1-2 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 1-2 Discharge Air Flow
equip ref: Bravo VAV 1-2
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:10.745-04:00

Bravo VAV 1-2 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 1-2 Discharge Air Flow Setpoint
equip ref: Bravo VAV 1-2
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:10.995-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:10.995-04:00

Bravo VAV 1-2 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 1-2 Heating Valve Output
equip ref: Bravo VAV 1-2
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:10.126-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:10.126-04:00

Bravo VAV 1-2 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 1-2 Supply Air Temperature
equip ref: Bravo VAV 1-2
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:10.745-04:00

Bravo VAV 1-2 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 1-2 Zone Air Temp Setpoint
equip ref: Bravo VAV 1-2
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:10.374-04:00

Bravo VAV 1-2 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 1-2 Zone Temperature
equip ref: Bravo VAV 1-2
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:10.126-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:10.126-04:00

Bravo VAV 1-20
type: thermostat
type: vav
has tag: equip
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-1
dis: Bravo VAV 1-20
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:151°F, designHotWaterPower:10.8MMBTU/h, designHotWaterFlow:0.28gal/min, designAirFlow:800cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 151
  design hot water power: 10.8
  design hot water flow: 0.28
  design air flow: 800

Bravo VAV 1-20 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 1-20 Damper Output
equip ref: Bravo VAV 1-20
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:10.003-04:00

Bravo VAV 1-20 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 1-20 Discharge Air Flow
equip ref: Bravo VAV 1-20
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:10.126-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:10.126-04:00

Bravo VAV 1-20 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 1-20 Discharge Air Flow Setpoint
equip ref: Bravo VAV 1-20
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:13.145-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:13.145-04:00

Bravo VAV 1-20 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 1-20 Heating Valve Output
equip ref: Bravo VAV 1-20
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:10.87-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:10.87-04:00

Bravo VAV 1-20 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 1-20 Supply Air Temperature
equip ref: Bravo VAV 1-20
kind: Str
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:09.879-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:09.879-04:00

Bravo VAV 1-20 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 1-20 Zone Air Temp Setpoint
equip ref: Bravo VAV 1-20
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:09.752-04:00

Bravo VAV 1-20 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 1-20 Zone Temperature
equip ref: Bravo VAV 1-20
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:10.126-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:10.126-04:00

Bravo VAV 1-3
type: thermostat
type: vav
has tag: equip
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-1
dis: Bravo VAV 1-3
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:152°F, designHotWaterPower:83.5MMBTU/h, designHotWaterFlow:12gal/min, designAirFlow:3000cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 152
  design hot water power: 83.5
  design hot water flow: 12
  design air flow: 3000

Bravo VAV 1-3 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 1-3 Damper Output
equip ref: Bravo VAV 1-3
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:07.721-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:07.721-04:00

Bravo VAV 1-3 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 1-3 Discharge Air Flow
equip ref: Bravo VAV 1-3
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:09.627-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:09.627-04:00

Bravo VAV 1-3 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 1-3 Discharge Air Flow Setpoint
equip ref: Bravo VAV 1-3
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:10.62-04:00

Bravo VAV 1-3 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 1-3 Heating Valve Output
equip ref: Bravo VAV 1-3
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:11.258-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:11.258-04:00

Bravo VAV 1-3 Supply Air Humidity
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: humidity
has tag: point
has tag: sensor
dis: Bravo VAV 1-3 Supply Air Humidity
equip ref: Bravo VAV 1-3
kind: Number
point function: sensor
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DisChgrHumid, dataSyncRecovered:2020-07-10T01:00:10.249-04:00 New_York, backgroundPoint}
  source point name: DisChgrHumid
  data sync recovered: 2020-07-10T01:00:10.249-04:00

Bravo VAV 1-3 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 1-3 Supply Air Temperature
equip ref: Bravo VAV 1-3
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:10.374-04:00

Bravo VAV 1-3 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 1-3 Zone Air Temp Setpoint
equip ref: Bravo VAV 1-3
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:10.497-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:10.497-04:00

Bravo VAV 1-3 Zone Relative Humidity
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: humidity
has tag: point
has tag: sensor
has tag: zone
dis: Bravo VAV 1-3 Zone Relative Humidity
equip ref: Bravo VAV 1-3
kind: Number
point function: sensor
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {predictionConf:0.7237593125289187, sourcePointName:SpaceHum, dataSyncRecovered:2020-07-10T01:00:10.249-04:00 New_York, inScope, backgroundPoint}
  prediction conf: 0.7237593125289187
  source point name: SpaceHum
  data sync recovered: 2020-07-10T01:00:10.249-04:00

Bravo VAV 1-3 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 1-3 Zone Temperature
equip ref: Bravo VAV 1-3
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:07.473-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:07.473-04:00

Bravo VAV 1-4
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-1
dis: Bravo VAV 1-4
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:152°F, designHotWaterPower:3.8MMBTU/h, designHotWaterFlow:0.75gal/min, designAirFlow:300cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 152
  design hot water power: 3.8
  design hot water flow: 0.75
  design air flow: 300

Bravo VAV 1-4 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 1-4 Damper Output
equip ref: Bravo VAV 1-4
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:11.258-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:11.258-04:00

Bravo VAV 1-4 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 1-4 Discharge Air Flow
equip ref: Bravo VAV 1-4
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:10.497-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:10.497-04:00

Bravo VAV 1-4 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 1-4 Discharge Air Flow Setpoint
equip ref: Bravo VAV 1-4
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:10.374-04:00

Bravo VAV 1-4 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 1-4 Heating Valve Output
equip ref: Bravo VAV 1-4
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:13.145-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:13.145-04:00

Bravo VAV 1-4 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 1-4 Supply Air Temperature
equip ref: Bravo VAV 1-4
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:09.627-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:09.627-04:00

Bravo VAV 1-4 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 1-4 Zone Air Temp Setpoint
equip ref: Bravo VAV 1-4
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:10.745-04:00

Bravo VAV 1-4 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 1-4 Zone Temperature
equip ref: Bravo VAV 1-4
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:07.473-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:07.473-04:00

Bravo VAV 1-5
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-1
dis: Bravo VAV 1-5
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:152°F, designHotWaterPower:10.5MMBTU/h, designHotWaterFlow:1.5gal/min, designAirFlow:450cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 152
  design hot water power: 10.5
  design hot water flow: 1.5
  design air flow: 450

Bravo VAV 1-5 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 1-5 Damper Output
equip ref: Bravo VAV 1-5
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:10.374-04:00

Bravo VAV 1-5 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 1-5 Discharge Air Flow
equip ref: Bravo VAV 1-5
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:10.995-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:10.995-04:00

Bravo VAV 1-5 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 1-5 Discharge Air Flow Setpoint
equip ref: Bravo VAV 1-5
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:09.752-04:00

Bravo VAV 1-5 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 1-5 Heating Valve Output
equip ref: Bravo VAV 1-5
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:09.752-04:00

Bravo VAV 1-5 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 1-5 Supply Air Temperature
equip ref: Bravo VAV 1-5
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:10.374-04:00

Bravo VAV 1-5 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 1-5 Zone Air Temp Setpoint
equip ref: Bravo VAV 1-5
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:10.745-04:00

Bravo VAV 1-5 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 1-5 Zone Temperature
equip ref: Bravo VAV 1-5
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:10.249-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:10.249-04:00

Bravo VAV 1-6
type: thermostat
type: vav
has tag: equip
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-1
dis: Bravo VAV 1-6
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:152°F, designHotWaterPower:83.5MMBTU/h, designHotWaterFlow:12gal/min, designAirFlow:3000cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 152
  design hot water power: 83.5
  design hot water flow: 12
  design air flow: 3000

Bravo VAV 1-6 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 1-6 Damper Output
equip ref: Bravo VAV 1-6
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:07.721-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:07.721-04:00

Bravo VAV 1-6 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 1-6 Discharge Air Flow
equip ref: Bravo VAV 1-6
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:10.87-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:10.87-04:00

Bravo VAV 1-6 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 1-6 Discharge Air Flow Setpoint
equip ref: Bravo VAV 1-6
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:10.745-04:00

Bravo VAV 1-6 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 1-6 Heating Valve Output
equip ref: Bravo VAV 1-6
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:10.995-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:10.995-04:00

Bravo VAV 1-6 Supply Air Humidity
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: humidity
has tag: point
has tag: sensor
dis: Bravo VAV 1-6 Supply Air Humidity
equip ref: Bravo VAV 1-6
kind: Number
point function: sensor
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DisChgrHumid, dataSyncRecovered:2020-07-10T01:00:07.598-04:00 New_York, backgroundPoint}
  source point name: DisChgrHumid
  data sync recovered: 2020-07-10T01:00:07.598-04:00

Bravo VAV 1-6 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 1-6 Supply Air Temperature
equip ref: Bravo VAV 1-6
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:10.249-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:10.249-04:00

Bravo VAV 1-6 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 1-6 Zone Air Temp Setpoint
equip ref: Bravo VAV 1-6
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:10.745-04:00

Bravo VAV 1-6 Zone Relative Humidity
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: humidity
has tag: point
has tag: sensor
has tag: zone
dis: Bravo VAV 1-6 Zone Relative Humidity
equip ref: Bravo VAV 1-6
kind: Number
point function: sensor
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:SpaceHum, dataSyncRecovered:2020-07-10T01:00:11.258-04:00 New_York, inScope, backgroundPoint}
  source point name: SpaceHum
  data sync recovered: 2020-07-10T01:00:11.258-04:00

Bravo VAV 1-6 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 1-6 Zone Temperature
equip ref: Bravo VAV 1-6
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:07.598-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:07.598-04:00

Bravo VAV 1-7
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-1
dis: Bravo VAV 1-7
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:152°F, designHotWaterPower:7.6MMBTU/h, designHotWaterFlow:1.25gal/min, designAirFlow:450cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 152
  design hot water power: 7.6
  design hot water flow: 1.25
  design air flow: 450

Bravo VAV 1-7 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 1-7 Damper Output
equip ref: Bravo VAV 1-7
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:07.598-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:07.598-04:00

Bravo VAV 1-7 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 1-7 Discharge Air Flow
equip ref: Bravo VAV 1-7
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:07.721-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:07.721-04:00

Bravo VAV 1-7 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 1-7 Discharge Air Flow Setpoint
equip ref: Bravo VAV 1-7
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:10.87-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:10.87-04:00

Bravo VAV 1-7 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 1-7 Heating Valve Output
equip ref: Bravo VAV 1-7
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:10.87-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:10.87-04:00

Bravo VAV 1-7 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 1-7 Supply Air Temperature
equip ref: Bravo VAV 1-7
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:09.752-04:00

Bravo VAV 1-7 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 1-7 Zone Air Temp Setpoint
equip ref: Bravo VAV 1-7
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:10.995-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:10.995-04:00

Bravo VAV 1-7 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 1-7 Zone Temperature
equip ref: Bravo VAV 1-7
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:09.752-04:00

Bravo VAV 1-8
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-1
dis: Bravo VAV 1-8
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:150°F, designHotWaterPower:4.8MMBTU/h, designHotWaterFlow:0.75gal/min, designAirFlow:300cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 150
  design hot water power: 4.8
  design hot water flow: 0.75
  design air flow: 300

Bravo VAV 1-8 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 1-8 Damper Output
equip ref: Bravo VAV 1-8
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:09.752-04:00

Bravo VAV 1-8 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 1-8 Discharge Air Flow
equip ref: Bravo VAV 1-8
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:07.721-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:07.721-04:00

Bravo VAV 1-8 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 1-8 Discharge Air Flow Setpoint
equip ref: Bravo VAV 1-8
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:09.627-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:09.627-04:00

Bravo VAV 1-8 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 1-8 Heating Valve Output
equip ref: Bravo VAV 1-8
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:07.598-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:07.598-04:00

Bravo VAV 1-8 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 1-8 Supply Air Temperature
equip ref: Bravo VAV 1-8
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:09.627-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:09.627-04:00

Bravo VAV 1-8 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 1-8 Zone Air Temp Setpoint
equip ref: Bravo VAV 1-8
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:10.249-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:10.249-04:00

Bravo VAV 1-8 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 1-8 Zone Temperature
equip ref: Bravo VAV 1-8
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:10.374-04:00

Bravo VAV 1-9
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-1
dis: Bravo VAV 1-9
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:149°F, designHotWaterPower:15.3MMBTU/h, designHotWaterFlow:1.75gal/min, designAirFlow:875cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 149
  design hot water power: 15.3
  design hot water flow: 1.75
  design air flow: 875

Bravo VAV 1-9 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 1-9 Damper Output
equip ref: Bravo VAV 1-9
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:09.627-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:09.627-04:00

Bravo VAV 1-9 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 1-9 Discharge Air Flow
equip ref: Bravo VAV 1-9
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:09.879-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:09.879-04:00

Bravo VAV 1-9 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 1-9 Discharge Air Flow Setpoint
equip ref: Bravo VAV 1-9
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:09.627-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:09.627-04:00

Bravo VAV 1-9 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 1-9 Heating Valve Output
equip ref: Bravo VAV 1-9
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:10.62-04:00

Bravo VAV 1-9 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 1-9 Supply Air Temperature
equip ref: Bravo VAV 1-9
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:10.87-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:10.87-04:00

Bravo VAV 1-9 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 1-9 Zone Air Temp Setpoint
equip ref: Bravo VAV 1-9
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:09.879-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:09.879-04:00

Bravo VAV 1-9 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 1-9 Zone Temperature
equip ref: Bravo VAV 1-9
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:09.879-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:09.879-04:00

Bravo VAV 2-1
type: thermostat
type: vav
has tag: equip
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-2
dis: Bravo VAV 2-1
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:149°F, designHotWaterPower:8.9MMBTU/h, designHotWaterFlow:1gal/min, designAirFlow:450cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 149
  design hot water power: 8.9
  design hot water flow: 1
  design air flow: 450

Bravo VAV 2-1 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 2-1 Damper Output
equip ref: Bravo VAV 2-1
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:10.249-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:10.249-04:00

Bravo VAV 2-1 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 2-1 Discharge Air Flow
equip ref: Bravo VAV 2-1
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:10.87-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:10.87-04:00

Bravo VAV 2-1 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 2-1 Discharge Air Flow Setpoint
equip ref: Bravo VAV 2-1
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:10.87-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:10.87-04:00

Bravo VAV 2-1 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 2-1 Heating Valve Output
equip ref: Bravo VAV 2-1
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:07.598-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:07.598-04:00

Bravo VAV 2-1 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 2-1 Supply Air Temperature
equip ref: Bravo VAV 2-1
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:10.995-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:10.995-04:00

Bravo VAV 2-1 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 2-1 Zone Air Temp Setpoint
equip ref: Bravo VAV 2-1
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:10.003-04:00

Bravo VAV 2-1 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 2-1 Zone Temperature
equip ref: Bravo VAV 2-1
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:10.497-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:10.497-04:00

Bravo VAV 2-10
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-2
dis: Bravo VAV 2-10
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:151°F, designHotWaterPower:4.3MMBTU/h, designHotWaterFlow:0.75gal/min, designAirFlow:175cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 151
  design hot water power: 4.3
  design hot water flow: 0.75
  design air flow: 175

Bravo VAV 2-10 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 2-10 Damper Output
equip ref: Bravo VAV 2-10
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:10.995-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:10.995-04:00

Bravo VAV 2-10 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 2-10 Discharge Air Flow
equip ref: Bravo VAV 2-10
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:10.003-04:00

Bravo VAV 2-10 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 2-10 Discharge Air Flow Setpoint
equip ref: Bravo VAV 2-10
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:10.126-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:10.126-04:00

Bravo VAV 2-10 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 2-10 Heating Valve Output
equip ref: Bravo VAV 2-10
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:07.473-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:07.473-04:00

Bravo VAV 2-10 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 2-10 Supply Air Temperature
equip ref: Bravo VAV 2-10
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:07.721-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:07.721-04:00

Bravo VAV 2-10 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 2-10 Zone Air Temp Setpoint
equip ref: Bravo VAV 2-10
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:07.473-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:07.473-04:00

Bravo VAV 2-10 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 2-10 Zone Temperature
equip ref: Bravo VAV 2-10
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:10.249-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:10.249-04:00

Bravo VAV 2-11
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-2
dis: Bravo VAV 2-11
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:149°F, designHotWaterPower:9.2MMBTU/h, designHotWaterFlow:1gal/min, designAirFlow:450cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 149
  design hot water power: 9.2
  design hot water flow: 1
  design air flow: 450

Bravo VAV 2-11 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 2-11 Damper Output
equip ref: Bravo VAV 2-11
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:09.752-04:00

Bravo VAV 2-11 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 2-11 Discharge Air Flow
equip ref: Bravo VAV 2-11
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:09.879-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:09.879-04:00

Bravo VAV 2-11 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 2-11 Discharge Air Flow Setpoint
equip ref: Bravo VAV 2-11
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:09.627-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:09.627-04:00

Bravo VAV 2-11 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 2-11 Heating Valve Output
equip ref: Bravo VAV 2-11
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:10.87-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:10.87-04:00

Bravo VAV 2-11 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 2-11 Supply Air Temperature
equip ref: Bravo VAV 2-11
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:13.145-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:13.145-04:00

Bravo VAV 2-11 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 2-11 Zone Air Temp Setpoint
equip ref: Bravo VAV 2-11
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:09.752-04:00

Bravo VAV 2-11 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 2-11 Zone Temperature
equip ref: Bravo VAV 2-11
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:07.598-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:07.598-04:00

Bravo VAV 2-12
type: thermostat
type: vav
has tag: equip
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-2
dis: Bravo VAV 2-12
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:152°F, designHotWaterPower:4.6MMBTU/h, designHotWaterFlow:0.75gal/min, designAirFlow:250cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 152
  design hot water power: 4.6
  design hot water flow: 0.75
  design air flow: 250

Bravo VAV 2-12 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 2-12 Damper Output
equip ref: Bravo VAV 2-12
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:10.374-04:00

Bravo VAV 2-12 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 2-12 Discharge Air Flow
equip ref: Bravo VAV 2-12
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:10.497-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:10.497-04:00

Bravo VAV 2-12 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 2-12 Discharge Air Flow Setpoint
equip ref: Bravo VAV 2-12
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:09.752-04:00

Bravo VAV 2-12 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 2-12 Heating Valve Output
equip ref: Bravo VAV 2-12
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:10.497-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:10.497-04:00

Bravo VAV 2-12 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 2-12 Supply Air Temperature
equip ref: Bravo VAV 2-12
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:10.995-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:10.995-04:00

Bravo VAV 2-12 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 2-12 Zone Air Temp Setpoint
equip ref: Bravo VAV 2-12
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:09.627-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:09.627-04:00

Bravo VAV 2-12 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 2-12 Zone Temperature
equip ref: Bravo VAV 2-12
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:10.87-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:10.87-04:00

Bravo VAV 2-13
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-2
dis: Bravo VAV 2-13
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:149°F, designHotWaterPower:8.9MMBTU/h, designHotWaterFlow:1gal/min, designAirFlow:450cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 149
  design hot water power: 8.9
  design hot water flow: 1
  design air flow: 450

Bravo VAV 2-13 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 2-13 Damper Output
equip ref: Bravo VAV 2-13
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:10.126-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:10.126-04:00

Bravo VAV 2-13 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 2-13 Discharge Air Flow
equip ref: Bravo VAV 2-13
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:07.473-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:07.473-04:00

Bravo VAV 2-13 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 2-13 Discharge Air Flow Setpoint
equip ref: Bravo VAV 2-13
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:10.003-04:00

Bravo VAV 2-13 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 2-13 Heating Valve Output
equip ref: Bravo VAV 2-13
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:10.126-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:10.126-04:00

Bravo VAV 2-13 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 2-13 Supply Air Temperature
equip ref: Bravo VAV 2-13
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:10.126-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:10.126-04:00

Bravo VAV 2-13 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 2-13 Zone Air Temp Setpoint
equip ref: Bravo VAV 2-13
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:10.62-04:00

Bravo VAV 2-13 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 2-13 Zone Temperature
equip ref: Bravo VAV 2-13
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:10.249-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:10.249-04:00

Bravo VAV 2-14
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-2
dis: Bravo VAV 2-14
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:150°F, designHotWaterPower:24.2MMBTU/h, designHotWaterFlow:2.5gal/min, designAirFlow:1450cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 150
  design hot water power: 24.2
  design hot water flow: 2.5
  design air flow: 1450

Bravo VAV 2-14 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 2-14 Damper Output
equip ref: Bravo VAV 2-14
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:13.145-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:13.145-04:00

Bravo VAV 2-14 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 2-14 Discharge Air Flow
equip ref: Bravo VAV 2-14
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:10.249-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:10.249-04:00

Bravo VAV 2-14 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 2-14 Discharge Air Flow Setpoint
equip ref: Bravo VAV 2-14
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:09.627-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:09.627-04:00

Bravo VAV 2-14 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 2-14 Heating Valve Output
equip ref: Bravo VAV 2-14
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:11.258-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:11.258-04:00

Bravo VAV 2-14 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 2-14 Supply Air Temperature
equip ref: Bravo VAV 2-14
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:09.879-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:09.879-04:00

Bravo VAV 2-14 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 2-14 Zone Air Temp Setpoint
equip ref: Bravo VAV 2-14
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:10.995-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:10.995-04:00

Bravo VAV 2-14 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 2-14 Zone Temperature
equip ref: Bravo VAV 2-14
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:09.879-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:09.879-04:00

Bravo VAV 2-15
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-2
dis: Bravo VAV 2-15
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:149°F, designHotWaterPower:9.7MMBTU/h, designHotWaterFlow:1gal/min, designAirFlow:400cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 149
  design hot water power: 9.7
  design hot water flow: 1
  design air flow: 400

Bravo VAV 2-15 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 2-15 Damper Output
equip ref: Bravo VAV 2-15
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:09.752-04:00

Bravo VAV 2-15 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 2-15 Discharge Air Flow
equip ref: Bravo VAV 2-15
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:10.87-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:10.87-04:00

Bravo VAV 2-15 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 2-15 Discharge Air Flow Setpoint
equip ref: Bravo VAV 2-15
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:10.374-04:00

Bravo VAV 2-15 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 2-15 Heating Valve Output
equip ref: Bravo VAV 2-15
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:10.497-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:10.497-04:00

Bravo VAV 2-15 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 2-15 Supply Air Temperature
equip ref: Bravo VAV 2-15
kind: Str
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:10.995-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:10.995-04:00

Bravo VAV 2-15 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 2-15 Zone Air Temp Setpoint
equip ref: Bravo VAV 2-15
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:10.249-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:10.249-04:00

Bravo VAV 2-15 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 2-15 Zone Temperature
equip ref: Bravo VAV 2-15
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:07.721-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:07.721-04:00

Bravo VAV 2-16
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-2
dis: Bravo VAV 2-16
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:149°F, designHotWaterPower:9.2MMBTU/h, designHotWaterFlow:1gal/min, designAirFlow:400cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 149
  design hot water power: 9.2
  design hot water flow: 1
  design air flow: 400

Bravo VAV 2-16 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 2-16 Damper Output
equip ref: Bravo VAV 2-16
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:09.627-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:09.627-04:00

Bravo VAV 2-16 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 2-16 Discharge Air Flow
equip ref: Bravo VAV 2-16
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:10.249-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:10.249-04:00

Bravo VAV 2-16 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 2-16 Discharge Air Flow Setpoint
equip ref: Bravo VAV 2-16
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:10.745-04:00

Bravo VAV 2-16 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 2-16 Heating Valve Output
equip ref: Bravo VAV 2-16
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:09.752-04:00

Bravo VAV 2-16 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 2-16 Supply Air Temperature
equip ref: Bravo VAV 2-16
kind: Str
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:10.497-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:10.497-04:00

Bravo VAV 2-16 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 2-16 Zone Air Temp Setpoint
equip ref: Bravo VAV 2-16
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:09.879-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:09.879-04:00

Bravo VAV 2-16 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 2-16 Zone Temperature
equip ref: Bravo VAV 2-16
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:10.126-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:10.126-04:00

Bravo VAV 2-17
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-2
dis: Bravo VAV 2-17
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:149°F, designHotWaterPower:8.9MMBTU/h, designHotWaterFlow:1gal/min, designAirFlow:400cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 149
  design hot water power: 8.9
  design hot water flow: 1
  design air flow: 400

Bravo VAV 2-17 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 2-17 Damper Output
equip ref: Bravo VAV 2-17
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:10.249-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:10.249-04:00

Bravo VAV 2-17 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 2-17 Discharge Air Flow
equip ref: Bravo VAV 2-17
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:11.125-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:11.125-04:00

Bravo VAV 2-17 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 2-17 Discharge Air Flow Setpoint
equip ref: Bravo VAV 2-17
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:09.879-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:09.879-04:00

Bravo VAV 2-17 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 2-17 Heating Valve Output
equip ref: Bravo VAV 2-17
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:07.721-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:07.721-04:00

Bravo VAV 2-17 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 2-17 Supply Air Temperature
equip ref: Bravo VAV 2-17
kind: Str
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:10.126-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:10.126-04:00

Bravo VAV 2-17 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 2-17 Zone Air Temp Setpoint
equip ref: Bravo VAV 2-17
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:09.627-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:09.627-04:00

Bravo VAV 2-17 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 2-17 Zone Temperature
equip ref: Bravo VAV 2-17
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:10.374-04:00

Bravo VAV 2-18
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-2
dis: Bravo VAV 2-18
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:152°F, designHotWaterPower:15MMBTU/h, designHotWaterFlow:1.75gal/min, designAirFlow:550cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 152
  design hot water power: 15
  design hot water flow: 1.75
  design air flow: 550

Bravo VAV 2-18 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 2-18 Damper Output
equip ref: Bravo VAV 2-18
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:10.745-04:00

Bravo VAV 2-18 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 2-18 Discharge Air Flow
equip ref: Bravo VAV 2-18
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:10.745-04:00

Bravo VAV 2-18 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 2-18 Discharge Air Flow Setpoint
equip ref: Bravo VAV 2-18
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:10.87-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:10.87-04:00

Bravo VAV 2-18 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 2-18 Heating Valve Output
equip ref: Bravo VAV 2-18
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:10.374-04:00

Bravo VAV 2-18 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 2-18 Supply Air Temperature
equip ref: Bravo VAV 2-18
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:10.003-04:00

Bravo VAV 2-18 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 2-18 Zone Air Temp Setpoint
equip ref: Bravo VAV 2-18
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:09.752-04:00

Bravo VAV 2-18 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 2-18 Zone Temperature
equip ref: Bravo VAV 2-18
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:10.003-04:00

Bravo VAV 2-19
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-2
dis: Bravo VAV 2-19
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:153°F, designHotWaterPower:6.2MMBTU/h, designHotWaterFlow:0.75gal/min, designAirFlow:350cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 153
  design hot water power: 6.2
  design hot water flow: 0.75
  design air flow: 350

Bravo VAV 2-19 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 2-19 Damper Output
equip ref: Bravo VAV 2-19
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:07.721-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:07.721-04:00

Bravo VAV 2-19 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 2-19 Discharge Air Flow
equip ref: Bravo VAV 2-19
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:11.258-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:11.258-04:00

Bravo VAV 2-19 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 2-19 Discharge Air Flow Setpoint
equip ref: Bravo VAV 2-19
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:07.598-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:07.598-04:00

Bravo VAV 2-19 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 2-19 Heating Valve Output
equip ref: Bravo VAV 2-19
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:09.627-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:09.627-04:00

Bravo VAV 2-19 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 2-19 Supply Air Temperature
equip ref: Bravo VAV 2-19
kind: Str
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:10.62-04:00

Bravo VAV 2-19 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 2-19 Zone Air Temp Setpoint
equip ref: Bravo VAV 2-19
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:10.745-04:00

Bravo VAV 2-19 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 2-19 Zone Temperature
equip ref: Bravo VAV 2-19
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:10.249-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:10.249-04:00

Bravo VAV 2-2
type: thermostat
type: vav
has tag: equip
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-2
dis: Bravo VAV 2-2
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:153°F, designHotWaterPower:9.6MMBTU/h, designHotWaterFlow:1.25gal/min, designAirFlow:650cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 153
  design hot water power: 9.6
  design hot water flow: 1.25
  design air flow: 650

Bravo VAV 2-2 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 2-2 Damper Output
equip ref: Bravo VAV 2-2
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:10.497-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:10.497-04:00

Bravo VAV 2-2 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 2-2 Discharge Air Flow
equip ref: Bravo VAV 2-2
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:09.752-04:00

Bravo VAV 2-2 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 2-2 Discharge Air Flow Setpoint
equip ref: Bravo VAV 2-2
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:07.598-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:07.598-04:00

Bravo VAV 2-2 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 2-2 Heating Valve Output
equip ref: Bravo VAV 2-2
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:10.62-04:00

Bravo VAV 2-2 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 2-2 Supply Air Temperature
equip ref: Bravo VAV 2-2
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:07.721-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:07.721-04:00

Bravo VAV 2-2 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 2-2 Zone Air Temp Setpoint
equip ref: Bravo VAV 2-2
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:10.374-04:00

Bravo VAV 2-2 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 2-2 Zone Temperature
equip ref: Bravo VAV 2-2
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:09.627-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:09.627-04:00

Bravo VAV 2-20
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-2
dis: Bravo VAV 2-20
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:152°F, designHotWaterPower:10.8MMBTU/h, designHotWaterFlow:1.25gal/min, designAirFlow:650cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 152
  design hot water power: 10.8
  design hot water flow: 1.25
  design air flow: 650

Bravo VAV 2-20 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 2-20 Damper Output
equip ref: Bravo VAV 2-20
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:09.879-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:09.879-04:00

Bravo VAV 2-20 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 2-20 Discharge Air Flow
equip ref: Bravo VAV 2-20
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:10.87-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:10.87-04:00

Bravo VAV 2-20 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 2-20 Discharge Air Flow Setpoint
equip ref: Bravo VAV 2-20
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:10.003-04:00

Bravo VAV 2-20 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 2-20 Heating Valve Output
equip ref: Bravo VAV 2-20
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:10.249-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:10.249-04:00

Bravo VAV 2-20 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 2-20 Supply Air Temperature
equip ref: Bravo VAV 2-20
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:10.003-04:00

Bravo VAV 2-20 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 2-20 Zone Air Temp Setpoint
equip ref: Bravo VAV 2-20
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:13.145-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:13.145-04:00

Bravo VAV 2-20 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 2-20 Zone Temperature
equip ref: Bravo VAV 2-20
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:10.126-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:10.126-04:00

Bravo VAV 2-21
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-2
dis: Bravo VAV 2-21
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:153°F, designHotWaterPower:10.4MMBTU/h, designHotWaterFlow:1.25gal/min, designAirFlow:650cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 153
  design hot water power: 10.4
  design hot water flow: 1.25
  design air flow: 650

Bravo VAV 2-21 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 2-21 Damper Output
equip ref: Bravo VAV 2-21
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:10.249-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:10.249-04:00

Bravo VAV 2-21 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 2-21 Discharge Air Flow
equip ref: Bravo VAV 2-21
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:10.62-04:00

Bravo VAV 2-21 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 2-21 Discharge Air Flow Setpoint
equip ref: Bravo VAV 2-21
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:13.145-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:13.145-04:00

Bravo VAV 2-21 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 2-21 Heating Valve Output
equip ref: Bravo VAV 2-21
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:09.752-04:00

Bravo VAV 2-21 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 2-21 Supply Air Temperature
equip ref: Bravo VAV 2-21
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:10.003-04:00

Bravo VAV 2-21 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 2-21 Zone Air Temp Setpoint
equip ref: Bravo VAV 2-21
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:10.126-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:10.126-04:00

Bravo VAV 2-21 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 2-21 Zone Temperature
equip ref: Bravo VAV 2-21
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:10.745-04:00

Bravo VAV 2-22
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-2
dis: Bravo VAV 2-22
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:149°F, designHotWaterPower:9.2MMBTU/h, designHotWaterFlow:1gal/min, designAirFlow:450cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 149
  design hot water power: 9.2
  design hot water flow: 1
  design air flow: 450

Bravo VAV 2-22 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 2-22 Damper Output
equip ref: Bravo VAV 2-22
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:10.497-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:10.497-04:00

Bravo VAV 2-22 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 2-22 Discharge Air Flow
equip ref: Bravo VAV 2-22
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:10.745-04:00

Bravo VAV 2-22 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 2-22 Discharge Air Flow Setpoint
equip ref: Bravo VAV 2-22
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:10.995-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:10.995-04:00

Bravo VAV 2-22 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 2-22 Heating Valve Output
equip ref: Bravo VAV 2-22
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:10.497-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:10.497-04:00

Bravo VAV 2-22 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 2-22 Supply Air Temperature
equip ref: Bravo VAV 2-22
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:10.249-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:10.249-04:00

Bravo VAV 2-22 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 2-22 Zone Air Temp Setpoint
equip ref: Bravo VAV 2-22
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:07.598-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:07.598-04:00

Bravo VAV 2-22 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 2-22 Zone Temperature
equip ref: Bravo VAV 2-22
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:13.145-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:13.145-04:00

Bravo VAV 2-23
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-2
dis: Bravo VAV 2-23
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:148°F, designHotWaterPower:6.2MMBTU/h, designHotWaterFlow:0.75gal/min, designAirFlow:350cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 148
  design hot water power: 6.2
  design hot water flow: 0.75
  design air flow: 350

Bravo VAV 2-23 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 2-23 Damper Output
equip ref: Bravo VAV 2-23
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:09.627-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:09.627-04:00

Bravo VAV 2-23 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 2-23 Discharge Air Flow
equip ref: Bravo VAV 2-23
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:10.249-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:10.249-04:00

Bravo VAV 2-23 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 2-23 Discharge Air Flow Setpoint
equip ref: Bravo VAV 2-23
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:09.752-04:00

Bravo VAV 2-23 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 2-23 Heating Valve Output
equip ref: Bravo VAV 2-23
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:10.497-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:10.497-04:00

Bravo VAV 2-23 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 2-23 Supply Air Temperature
equip ref: Bravo VAV 2-23
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:10.62-04:00

Bravo VAV 2-23 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 2-23 Zone Air Temp Setpoint
equip ref: Bravo VAV 2-23
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:10.62-04:00

Bravo VAV 2-23 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 2-23 Zone Temperature
equip ref: Bravo VAV 2-23
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:09.752-04:00

Bravo VAV 2-24
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-2
dis: Bravo VAV 2-24
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:150°F, designHotWaterPower:15.4MMBTU/h, designHotWaterFlow:2.5gal/min, designAirFlow:1600cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 150
  design hot water power: 15.4
  design hot water flow: 2.5
  design air flow: 1600

Bravo VAV 2-24 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 2-24 Damper Output
equip ref: Bravo VAV 2-24
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:11.258-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:11.258-04:00

Bravo VAV 2-24 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 2-24 Discharge Air Flow
equip ref: Bravo VAV 2-24
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:10.003-04:00

Bravo VAV 2-24 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 2-24 Discharge Air Flow Setpoint
equip ref: Bravo VAV 2-24
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:13.145-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:13.145-04:00

Bravo VAV 2-24 Heating Valve
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 2-24 Heating Valve
equip ref: Bravo VAV 2-24
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:10.249-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:10.249-04:00

Bravo VAV 2-24 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 2-24 Supply Air Temperature
equip ref: Bravo VAV 2-24
kind: Str
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:10.003-04:00

Bravo VAV 2-24 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 2-24 Zone Air Temp Setpoint
equip ref: Bravo VAV 2-24
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:09.752-04:00

Bravo VAV 2-24 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 2-24 Zone Temperature
equip ref: Bravo VAV 2-24
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:09.879-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:09.879-04:00

Bravo VAV 2-25
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-2
dis: Bravo VAV 2-25
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:153°F, designHotWaterPower:4.4MMBTU/h, designHotWaterFlow:0.75gal/min, designAirFlow:250cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 153
  design hot water power: 4.4
  design hot water flow: 0.75
  design air flow: 250

Bravo VAV 2-25 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 2-25 Damper Output
equip ref: Bravo VAV 2-25
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:07.721-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:07.721-04:00

Bravo VAV 2-25 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 2-25 Discharge Air Flow
equip ref: Bravo VAV 2-25
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:11.125-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:11.125-04:00

Bravo VAV 2-25 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 2-25 Discharge Air Flow Setpoint
equip ref: Bravo VAV 2-25
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:10.126-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:10.126-04:00

Bravo VAV 2-25 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 2-25 Heating Valve Output
equip ref: Bravo VAV 2-25
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:10.249-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:10.249-04:00

Bravo VAV 2-25 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 2-25 Supply Air Temperature
equip ref: Bravo VAV 2-25
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:09.752-04:00

Bravo VAV 2-25 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 2-25 Zone Air Temp Setpoint
equip ref: Bravo VAV 2-25
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:10.745-04:00

Bravo VAV 2-25 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 2-25 Zone Temperature
equip ref: Bravo VAV 2-25
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:10.995-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:10.995-04:00

Bravo VAV 2-26
type: thermostat
type: vav
has tag: equip
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-2
dis: Bravo VAV 2-26
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:148°F, designHotWaterPower:4.2MMBTU/h, designHotWaterFlow:0.5gal/min, designAirFlow:300cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 148
  design hot water power: 4.2
  design hot water flow: 0.5
  design air flow: 300

Bravo VAV 2-26 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 2-26 Damper Output
equip ref: Bravo VAV 2-26
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:09.627-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:09.627-04:00

Bravo VAV 2-26 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 2-26 Discharge Air Flow
equip ref: Bravo VAV 2-26
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:10.126-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:10.126-04:00

Bravo VAV 2-26 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 2-26 Discharge Air Flow Setpoint
equip ref: Bravo VAV 2-26
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:09.752-04:00

Bravo VAV 2-26 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 2-26 Heating Valve Output
equip ref: Bravo VAV 2-26
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:13.145-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:13.145-04:00

Bravo VAV 2-26 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 2-26 Supply Air Temperature
equip ref: Bravo VAV 2-26
kind: Str
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:09.879-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:09.879-04:00

Bravo VAV 2-26 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 2-26 Zone Air Temp Setpoint
equip ref: Bravo VAV 2-26
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:10.87-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:10.87-04:00

Bravo VAV 2-26 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 2-26 Zone Temperature
equip ref: Bravo VAV 2-26
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:07.598-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:07.598-04:00

Bravo VAV 2-27
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-2
dis: Bravo VAV 2-27
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:148°F, designHotWaterPower:18.6MMBTU/h, designHotWaterFlow:2gal/min, designAirFlow:1125cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 148
  design hot water power: 18.6
  design hot water flow: 2
  design air flow: 1125

Bravo VAV 2-27 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 2-27 Damper Output
equip ref: Bravo VAV 2-27
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:10.87-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:10.87-04:00

Bravo VAV 2-27 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 2-27 Discharge Air Flow
equip ref: Bravo VAV 2-27
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:10.62-04:00

Bravo VAV 2-27 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 2-27 Discharge Air Flow Setpoint
equip ref: Bravo VAV 2-27
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:10.62-04:00

Bravo VAV 2-27 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 2-27 Heating Valve Output
equip ref: Bravo VAV 2-27
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:10.126-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:10.126-04:00

Bravo VAV 2-27 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 2-27 Supply Air Temperature
equip ref: Bravo VAV 2-27
kind: Str
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:09.627-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:09.627-04:00

Bravo VAV 2-27 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 2-27 Zone Air Temp Setpoint
equip ref: Bravo VAV 2-27
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:07.721-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:07.721-04:00

Bravo VAV 2-27 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 2-27 Zone Temperature
equip ref: Bravo VAV 2-27
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:09.752-04:00

Bravo VAV 2-28
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-2
dis: Bravo VAV 2-28
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:149°F, designHotWaterPower:9.5MMBTU/h, designHotWaterFlow:1gal/min, designAirFlow:500cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 149
  design hot water power: 9.5
  design hot water flow: 1
  design air flow: 500

Bravo VAV 2-28 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 2-28 Damper Output
equip ref: Bravo VAV 2-28
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:07.721-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:07.721-04:00

Bravo VAV 2-28 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 2-28 Discharge Air Flow
equip ref: Bravo VAV 2-28
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:10.995-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:10.995-04:00

Bravo VAV 2-28 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 2-28 Discharge Air Flow Setpoint
equip ref: Bravo VAV 2-28
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:10.497-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:10.497-04:00

Bravo VAV 2-28 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 2-28 Heating Valve Output
equip ref: Bravo VAV 2-28
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:10.249-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:10.249-04:00

Bravo VAV 2-28 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 2-28 Supply Air Temperature
equip ref: Bravo VAV 2-28
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:09.627-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:09.627-04:00

Bravo VAV 2-28 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 2-28 Zone Air Temp Setpoint
equip ref: Bravo VAV 2-28
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:13.145-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:13.145-04:00

Bravo VAV 2-28 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 2-28 Zone Temperature
equip ref: Bravo VAV 2-28
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:10.374-04:00

Bravo VAV 2-29
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-2
dis: Bravo VAV 2-29
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:149°F, designHotWaterPower:9.8MMBTU/h, designHotWaterFlow:1gal/min, designAirFlow:500cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 149
  design hot water power: 9.8
  design hot water flow: 1
  design air flow: 500

Bravo VAV 2-29 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 2-29 Damper Output
equip ref: Bravo VAV 2-29
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:09.627-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:09.627-04:00

Bravo VAV 2-29 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 2-29 Discharge Air Flow
equip ref: Bravo VAV 2-29
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:10.249-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:10.249-04:00

Bravo VAV 2-29 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 2-29 Discharge Air Flow Setpoint
equip ref: Bravo VAV 2-29
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:10.745-04:00

Bravo VAV 2-29 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 2-29 Heating Valve Output
equip ref: Bravo VAV 2-29
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:11.125-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:11.125-04:00

Bravo VAV 2-29 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 2-29 Supply Air Temperature
equip ref: Bravo VAV 2-29
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:13.145-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:13.145-04:00

Bravo VAV 2-29 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 2-29 Zone Air Temp Setpoint
equip ref: Bravo VAV 2-29
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:10.62-04:00

Bravo VAV 2-29 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 2-29 Zone Temperature
equip ref: Bravo VAV 2-29
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:10.126-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:10.126-04:00

Bravo VAV 2-3
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-2
dis: Bravo VAV 2-3
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:149°F, designHotWaterPower:9.2MMBTU/h, designHotWaterFlow:1gal/min, designAirFlow:450cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 149
  design hot water power: 9.2
  design hot water flow: 1
  design air flow: 450

Bravo VAV 2-3 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 2-3 Damper Output
equip ref: Bravo VAV 2-3
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:09.627-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:09.627-04:00

Bravo VAV 2-3 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 2-3 Discharge Air Flow
equip ref: Bravo VAV 2-3
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:10.87-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:10.87-04:00

Bravo VAV 2-3 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 2-3 Discharge Air Flow Setpoint
equip ref: Bravo VAV 2-3
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:11.258-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:11.258-04:00

Bravo VAV 2-3 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 2-3 Heating Valve Output
equip ref: Bravo VAV 2-3
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:10.249-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:10.249-04:00

Bravo VAV 2-3 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 2-3 Supply Air Temperature
equip ref: Bravo VAV 2-3
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:10.745-04:00

Bravo VAV 2-3 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 2-3 Zone Air Temp Setpoint
equip ref: Bravo VAV 2-3
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:10.87-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:10.87-04:00

Bravo VAV 2-3 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 2-3 Zone Temperature
equip ref: Bravo VAV 2-3
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:11.125-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:11.125-04:00

Bravo VAV 2-30
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-2
dis: Bravo VAV 2-30
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:149°F, designHotWaterPower:9.5MMBTU/h, designHotWaterFlow:1gal/min, designAirFlow:500cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 149
  design hot water power: 9.5
  design hot water flow: 1
  design air flow: 500

Bravo VAV 2-30 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 2-30 Damper Output
equip ref: Bravo VAV 2-30
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:10.87-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:10.87-04:00

Bravo VAV 2-30 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 2-30 Discharge Air Flow
equip ref: Bravo VAV 2-30
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:09.879-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:09.879-04:00

Bravo VAV 2-30 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 2-30 Discharge Air Flow Setpoint
equip ref: Bravo VAV 2-30
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:09.627-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:09.627-04:00

Bravo VAV 2-30 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 2-30 Heating Valve Output
equip ref: Bravo VAV 2-30
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:10.374-04:00

Bravo VAV 2-30 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 2-30 Supply Air Temperature
equip ref: Bravo VAV 2-30
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:10.745-04:00

Bravo VAV 2-30 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 2-30 Zone Air Temp Setpoint
equip ref: Bravo VAV 2-30
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:09.879-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:09.879-04:00

Bravo VAV 2-30 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 2-30 Zone Temperature
equip ref: Bravo VAV 2-30
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:09.752-04:00

Bravo VAV 2-31
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-2
dis: Bravo VAV 2-31
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:153°F, designHotWaterPower:18.6MMBTU/h, designHotWaterFlow:2gal/min, designAirFlow:650cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 153
  design hot water power: 18.6
  design hot water flow: 2
  design air flow: 650

Bravo VAV 2-31 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 2-31 Damper Output
equip ref: Bravo VAV 2-31
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:10.374-04:00

Bravo VAV 2-31 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 2-31 Discharge Air Flow
equip ref: Bravo VAV 2-31
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:13.145-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:13.145-04:00

Bravo VAV 2-31 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 2-31 Discharge Air Flow Setpoint
equip ref: Bravo VAV 2-31
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:10.87-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:10.87-04:00

Bravo VAV 2-31 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 2-31 Heating Valve Output
equip ref: Bravo VAV 2-31
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:10.62-04:00

Bravo VAV 2-31 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 2-31 Supply Air Temperature
equip ref: Bravo VAV 2-31
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:11.125-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:11.125-04:00

Bravo VAV 2-31 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 2-31 Zone Air Temp Setpoint
equip ref: Bravo VAV 2-31
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:11.258-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:11.258-04:00

Bravo VAV 2-31 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 2-31 Zone Temperature
equip ref: Bravo VAV 2-31
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:09.879-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:09.879-04:00

Bravo VAV 2-32
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-2
dis: Bravo VAV 2-32
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:149°F, designHotWaterPower:28.6MMBTU/h, designHotWaterFlow:3.5gal/min, designAirFlow:2150cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 149
  design hot water power: 28.6
  design hot water flow: 3.5
  design air flow: 2150

Bravo VAV 2-32 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 2-32 Damper Output
equip ref: Bravo VAV 2-32
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:10.003-04:00

Bravo VAV 2-32 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 2-32 Discharge Air Flow
equip ref: Bravo VAV 2-32
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:10.374-04:00

Bravo VAV 2-32 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 2-32 Discharge Air Flow Setpoint
equip ref: Bravo VAV 2-32
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:10.745-04:00

Bravo VAV 2-32 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 2-32 Heating Valve Output
equip ref: Bravo VAV 2-32
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:10.126-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:10.126-04:00

Bravo VAV 2-32 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 2-32 Supply Air Temperature
equip ref: Bravo VAV 2-32
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:09.627-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:09.627-04:00

Bravo VAV 2-32 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 2-32 Zone Air Temp Setpoint
equip ref: Bravo VAV 2-32
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:10.62-04:00

Bravo VAV 2-32 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 2-32 Zone Temperature
equip ref: Bravo VAV 2-32
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:10.497-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:10.497-04:00

Bravo VAV 2-33
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-2
dis: Bravo VAV 2-33
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:148°F, designHotWaterPower:3.1MMBTU/h, designHotWaterFlow:0.5gal/min, designAirFlow:200cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 148
  design hot water power: 3.1
  design hot water flow: 0.5
  design air flow: 200

Bravo VAV 2-33 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 2-33 Damper Output
equip ref: Bravo VAV 2-33
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:10.374-04:00

Bravo VAV 2-33 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 2-33 Discharge Air Flow
equip ref: Bravo VAV 2-33
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:10.249-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:10.249-04:00

Bravo VAV 2-33 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 2-33 Discharge Air Flow Setpoint
equip ref: Bravo VAV 2-33
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:09.627-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:09.627-04:00

Bravo VAV 2-33 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 2-33 Heating Valve Output
equip ref: Bravo VAV 2-33
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:10.62-04:00

Bravo VAV 2-33 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 2-33 Supply Air Temperature
equip ref: Bravo VAV 2-33
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:09.752-04:00

Bravo VAV 2-33 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 2-33 Zone Air Temp Setpoint
equip ref: Bravo VAV 2-33
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:09.627-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:09.627-04:00

Bravo VAV 2-33 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 2-33 Zone Temperature
equip ref: Bravo VAV 2-33
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:10.87-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:10.87-04:00

Bravo VAV 2-34
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-2
dis: Bravo VAV 2-34
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:149°F, designHotWaterPower:10.3MMBTU/h, designHotWaterFlow:1gal/min, designAirFlow:575cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 149
  design hot water power: 10.3
  design hot water flow: 1
  design air flow: 575

Bravo VAV 2-34 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 2-34 Damper Output
equip ref: Bravo VAV 2-34
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:10.249-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:10.249-04:00

Bravo VAV 2-34 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 2-34 Discharge Air Flow
equip ref: Bravo VAV 2-34
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:07.598-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:07.598-04:00

Bravo VAV 2-34 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 2-34 Discharge Air Flow Setpoint
equip ref: Bravo VAV 2-34
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:07.598-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:07.598-04:00

Bravo VAV 2-34 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 2-34 Heating Valve Output
equip ref: Bravo VAV 2-34
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:13.145-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:13.145-04:00

Bravo VAV 2-34 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 2-34 Supply Air Temperature
equip ref: Bravo VAV 2-34
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:10.62-04:00

Bravo VAV 2-34 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 2-34 Zone Air Temp Setpoint
equip ref: Bravo VAV 2-34
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:10.995-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:10.995-04:00

Bravo VAV 2-34 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 2-34 Zone Temperature
equip ref: Bravo VAV 2-34
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:10.249-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:10.249-04:00

Bravo VAV 2-35
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-2
dis: Bravo VAV 2-35
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:148°F, designHotWaterPower:3.1MMBTU/h, designHotWaterFlow:0.5gal/min, designAirFlow:250cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 148
  design hot water power: 3.1
  design hot water flow: 0.5
  design air flow: 250

Bravo VAV 2-35 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 2-35 Damper Output
equip ref: Bravo VAV 2-35
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:09.879-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:09.879-04:00

Bravo VAV 2-35 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 2-35 Discharge Air Flow
equip ref: Bravo VAV 2-35
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:07.473-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:07.473-04:00

Bravo VAV 2-35 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 2-35 Discharge Air Flow Setpoint
equip ref: Bravo VAV 2-35
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:10.497-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:10.497-04:00

Bravo VAV 2-35 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 2-35 Heating Valve Output
equip ref: Bravo VAV 2-35
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:10.374-04:00

Bravo VAV 2-35 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 2-35 Supply Air Temperature
equip ref: Bravo VAV 2-35
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:10.249-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:10.249-04:00

Bravo VAV 2-35 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 2-35 Zone Air Temp Setpoint
equip ref: Bravo VAV 2-35
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:10.87-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:10.87-04:00

Bravo VAV 2-35 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 2-35 Zone Temperature
equip ref: Bravo VAV 2-35
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:10.62-04:00

Bravo VAV 2-36
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-2
dis: Bravo VAV 2-36
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:149°F, designHotWaterPower:9.2MMBTU/h, designHotWaterFlow:1gal/min, designAirFlow:450cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 149
  design hot water power: 9.2
  design hot water flow: 1
  design air flow: 450

Bravo VAV 2-36 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 2-36 Damper Output
equip ref: Bravo VAV 2-36
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:10.497-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:10.497-04:00

Bravo VAV 2-36 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 2-36 Discharge Air Flow
equip ref: Bravo VAV 2-36
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:07.721-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:07.721-04:00

Bravo VAV 2-36 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 2-36 Discharge Air Flow Setpoint
equip ref: Bravo VAV 2-36
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:09.627-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:09.627-04:00

Bravo VAV 2-36 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 2-36 Heating Valve Output
equip ref: Bravo VAV 2-36
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:07.598-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:07.598-04:00

Bravo VAV 2-36 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 2-36 Supply Air Temperature
equip ref: Bravo VAV 2-36
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:09.879-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:09.879-04:00

Bravo VAV 2-36 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 2-36 Zone Air Temp Setpoint
equip ref: Bravo VAV 2-36
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:09.627-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:09.627-04:00

Bravo VAV 2-36 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 2-36 Zone Temperature
equip ref: Bravo VAV 2-36
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:09.627-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:09.627-04:00

Bravo VAV 2-37
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-2
dis: Bravo VAV 2-37
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:150°F, designHotWaterPower:10.5MMBTU/h, designHotWaterFlow:1.25gal/min, designAirFlow:500cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 150
  design hot water power: 10.5
  design hot water flow: 1.25
  design air flow: 500

Bravo VAV 2-37 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 2-37 Damper Output
equip ref: Bravo VAV 2-37
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:09.879-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:09.879-04:00

Bravo VAV 2-37 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 2-37 Discharge Air Flow
equip ref: Bravo VAV 2-37
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:09.752-04:00

Bravo VAV 2-37 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 2-37 Discharge Air Flow Setpoint
equip ref: Bravo VAV 2-37
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:10.249-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:10.249-04:00

Bravo VAV 2-37 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 2-37 Heating Valve Output
equip ref: Bravo VAV 2-37
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:09.752-04:00

Bravo VAV 2-37 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 2-37 Supply Air Temperature
equip ref: Bravo VAV 2-37
kind: Str
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:10.62-04:00

Bravo VAV 2-37 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 2-37 Zone Air Temp Setpoint
equip ref: Bravo VAV 2-37
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:09.627-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:09.627-04:00

Bravo VAV 2-37 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 2-37 Zone Temperature
equip ref: Bravo VAV 2-37
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:10.249-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:10.249-04:00

Bravo VAV 2-38
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-2
dis: Bravo VAV 2-38
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:148°F, designHotWaterPower:4.9MMBTU/h, designHotWaterFlow:0.5gal/min, designAirFlow:250cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 148
  design hot water power: 4.9
  design hot water flow: 0.5
  design air flow: 250

Bravo VAV 2-38 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 2-38 Damper Output
equip ref: Bravo VAV 2-38
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:13.145-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:13.145-04:00

Bravo VAV 2-38 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 2-38 Discharge Air Flow
equip ref: Bravo VAV 2-38
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:11.258-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:11.258-04:00

Bravo VAV 2-38 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 2-38 Discharge Air Flow Setpoint
equip ref: Bravo VAV 2-38
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:10.497-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:10.497-04:00

Bravo VAV 2-38 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 2-38 Heating Valve Output
equip ref: Bravo VAV 2-38
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:10.745-04:00

Bravo VAV 2-38 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 2-38 Supply Air Temperature
equip ref: Bravo VAV 2-38
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:10.62-04:00

Bravo VAV 2-38 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 2-38 Zone Air Temp Setpoint
equip ref: Bravo VAV 2-38
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:09.627-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:09.627-04:00

Bravo VAV 2-38 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 2-38 Zone Temperature
equip ref: Bravo VAV 2-38
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:10.87-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:10.87-04:00

Bravo VAV 2-39
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-2
dis: Bravo VAV 2-39
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:153°F, designHotWaterPower:9.5MMBTU/h, designHotWaterFlow:9.5gal/min, designAirFlow:475cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 153
  design hot water power: 9.5
  design hot water flow: 9.5
  design air flow: 475

Bravo VAV 2-39 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 2-39 Damper Output
equip ref: Bravo VAV 2-39
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:10.745-04:00

Bravo VAV 2-39 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 2-39 Discharge Air Flow
equip ref: Bravo VAV 2-39
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:11.125-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:11.125-04:00

Bravo VAV 2-39 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 2-39 Discharge Air Flow Setpoint
equip ref: Bravo VAV 2-39
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:10.126-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:10.126-04:00

Bravo VAV 2-39 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 2-39 Heating Valve Output
equip ref: Bravo VAV 2-39
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:10.374-04:00

Bravo VAV 2-39 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 2-39 Supply Air Temperature
equip ref: Bravo VAV 2-39
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:10.003-04:00

Bravo VAV 2-39 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 2-39 Zone Air Temp Setpoint
equip ref: Bravo VAV 2-39
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:10.745-04:00

Bravo VAV 2-39 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 2-39 Zone Temperature
equip ref: Bravo VAV 2-39
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:09.879-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:09.879-04:00

Bravo VAV 2-4
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-2
dis: Bravo VAV 2-4
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:151°F, designHotWaterPower:2.9MMBTU/h, designHotWaterFlow:0.5gal/min, designAirFlow:150cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 151
  design hot water power: 2.9
  design hot water flow: 0.5
  design air flow: 150

Bravo VAV 2-4 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 2-4 Damper Output
equip ref: Bravo VAV 2-4
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:10.497-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:10.497-04:00

Bravo VAV 2-4 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 2-4 Discharge Air Flow
equip ref: Bravo VAV 2-4
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:09.752-04:00

Bravo VAV 2-4 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 2-4 Discharge Air Flow Setpoint
equip ref: Bravo VAV 2-4
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:10.995-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:10.995-04:00

Bravo VAV 2-4 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 2-4 Heating Valve Output
equip ref: Bravo VAV 2-4
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:09.879-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:09.879-04:00

Bravo VAV 2-4 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 2-4 Supply Air Temperature
equip ref: Bravo VAV 2-4
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:10.62-04:00

Bravo VAV 2-4 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 2-4 Zone Air Temp Setpoint
equip ref: Bravo VAV 2-4
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:10.62-04:00

Bravo VAV 2-4 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 2-4 Zone Temperature
equip ref: Bravo VAV 2-4
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:10.003-04:00

Bravo VAV 2-40
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-2
dis: Bravo VAV 2-40
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:153°F, designHotWaterPower:9.8MMBTU/h, designHotWaterFlow:1.25gal/min, designAirFlow:475cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 153
  design hot water power: 9.8
  design hot water flow: 1.25
  design air flow: 475

Bravo VAV 2-40 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 2-40 Damper Output
equip ref: Bravo VAV 2-40
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:10.003-04:00

Bravo VAV 2-40 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 2-40 Discharge Air Flow
equip ref: Bravo VAV 2-40
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:13.145-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:13.145-04:00

Bravo VAV 2-40 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 2-40 Discharge Air Flow Setpoint
equip ref: Bravo VAV 2-40
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:10.745-04:00

Bravo VAV 2-40 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 2-40 Heating Valve Output
equip ref: Bravo VAV 2-40
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:10.995-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:10.995-04:00

Bravo VAV 2-40 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 2-40 Supply Air Temperature
equip ref: Bravo VAV 2-40
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:13.145-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:13.145-04:00

Bravo VAV 2-40 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 2-40 Zone Air Temp Setpoint
equip ref: Bravo VAV 2-40
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:10.003-04:00

Bravo VAV 2-40 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 2-40 Zone Temperature
equip ref: Bravo VAV 2-40
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:09.752-04:00

Bravo VAV 2-41
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-2
dis: Bravo VAV 2-41
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:153°F, designHotWaterPower:9.5MMBTU/h, designHotWaterFlow:1.25gal/min, designAirFlow:475cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 153
  design hot water power: 9.5
  design hot water flow: 1.25
  design air flow: 475

Bravo VAV 2-41 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 2-41 Damper Output
equip ref: Bravo VAV 2-41
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:09.626-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:09.626-04:00

Bravo VAV 2-41 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 2-41 Discharge Air Flow
equip ref: Bravo VAV 2-41
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:09.627-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:09.627-04:00

Bravo VAV 2-41 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 2-41 Discharge Air Flow Setpoint
equip ref: Bravo VAV 2-41
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:09.879-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:09.879-04:00

Bravo VAV 2-41 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 2-41 Heating Valve Output
equip ref: Bravo VAV 2-41
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:10.374-04:00

Bravo VAV 2-41 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 2-41 Supply Air Temperature
equip ref: Bravo VAV 2-41
kind: Str
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:10.87-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:10.87-04:00

Bravo VAV 2-41 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 2-41 Zone Air Temp Setpoint
equip ref: Bravo VAV 2-41
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:10.497-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:10.497-04:00

Bravo VAV 2-41 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 2-41 Zone Temperature
equip ref: Bravo VAV 2-41
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:09.879-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:09.879-04:00

Bravo VAV 2-42
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-2
dis: Bravo VAV 2-42
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:149°F, designHotWaterPower:8.9MMBTU/h, designHotWaterFlow:1gal/min, designAirFlow:450cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 149
  design hot water power: 8.9
  design hot water flow: 1
  design air flow: 450

Bravo VAV 2-42 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 2-42 Damper Output
equip ref: Bravo VAV 2-42
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:10.126-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:10.126-04:00

Bravo VAV 2-42 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 2-42 Discharge Air Flow
equip ref: Bravo VAV 2-42
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:10.87-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:10.87-04:00

Bravo VAV 2-42 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 2-42 Discharge Air Flow Setpoint
equip ref: Bravo VAV 2-42
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:10.62-04:00

Bravo VAV 2-42 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 2-42 Heating Valve Output
equip ref: Bravo VAV 2-42
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:09.627-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:09.627-04:00

Bravo VAV 2-42 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 2-42 Supply Air Temperature
equip ref: Bravo VAV 2-42
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:11.125-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:11.125-04:00

Bravo VAV 2-42 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 2-42 Zone Air Temp Setpoint
equip ref: Bravo VAV 2-42
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:10.745-04:00

Bravo VAV 2-42 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 2-42 Zone Temperature
equip ref: Bravo VAV 2-42
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:09.752-04:00

Bravo VAV 2-43
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-2
dis: Bravo VAV 2-43
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:141°F, designHotWaterPower:4.7MMBTU/h, designHotWaterFlow:0.75gal/min, designAirFlow:350cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 141
  design hot water power: 4.7
  design hot water flow: 0.75
  design air flow: 350

Bravo VAV 2-43 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 2-43 Damper Output
equip ref: Bravo VAV 2-43
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:10.87-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:10.87-04:00

Bravo VAV 2-43 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 2-43 Discharge Air Flow
equip ref: Bravo VAV 2-43
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:10.126-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:10.126-04:00

Bravo VAV 2-43 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 2-43 Discharge Air Flow Setpoint
equip ref: Bravo VAV 2-43
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:10.497-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:10.497-04:00

Bravo VAV 2-43 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 2-43 Heating Valve Output
equip ref: Bravo VAV 2-43
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:11.125-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:11.125-04:00

Bravo VAV 2-43 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 2-43 Supply Air Temperature
equip ref: Bravo VAV 2-43
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:10.126-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:10.126-04:00

Bravo VAV 2-43 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 2-43 Zone Air Temp Setpoint
equip ref: Bravo VAV 2-43
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:10.374-04:00

Bravo VAV 2-43 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 2-43 Zone Temperature
equip ref: Bravo VAV 2-43
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:10.249-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:10.249-04:00

Bravo VAV 2-44
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-2
dis: Bravo VAV 2-44
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:149°F, designHotWaterPower:9.2MMBTU/h, designHotWaterFlow:1gal/min, designAirFlow:450cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 149
  design hot water power: 9.2
  design hot water flow: 1
  design air flow: 450

Bravo VAV 2-44 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 2-44 Damper Output
equip ref: Bravo VAV 2-44
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:07.473-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:07.473-04:00

Bravo VAV 2-44 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 2-44 Discharge Air Flow
equip ref: Bravo VAV 2-44
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:10.003-04:00

Bravo VAV 2-44 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 2-44 Discharge Air Flow Setpoint
equip ref: Bravo VAV 2-44
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:07.598-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:07.598-04:00

Bravo VAV 2-44 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 2-44 Heating Valve Output
equip ref: Bravo VAV 2-44
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:10.995-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:10.995-04:00

Bravo VAV 2-44 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 2-44 Supply Air Temperature
equip ref: Bravo VAV 2-44
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:10.374-04:00

Bravo VAV 2-44 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 2-44 Zone Air Temp Setpoint
equip ref: Bravo VAV 2-44
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:09.627-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:09.627-04:00

Bravo VAV 2-44 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 2-44 Zone Temperature
equip ref: Bravo VAV 2-44
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:11.125-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:11.125-04:00

Bravo VAV 2-45
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-2
dis: Bravo VAV 2-45
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:150°F, designHotWaterPower:17.8MMBTU/h, designHotWaterFlow:1.75gal/min, designAirFlow:600cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 150
  design hot water power: 17.8
  design hot water flow: 1.75
  design air flow: 600

Bravo VAV 2-45 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 2-45 Damper Output
equip ref: Bravo VAV 2-45
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:10.374-04:00

Bravo VAV 2-45 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 2-45 Discharge Air Flow
equip ref: Bravo VAV 2-45
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:10.745-04:00

Bravo VAV 2-45 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 2-45 Discharge Air Flow Setpoint
equip ref: Bravo VAV 2-45
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:10.374-04:00

Bravo VAV 2-45 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 2-45 Heating Valve Output
equip ref: Bravo VAV 2-45
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:09.879-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:09.879-04:00

Bravo VAV 2-45 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 2-45 Supply Air Temperature
equip ref: Bravo VAV 2-45
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:10.497-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:10.497-04:00

Bravo VAV 2-45 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 2-45 Zone Air Temp Setpoint
equip ref: Bravo VAV 2-45
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:10.374-04:00

Bravo VAV 2-45 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 2-45 Zone Temperature
equip ref: Bravo VAV 2-45
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:10.497-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:10.497-04:00

Bravo VAV 2-46
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-2
dis: Bravo VAV 2-46
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:153°F, designHotWaterPower:9.8MMBTU/h, designHotWaterFlow:1.25gal/min, designAirFlow:475cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 153
  design hot water power: 9.8
  design hot water flow: 1.25
  design air flow: 475

Bravo VAV 2-46 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 2-46 Damper Output
equip ref: Bravo VAV 2-46
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:10.003-04:00

Bravo VAV 2-46 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 2-46 Discharge Air Flow
equip ref: Bravo VAV 2-46
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:10.249-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:10.249-04:00

Bravo VAV 2-46 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 2-46 Discharge Air Flow Setpoint
equip ref: Bravo VAV 2-46
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:13.145-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:13.145-04:00

Bravo VAV 2-46 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 2-46 Heating Valve Output
equip ref: Bravo VAV 2-46
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:10.62-04:00

Bravo VAV 2-46 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 2-46 Supply Air Temperature
equip ref: Bravo VAV 2-46
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:10.745-04:00

Bravo VAV 2-46 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 2-46 Zone Air Temp Setpoint
equip ref: Bravo VAV 2-46
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:07.598-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:07.598-04:00

Bravo VAV 2-46 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 2-46 Zone Temperature
equip ref: Bravo VAV 2-46
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:10.003-04:00

Bravo VAV 2-47
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-2
dis: Bravo VAV 2-47
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:149°F, designHotWaterPower:25.9MMBTU/h, designHotWaterFlow:2.5gal/min, designAirFlow:1400cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 149
  design hot water power: 25.9
  design hot water flow: 2.5
  design air flow: 1400

Bravo VAV 2-47 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 2-47 Damper Output
equip ref: Bravo VAV 2-47
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:10.374-04:00

Bravo VAV 2-47 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 2-47 Discharge Air Flow
equip ref: Bravo VAV 2-47
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:11.258-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:11.258-04:00

Bravo VAV 2-47 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 2-47 Discharge Air Flow Setpoint
equip ref: Bravo VAV 2-47
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:07.598-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:07.598-04:00

Bravo VAV 2-47 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 2-47 Heating Valve Output
equip ref: Bravo VAV 2-47
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:07.598-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:07.598-04:00

Bravo VAV 2-47 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 2-47 Supply Air Temperature
equip ref: Bravo VAV 2-47
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:13.145-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:13.145-04:00

Bravo VAV 2-47 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 2-47 Zone Air Temp Setpoint
equip ref: Bravo VAV 2-47
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:11.125-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:11.125-04:00

Bravo VAV 2-47 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 2-47 Zone Temperature
equip ref: Bravo VAV 2-47
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:07.598-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:07.598-04:00

Bravo VAV 2-48
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-2
dis: Bravo VAV 2-48
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:153°F, designHotWaterPower:9.5MMBTU/h, designHotWaterFlow:1.25gal/min, designAirFlow:475cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 153
  design hot water power: 9.5
  design hot water flow: 1.25
  design air flow: 475

Bravo VAV 2-48 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 2-48 Damper Output
equip ref: Bravo VAV 2-48
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:10.003-04:00

Bravo VAV 2-48 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 2-48 Discharge Air Flow
equip ref: Bravo VAV 2-48
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:07.721-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:07.721-04:00

Bravo VAV 2-48 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 2-48 Discharge Air Flow Setpoint
equip ref: Bravo VAV 2-48
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:10.62-04:00

Bravo VAV 2-48 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 2-48 Heating Valve Output
equip ref: Bravo VAV 2-48
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:10.126-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:10.126-04:00

Bravo VAV 2-48 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 2-48 Supply Air Temperature
equip ref: Bravo VAV 2-48
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:10.62-04:00

Bravo VAV 2-48 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 2-48 Zone Air Temp Setpoint
equip ref: Bravo VAV 2-48
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:10.003-04:00

Bravo VAV 2-48 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 2-48 Zone Temperature
equip ref: Bravo VAV 2-48
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:10.995-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:10.995-04:00

Bravo VAV 2-49
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-2
dis: Bravo VAV 2-49
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:153°F, designHotWaterPower:9.5MMBTU/h, designHotWaterFlow:1.25gal/min, designAirFlow:475cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 153
  design hot water power: 9.5
  design hot water flow: 1.25
  design air flow: 475

Bravo VAV 2-49 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 2-49 Damper Output
equip ref: Bravo VAV 2-49
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:10.003-04:00

Bravo VAV 2-49 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 2-49 Discharge Air Flow
equip ref: Bravo VAV 2-49
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:07.598-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:07.598-04:00

Bravo VAV 2-49 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 2-49 Discharge Air Flow Setpoint
equip ref: Bravo VAV 2-49
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:10.497-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:10.497-04:00

Bravo VAV 2-49 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 2-49 Heating Valve Output
equip ref: Bravo VAV 2-49
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:10.126-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:10.126-04:00

Bravo VAV 2-49 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 2-49 Supply Air Temperature
equip ref: Bravo VAV 2-49
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:09.879-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:09.879-04:00

Bravo VAV 2-49 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 2-49 Zone Air Temp Setpoint
equip ref: Bravo VAV 2-49
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:10.497-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:10.497-04:00

Bravo VAV 2-49 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 2-49 Zone Temperature
equip ref: Bravo VAV 2-49
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:07.473-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:07.473-04:00

Bravo VAV 2-5
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-2
dis: Bravo VAV 2-5
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:151°F, designHotWaterPower:3.1MMBTU/h, designHotWaterFlow:0.5gal/min, designAirFlow:200cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 151
  design hot water power: 3.1
  design hot water flow: 0.5
  design air flow: 200

Bravo VAV 2-5 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 2-5 Damper Output
equip ref: Bravo VAV 2-5
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:10.745-04:00

Bravo VAV 2-5 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 2-5 Discharge Air Flow
equip ref: Bravo VAV 2-5
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:07.598-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:07.598-04:00

Bravo VAV 2-5 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 2-5 Discharge Air Flow Setpoint
equip ref: Bravo VAV 2-5
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:09.879-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:09.879-04:00

Bravo VAV 2-5 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 2-5 Heating Valve Output
equip ref: Bravo VAV 2-5
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:10.87-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:10.87-04:00

Bravo VAV 2-5 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 2-5 Supply Air Temperature
equip ref: Bravo VAV 2-5
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:09.627-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:09.627-04:00

Bravo VAV 2-5 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 2-5 Zone Air Temp Setpoint
equip ref: Bravo VAV 2-5
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:07.598-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:07.598-04:00

Bravo VAV 2-5 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 2-5 Zone Temperature
equip ref: Bravo VAV 2-5
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:07.473-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:07.473-04:00

Bravo VAV 2-50
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-2
dis: Bravo VAV 2-50
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:153°F, designHotWaterPower:9.8MMBTU/h, designHotWaterFlow:1.25gal/min, designAirFlow:475cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 153
  design hot water power: 9.8
  design hot water flow: 1.25
  design air flow: 475

Bravo VAV 2-50 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 2-50 Damper Output
equip ref: Bravo VAV 2-50
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:11.125-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:11.125-04:00

Bravo VAV 2-50 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 2-50 Discharge Air Flow
equip ref: Bravo VAV 2-50
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:09.879-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:09.879-04:00

Bravo VAV 2-50 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 2-50 Discharge Air Flow Setpoint
equip ref: Bravo VAV 2-50
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:10.87-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:10.87-04:00

Bravo VAV 2-50 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 2-50 Heating Valve Output
equip ref: Bravo VAV 2-50
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:10.995-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:10.995-04:00

Bravo VAV 2-50 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 2-50 Supply Air Temperature
equip ref: Bravo VAV 2-50
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:10.62-04:00

Bravo VAV 2-50 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 2-50 Zone Air Temp Setpoint
equip ref: Bravo VAV 2-50
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:11.125-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:11.125-04:00

Bravo VAV 2-50 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 2-50 Zone Temperature
equip ref: Bravo VAV 2-50
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:07.598-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:07.598-04:00

Bravo VAV 2-6
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-2
dis: Bravo VAV 2-6
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:148°F, designHotWaterPower:4.7MMBTU/h, designHotWaterFlow:0.5gal/min, designAirFlow:350cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 148
  design hot water power: 4.7
  design hot water flow: 0.5
  design air flow: 350

Bravo VAV 2-6 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 2-6 Damper Output
equip ref: Bravo VAV 2-6
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:09.752-04:00

Bravo VAV 2-6 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 2-6 Discharge Air Flow
equip ref: Bravo VAV 2-6
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:11.258-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:11.258-04:00

Bravo VAV 2-6 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 2-6 Discharge Air Flow Setpoint
equip ref: Bravo VAV 2-6
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:10.003-04:00

Bravo VAV 2-6 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 2-6 Heating Valve Output
equip ref: Bravo VAV 2-6
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:09.627-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:09.627-04:00

Bravo VAV 2-6 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 2-6 Supply Air Temperature
equip ref: Bravo VAV 2-6
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:10.87-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:10.87-04:00

Bravo VAV 2-6 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 2-6 Zone Air Temp Setpoint
equip ref: Bravo VAV 2-6
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:10.745-04:00

Bravo VAV 2-6 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 2-6 Zone Temperature
equip ref: Bravo VAV 2-6
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:09.879-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:09.879-04:00

Bravo VAV 2-7
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-2
dis: Bravo VAV 2-7
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:152°F, designHotWaterPower:10MMBTU/h, designHotWaterFlow:1.25gal/min, designAirFlow:650cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 152
  design hot water power: 10
  design hot water flow: 1.25
  design air flow: 650

Bravo VAV 2-7 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 2-7 Damper Output
equip ref: Bravo VAV 2-7
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:10.003-04:00

Bravo VAV 2-7 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 2-7 Discharge Air Flow
equip ref: Bravo VAV 2-7
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:10.995-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:10.995-04:00

Bravo VAV 2-7 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 2-7 Discharge Air Flow Setpoint
equip ref: Bravo VAV 2-7
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:07.598-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:07.598-04:00

Bravo VAV 2-7 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 2-7 Heating Valve Output
equip ref: Bravo VAV 2-7
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:09.752-04:00

Bravo VAV 2-7 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 2-7 Supply Air Temperature
equip ref: Bravo VAV 2-7
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:09.879-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:09.879-04:00

Bravo VAV 2-7 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 2-7 Zone Air Temp Setpoint
equip ref: Bravo VAV 2-7
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:10.126-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:10.126-04:00

Bravo VAV 2-7 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 2-7 Zone Temperature
equip ref: Bravo VAV 2-7
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:10.003-04:00

Bravo VAV 2-8
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-2
dis: Bravo VAV 2-8
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:153°F, designHotWaterPower:4.1MMBTU/h, designHotWaterFlow:0.75gal/min, designAirFlow:300cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 153
  design hot water power: 4.1
  design hot water flow: 0.75
  design air flow: 300

Bravo VAV 2-8 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 2-8 Damper Output
equip ref: Bravo VAV 2-8
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:10.249-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:10.249-04:00

Bravo VAV 2-8 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 2-8 Discharge Air Flow
equip ref: Bravo VAV 2-8
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:10.745-04:00

Bravo VAV 2-8 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 2-8 Discharge Air Flow Setpoint
equip ref: Bravo VAV 2-8
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:10.995-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:10.995-04:00

Bravo VAV 2-8 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 2-8 Heating Valve Output
equip ref: Bravo VAV 2-8
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:09.752-04:00

Bravo VAV 2-8 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 2-8 Supply Air Temperature
equip ref: Bravo VAV 2-8
kind: Str
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:07.598-04:00 New_York, pointType:, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:07.598-04:00

Bravo VAV 2-8 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 2-8 Zone Air Temp Setpoint
equip ref: Bravo VAV 2-8
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:10.126-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:10.126-04:00

Bravo VAV 2-8 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 2-8 Zone Temperature
equip ref: Bravo VAV 2-8
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:10.249-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:10.249-04:00

Bravo VAV 2-9
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-2
dis: Bravo VAV 2-9
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:149°F, designHotWaterPower:8.9MMBTU/h, designHotWaterFlow:1gal/min, designAirFlow:450cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 149
  design hot water power: 8.9
  design hot water flow: 1
  design air flow: 450

Bravo VAV 2-9 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 2-9 Damper Output
equip ref: Bravo VAV 2-9
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:07.598-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:07.598-04:00

Bravo VAV 2-9 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 2-9 Discharge Air Flow
equip ref: Bravo VAV 2-9
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:09.627-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:09.627-04:00

Bravo VAV 2-9 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 2-9 Discharge Air Flow Setpoint
equip ref: Bravo VAV 2-9
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:07.473-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:07.473-04:00

Bravo VAV 2-9 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 2-9 Heating Valve Output
equip ref: Bravo VAV 2-9
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:10.003-04:00

Bravo VAV 2-9 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 2-9 Supply Air Temperature
equip ref: Bravo VAV 2-9
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:10.003-04:00

Bravo VAV 2-9 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 2-9 Zone Air Temp Setpoint
equip ref: Bravo VAV 2-9
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:10.745-04:00

Bravo VAV 2-9 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 2-9 Zone Temperature
equip ref: Bravo VAV 2-9
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:10.374-04:00

Bravo VAV 3-1
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-3
dis: Bravo VAV 3-1
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:150°F, designHotWaterPower:14.1MMBTU/h, designHotWaterFlow:2.5gal/min, designAirFlow:1300cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 150
  design hot water power: 14.1
  design hot water flow: 2.5
  design air flow: 1300

Bravo VAV 3-1 Air Damper Command
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 3-1 Air Damper Command
equip ref: Bravo VAV 3-1
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-14T01:00:05.167-04:00 New_York, pointType:, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-14T01:00:05.167-04:00

Bravo VAV 3-1 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 3-1 Discharge Air Flow
equip ref: Bravo VAV 3-1
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:10.87-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:10.87-04:00

Bravo VAV 3-1 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 3-1 Discharge Air Flow Setpoint
equip ref: Bravo VAV 3-1
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:10.497-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:10.497-04:00

Bravo VAV 3-1 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 3-1 Heating Valve Output
equip ref: Bravo VAV 3-1
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:10.003-04:00

Bravo VAV 3-1 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 3-1 Supply Air Temperature
equip ref: Bravo VAV 3-1
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:10.003-04:00

Bravo VAV 3-1 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 3-1 Zone Air Temp Setpoint
equip ref: Bravo VAV 3-1
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:10.003-04:00

Bravo VAV 3-1 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 3-1 Zone Temperature
equip ref: Bravo VAV 3-1
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:10.745-04:00

Bravo VAV 3-10
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-3
dis: Bravo VAV 3-10
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:151°F, designHotWaterPower:7.3MMBTU/h, designHotWaterFlow:0.75gal/min, designAirFlow:350cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 151
  design hot water power: 7.3
  design hot water flow: 0.75
  design air flow: 350

Bravo VAV 3-10 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 3-10 Damper Output
equip ref: Bravo VAV 3-10
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:10.249-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:10.249-04:00

Bravo VAV 3-10 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 3-10 Discharge Air Flow
equip ref: Bravo VAV 3-10
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:10.003-04:00

Bravo VAV 3-10 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 3-10 Discharge Air Flow Setpoint
equip ref: Bravo VAV 3-10
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:10.995-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:10.995-04:00

Bravo VAV 3-10 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 3-10 Heating Valve Output
equip ref: Bravo VAV 3-10
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:10.497-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:10.497-04:00

Bravo VAV 3-10 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 3-10 Supply Air Temperature
equip ref: Bravo VAV 3-10
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:09.627-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:09.627-04:00

Bravo VAV 3-10 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 3-10 Zone Air Temp Setpoint
equip ref: Bravo VAV 3-10
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:10.003-04:00

Bravo VAV 3-10 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 3-10 Zone Temperature
equip ref: Bravo VAV 3-10
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:10.62-04:00

Bravo VAV 3-11
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-3
dis: Bravo VAV 3-11
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:150°F, designHotWaterPower:22.7MMBTU/h, designHotWaterFlow:2.25gal/min, designAirFlow:1100cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 150
  design hot water power: 22.7
  design hot water flow: 2.25
  design air flow: 1100

Bravo VAV 3-11 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 3-11 Damper Output
equip ref: Bravo VAV 3-11
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:10.126-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:10.126-04:00

Bravo VAV 3-11 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 3-11 Discharge Air Flow
equip ref: Bravo VAV 3-11
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:10.126-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:10.126-04:00

Bravo VAV 3-11 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 3-11 Discharge Air Flow Setpoint
equip ref: Bravo VAV 3-11
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:10.003-04:00

Bravo VAV 3-11 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 3-11 Heating Valve Output
equip ref: Bravo VAV 3-11
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:07.598-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:07.598-04:00

Bravo VAV 3-11 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 3-11 Supply Air Temperature
equip ref: Bravo VAV 3-11
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:13.145-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:13.145-04:00

Bravo VAV 3-11 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 3-11 Zone Air Temp Setpoint
equip ref: Bravo VAV 3-11
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:10.87-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:10.87-04:00

Bravo VAV 3-11 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 3-11 Zone Temperature
equip ref: Bravo VAV 3-11
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:10.995-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:10.995-04:00

Bravo VAV 3-12
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-3
dis: Bravo VAV 3-12
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:149°F, designHotWaterPower:9.8MMBTU/h, designHotWaterFlow:1.5gal/min, designAirFlow:1000cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 149
  design hot water power: 9.8
  design hot water flow: 1.5
  design air flow: 1000

Bravo VAV 3-12 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 3-12 Damper Output
equip ref: Bravo VAV 3-12
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:09.752-04:00

Bravo VAV 3-12 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 3-12 Discharge Air Flow
equip ref: Bravo VAV 3-12
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:09.879-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:09.879-04:00

Bravo VAV 3-12 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 3-12 Discharge Air Flow Setpoint
equip ref: Bravo VAV 3-12
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:10.126-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:10.126-04:00

Bravo VAV 3-12 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 3-12 Heating Valve Output
equip ref: Bravo VAV 3-12
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:10.497-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:10.497-04:00

Bravo VAV 3-12 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 3-12 Supply Air Temperature
equip ref: Bravo VAV 3-12
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:10.87-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:10.87-04:00

Bravo VAV 3-12 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 3-12 Zone Air Temp Setpoint
equip ref: Bravo VAV 3-12
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:10.62-04:00

Bravo VAV 3-12 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 3-12 Zone Temperature
equip ref: Bravo VAV 3-12
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:10.62-04:00

Bravo VAV 3-13
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-3
dis: Bravo VAV 3-13
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:151°F, designHotWaterPower:5.3MMBTU/h, designHotWaterFlow:0.75gal/min, designAirFlow:350cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 151
  design hot water power: 5.3
  design hot water flow: 0.75
  design air flow: 350

Bravo VAV 3-13 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 3-13 Damper Output
equip ref: Bravo VAV 3-13
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:10.003-04:00

Bravo VAV 3-13 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 3-13 Discharge Air Flow
equip ref: Bravo VAV 3-13
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:10.003-04:00

Bravo VAV 3-13 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 3-13 Discharge Air Flow Setpoint
equip ref: Bravo VAV 3-13
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:10.126-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:10.126-04:00

Bravo VAV 3-13 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 3-13 Heating Valve Output
equip ref: Bravo VAV 3-13
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:10.126-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:10.126-04:00

Bravo VAV 3-13 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 3-13 Supply Air Temperature
equip ref: Bravo VAV 3-13
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:10.745-04:00

Bravo VAV 3-13 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 3-13 Zone Air Temp Setpoint
equip ref: Bravo VAV 3-13
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:10.745-04:00

Bravo VAV 3-13 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 3-13 Zone Temperature
equip ref: Bravo VAV 3-13
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:10.003-04:00

Bravo VAV 3-14
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-3
dis: Bravo VAV 3-14
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:149°F, designHotWaterPower:5.4MMBTU/h, designHotWaterFlow:1gal/min, designAirFlow:500cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 149
  design hot water power: 5.4
  design hot water flow: 1
  design air flow: 500

Bravo VAV 3-14 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 3-14 Damper Output
equip ref: Bravo VAV 3-14
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:10.497-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:10.497-04:00

Bravo VAV 3-14 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 3-14 Discharge Air Flow
equip ref: Bravo VAV 3-14
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:09.627-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:09.627-04:00

Bravo VAV 3-14 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 3-14 Discharge Air Flow Setpoint
equip ref: Bravo VAV 3-14
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:11.258-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:11.258-04:00

Bravo VAV 3-14 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 3-14 Heating Valve Output
equip ref: Bravo VAV 3-14
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:13.145-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:13.145-04:00

Bravo VAV 3-14 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 3-14 Supply Air Temperature
equip ref: Bravo VAV 3-14
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:10.249-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:10.249-04:00

Bravo VAV 3-14 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 3-14 Zone Air Temp Setpoint
equip ref: Bravo VAV 3-14
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:11.125-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:11.125-04:00

Bravo VAV 3-14 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 3-14 Zone Temperature
equip ref: Bravo VAV 3-14
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:10.003-04:00

Bravo VAV 3-15
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-3
dis: Bravo VAV 3-15
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:147°F, designHotWaterPower:2.7MMBTU/h, designHotWaterFlow:0.5gal/min, designAirFlow:250cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 147
  design hot water power: 2.7
  design hot water flow: 0.5
  design air flow: 250

Bravo VAV 3-15 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 3-15 Damper Output
equip ref: Bravo VAV 3-15
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:10.374-04:00

Bravo VAV 3-15 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 3-15 Discharge Air Flow
equip ref: Bravo VAV 3-15
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:10.497-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:10.497-04:00

Bravo VAV 3-15 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 3-15 Discharge Air Flow Setpoint
equip ref: Bravo VAV 3-15
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:07.721-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:07.721-04:00

Bravo VAV 3-15 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 3-15 Heating Valve Output
equip ref: Bravo VAV 3-15
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:07.721-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:07.721-04:00

Bravo VAV 3-15 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 3-15 Supply Air Temperature
equip ref: Bravo VAV 3-15
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:07.721-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:07.721-04:00

Bravo VAV 3-15 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 3-15 Zone Air Temp Setpoint
equip ref: Bravo VAV 3-15
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:09.627-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:09.627-04:00

Bravo VAV 3-15 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 3-15 Zone Temperature
equip ref: Bravo VAV 3-15
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:09.752-04:00

Bravo VAV 3-16
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-3
dis: Bravo VAV 3-16
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:153°F, designHotWaterPower:3.3MMBTU/h, designHotWaterFlow:0.75gal/min, designAirFlow:300cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 153
  design hot water power: 3.3
  design hot water flow: 0.75
  design air flow: 300

Bravo VAV 3-16 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 3-16 Damper Output
equip ref: Bravo VAV 3-16
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:10.126-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:10.126-04:00

Bravo VAV 3-16 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 3-16 Discharge Air Flow
equip ref: Bravo VAV 3-16
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:10.374-04:00

Bravo VAV 3-16 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 3-16 Discharge Air Flow Setpoint
equip ref: Bravo VAV 3-16
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:09.627-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:09.627-04:00

Bravo VAV 3-16 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 3-16 Heating Valve Output
equip ref: Bravo VAV 3-16
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:09.752-04:00

Bravo VAV 3-16 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 3-16 Supply Air Temperature
equip ref: Bravo VAV 3-16
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:10.745-04:00

Bravo VAV 3-16 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 3-16 Zone Air Temp Setpoint
equip ref: Bravo VAV 3-16
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:10.745-04:00

Bravo VAV 3-16 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 3-16 Zone Temperature
equip ref: Bravo VAV 3-16
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:09.752-04:00

Bravo VAV 3-17
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-3
dis: Bravo VAV 3-17
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:153°F, designHotWaterPower:3.3MMBTU/h, designHotWaterFlow:0.75gal/min, designAirFlow:300cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 153
  design hot water power: 3.3
  design hot water flow: 0.75
  design air flow: 300

Bravo VAV 3-17 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 3-17 Damper Output
equip ref: Bravo VAV 3-17
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:10.126-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:10.126-04:00

Bravo VAV 3-17 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 3-17 Discharge Air Flow
equip ref: Bravo VAV 3-17
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:10.87-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:10.87-04:00

Bravo VAV 3-17 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 3-17 Discharge Air Flow Setpoint
equip ref: Bravo VAV 3-17
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:09.752-04:00

Bravo VAV 3-17 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 3-17 Heating Valve Output
equip ref: Bravo VAV 3-17
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:07.473-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:07.473-04:00

Bravo VAV 3-17 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 3-17 Supply Air Temperature
equip ref: Bravo VAV 3-17
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:07.598-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:07.598-04:00

Bravo VAV 3-17 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 3-17 Zone Air Temp Setpoint
equip ref: Bravo VAV 3-17
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:07.598-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:07.598-04:00

Bravo VAV 3-17 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 3-17 Zone Temperature
equip ref: Bravo VAV 3-17
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:09.752-04:00

Bravo VAV 3-18
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-3
dis: Bravo VAV 3-18
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:150°F, designHotWaterPower:12.4MMBTU/h, designHotWaterFlow:1.5gal/min, designAirFlow:500cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 150
  design hot water power: 12.4
  design hot water flow: 1.5
  design air flow: 500

Bravo VAV 3-18 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 3-18 Damper Output
equip ref: Bravo VAV 3-18
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:10.497-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:10.497-04:00

Bravo VAV 3-18 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 3-18 Discharge Air Flow
equip ref: Bravo VAV 3-18
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:09.752-04:00

Bravo VAV 3-18 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 3-18 Discharge Air Flow Setpoint
equip ref: Bravo VAV 3-18
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:09.627-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:09.627-04:00

Bravo VAV 3-18 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 3-18 Heating Valve Output
equip ref: Bravo VAV 3-18
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:10.374-04:00

Bravo VAV 3-18 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 3-18 Supply Air Temperature
equip ref: Bravo VAV 3-18
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:10.003-04:00

Bravo VAV 3-18 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 3-18 Zone Air Temp Setpoint
equip ref: Bravo VAV 3-18
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:10.003-04:00

Bravo VAV 3-18 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 3-18 Zone Temperature
equip ref: Bravo VAV 3-18
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:09.879-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:09.879-04:00

Bravo VAV 3-19
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-3
dis: Bravo VAV 3-19
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:155°F, designHotWaterPower:2.1MMBTU/h, designHotWaterFlow:0.5gal/min, designAirFlow:150cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 155
  design hot water power: 2.1
  design hot water flow: 0.5
  design air flow: 150

Bravo VAV 3-19 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 3-19 Damper Output
equip ref: Bravo VAV 3-19
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:09.627-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:09.627-04:00

Bravo VAV 3-19 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 3-19 Discharge Air Flow
equip ref: Bravo VAV 3-19
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:10.62-04:00

Bravo VAV 3-19 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 3-19 Discharge Air Flow Setpoint
equip ref: Bravo VAV 3-19
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:09.752-04:00

Bravo VAV 3-19 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 3-19 Heating Valve Output
equip ref: Bravo VAV 3-19
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:10.87-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:10.87-04:00

Bravo VAV 3-19 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 3-19 Supply Air Temperature
equip ref: Bravo VAV 3-19
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:10.249-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:10.249-04:00

Bravo VAV 3-19 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 3-19 Zone Air Temp Setpoint
equip ref: Bravo VAV 3-19
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:09.879-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:09.879-04:00

Bravo VAV 3-19 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 3-19 Zone Temperature
equip ref: Bravo VAV 3-19
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:11.125-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:11.125-04:00

Bravo VAV 3-2
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-3
dis: Bravo VAV 3-2
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:149°F, designHotWaterPower:8.7MMBTU/h, designHotWaterFlow:1.5gal/min, designAirFlow:800cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 149
  design hot water power: 8.7
  design hot water flow: 1.5
  design air flow: 800

Bravo VAV 3-2 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 3-2 Damper Output
equip ref: Bravo VAV 3-2
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:10.003-04:00

Bravo VAV 3-2 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 3-2 Discharge Air Flow
equip ref: Bravo VAV 3-2
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:10.249-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:10.249-04:00

Bravo VAV 3-2 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 3-2 Discharge Air Flow Setpoint
equip ref: Bravo VAV 3-2
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:09.879-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:09.879-04:00

Bravo VAV 3-2 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 3-2 Heating Valve Output
equip ref: Bravo VAV 3-2
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:10.62-04:00

Bravo VAV 3-2 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 3-2 Supply Air Temperature
equip ref: Bravo VAV 3-2
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:10.374-04:00

Bravo VAV 3-2 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 3-2 Zone Air Temp Setpoint
equip ref: Bravo VAV 3-2
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:10.62-04:00

Bravo VAV 3-2 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 3-2 Zone Temperature
equip ref: Bravo VAV 3-2
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:10.374-04:00

Bravo VAV 3-20
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-3
dis: Bravo VAV 3-20
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:153°F, designHotWaterPower:4.1MMBTU/h, designHotWaterFlow:0.75gal/min, designAirFlow:300cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 153
  design hot water power: 4.1
  design hot water flow: 0.75
  design air flow: 300

Bravo VAV 3-20 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 3-20 Damper Output
equip ref: Bravo VAV 3-20
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:11.258-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:11.258-04:00

Bravo VAV 3-20 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 3-20 Discharge Air Flow
equip ref: Bravo VAV 3-20
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:09.752-04:00

Bravo VAV 3-20 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 3-20 Discharge Air Flow Setpoint
equip ref: Bravo VAV 3-20
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:10.62-04:00

Bravo VAV 3-20 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 3-20 Heating Valve Output
equip ref: Bravo VAV 3-20
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:10.249-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:10.249-04:00

Bravo VAV 3-20 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 3-20 Supply Air Temperature
equip ref: Bravo VAV 3-20
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:10.995-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:10.995-04:00

Bravo VAV 3-20 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 3-20 Zone Air Temp Setpoint
equip ref: Bravo VAV 3-20
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:10.995-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:10.995-04:00

Bravo VAV 3-20 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 3-20 Zone Temperature
equip ref: Bravo VAV 3-20
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:09.752-04:00

Bravo VAV 3-21
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-3
dis: Bravo VAV 3-21
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:153°F, designHotWaterPower:6.5MMBTU/h, designHotWaterFlow:1gal/min, designAirFlow:300cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 153
  design hot water power: 6.5
  design hot water flow: 1
  design air flow: 300

Bravo VAV 3-21 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 3-21 Damper Output
equip ref: Bravo VAV 3-21
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:13.145-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:13.145-04:00

Bravo VAV 3-21 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 3-21 Discharge Air Flow
equip ref: Bravo VAV 3-21
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:11.258-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:11.258-04:00

Bravo VAV 3-21 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 3-21 Discharge Air Flow Setpoint
equip ref: Bravo VAV 3-21
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:10.497-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:10.497-04:00

Bravo VAV 3-21 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 3-21 Heating Valve Output
equip ref: Bravo VAV 3-21
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:07.598-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:07.598-04:00

Bravo VAV 3-21 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 3-21 Supply Air Temperature
equip ref: Bravo VAV 3-21
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:09.879-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:09.879-04:00

Bravo VAV 3-21 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 3-21 Zone Air Temp Setpoint
equip ref: Bravo VAV 3-21
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:11.125-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:11.125-04:00

Bravo VAV 3-21 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 3-21 Zone Temperature
equip ref: Bravo VAV 3-21
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:09.752-04:00

Bravo VAV 3-22
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-3
dis: Bravo VAV 3-22
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:151°F, designHotWaterPower:29.2MMBTU/h, designHotWaterFlow:3.5gal/min, designAirFlow:1250cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 151
  design hot water power: 29.2
  design hot water flow: 3.5
  design air flow: 1250

Bravo VAV 3-22 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 3-22 Damper Output
equip ref: Bravo VAV 3-22
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:10.62-04:00

Bravo VAV 3-22 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 3-22 Discharge Air Flow
equip ref: Bravo VAV 3-22
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:10.745-04:00

Bravo VAV 3-22 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 3-22 Discharge Air Flow Setpoint
equip ref: Bravo VAV 3-22
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:10.249-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:10.249-04:00

Bravo VAV 3-22 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 3-22 Heating Valve Output
equip ref: Bravo VAV 3-22
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:10.003-04:00

Bravo VAV 3-22 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 3-22 Supply Air Temperature
equip ref: Bravo VAV 3-22
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:07.598-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:07.598-04:00

Bravo VAV 3-22 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 3-22 Zone Air Temp Setpoint
equip ref: Bravo VAV 3-22
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:10.249-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:10.249-04:00

Bravo VAV 3-22 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 3-22 Zone Temperature
equip ref: Bravo VAV 3-22
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:11.125-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:11.125-04:00

Bravo VAV 3-23
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-3
dis: Bravo VAV 3-23
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:151°F, designHotWaterPower:2.2MMBTU/h, designHotWaterFlow:0.5gal/min, designAirFlow:200cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 151
  design hot water power: 2.2
  design hot water flow: 0.5
  design air flow: 200

Bravo VAV 3-23 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 3-23 Damper Output
equip ref: Bravo VAV 3-23
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, pointType:, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:10.62-04:00

Bravo VAV 3-23 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 3-23 Discharge Air Flow
equip ref: Bravo VAV 3-23
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:10.745-04:00

Bravo VAV 3-23 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 3-23 Discharge Air Flow Setpoint
equip ref: Bravo VAV 3-23
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:10.497-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:10.497-04:00

Bravo VAV 3-23 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 3-23 Heating Valve Output
equip ref: Bravo VAV 3-23
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:09.879-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:09.879-04:00

Bravo VAV 3-23 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 3-23 Supply Air Temperature
equip ref: Bravo VAV 3-23
kind: Str
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:10.126-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:10.126-04:00

Bravo VAV 3-23 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 3-23 Zone Air Temp Setpoint
equip ref: Bravo VAV 3-23
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:10.374-04:00

Bravo VAV 3-23 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 3-23 Zone Temperature
equip ref: Bravo VAV 3-23
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:10.126-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:10.126-04:00

Bravo VAV 3-24
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-3
dis: Bravo VAV 3-24
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:153°F, designHotWaterPower:6.4MMBTU/h, designHotWaterFlow:0.75gal/min, designAirFlow:300cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 153
  design hot water power: 6.4
  design hot water flow: 0.75
  design air flow: 300

Bravo VAV 3-24 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 3-24 Damper Output
equip ref: Bravo VAV 3-24
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:10.497-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:10.497-04:00

Bravo VAV 3-24 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 3-24 Discharge Air Flow
equip ref: Bravo VAV 3-24
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:10.497-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:10.497-04:00

Bravo VAV 3-24 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 3-24 Discharge Air Flow Setpoint
equip ref: Bravo VAV 3-24
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:10.003-04:00

Bravo VAV 3-24 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 3-24 Heating Valve Output
equip ref: Bravo VAV 3-24
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:10.995-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:10.995-04:00

Bravo VAV 3-24 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 3-24 Supply Air Temperature
equip ref: Bravo VAV 3-24
kind: Str
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:11.125-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:11.125-04:00

Bravo VAV 3-24 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 3-24 Zone Air Temp Setpoint
equip ref: Bravo VAV 3-24
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:09.879-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:09.879-04:00

Bravo VAV 3-24 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 3-24 Zone Temperature
equip ref: Bravo VAV 3-24
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:07.473-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:07.473-04:00

Bravo VAV 3-25
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-3
dis: Bravo VAV 3-25
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:149°F, designHotWaterPower:16.6MMBTU/h, designHotWaterFlow:2gal/min, designAirFlow:500cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 149
  design hot water power: 16.6
  design hot water flow: 2
  design air flow: 500

Bravo VAV 3-25 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 3-25 Damper Output
equip ref: Bravo VAV 3-25
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:07.473-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:07.473-04:00

Bravo VAV 3-25 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 3-25 Discharge Air Flow
equip ref: Bravo VAV 3-25
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:10.497-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:10.497-04:00

Bravo VAV 3-25 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 3-25 Discharge Air Flow Setpoint
equip ref: Bravo VAV 3-25
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:11.125-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:11.125-04:00

Bravo VAV 3-25 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 3-25 Heating Valve Output
equip ref: Bravo VAV 3-25
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:10.62-04:00

Bravo VAV 3-25 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 3-25 Supply Air Temperature
equip ref: Bravo VAV 3-25
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:10.497-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:10.497-04:00

Bravo VAV 3-25 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 3-25 Zone Air Temp Setpoint
equip ref: Bravo VAV 3-25
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:10.995-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:10.995-04:00

Bravo VAV 3-25 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 3-25 Zone Temperature
equip ref: Bravo VAV 3-25
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:10.62-04:00

Bravo VAV 3-26
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-3
dis: Bravo VAV 3-26
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:152°F, designHotWaterPower:12.9MMBTU/h, designHotWaterFlow:1.5gal/min, designAirFlow:400cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 152
  design hot water power: 12.9
  design hot water flow: 1.5
  design air flow: 400

Bravo VAV 3-26 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 3-26 Damper Output
equip ref: Bravo VAV 3-26
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:09.752-04:00

Bravo VAV 3-26 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 3-26 Discharge Air Flow
equip ref: Bravo VAV 3-26
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:10.249-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:10.249-04:00

Bravo VAV 3-26 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 3-26 Discharge Air Flow Setpoint
equip ref: Bravo VAV 3-26
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:07.598-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:07.598-04:00

Bravo VAV 3-26 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 3-26 Heating Valve Output
equip ref: Bravo VAV 3-26
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:10.62-04:00

Bravo VAV 3-26 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 3-26 Supply Air Temperature
equip ref: Bravo VAV 3-26
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:09.752-04:00

Bravo VAV 3-26 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 3-26 Zone Air Temp Setpoint
equip ref: Bravo VAV 3-26
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:09.627-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:09.627-04:00

Bravo VAV 3-26 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 3-26 Zone Temperature
equip ref: Bravo VAV 3-26
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:09.879-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:09.879-04:00

Bravo VAV 3-27
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-3
dis: Bravo VAV 3-27
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:153°F, designHotWaterPower:6MMBTU/h, designHotWaterFlow:0.75gal/min, designAirFlow:300cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 153
  design hot water power: 6
  design hot water flow: 0.75
  design air flow: 300

Bravo VAV 3-27 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 3-27 Damper Output
equip ref: Bravo VAV 3-27
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:07.473-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:07.473-04:00

Bravo VAV 3-27 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 3-27 Discharge Air Flow
equip ref: Bravo VAV 3-27
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:10.745-04:00

Bravo VAV 3-27 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 3-27 Discharge Air Flow Setpoint
equip ref: Bravo VAV 3-27
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:11.125-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:11.125-04:00

Bravo VAV 3-27 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 3-27 Heating Valve Output
equip ref: Bravo VAV 3-27
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:10.995-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:10.995-04:00

Bravo VAV 3-27 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 3-27 Supply Air Temperature
equip ref: Bravo VAV 3-27
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:09.879-04:00 New_York, pointType:, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:09.879-04:00

Bravo VAV 3-27 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 3-27 Zone Air Temp Setpoint
equip ref: Bravo VAV 3-27
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:10.62-04:00

Bravo VAV 3-27 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 3-27 Zone Temperature
equip ref: Bravo VAV 3-27
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:10.62-04:00

Bravo VAV 3-28
type: thermostat
type: vav
has tag: equip
has tag: fanPowered
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: thermostat
has tag: vav
has tag: zone
air ref: Bravo RTU-3
dis: Bravo VAV 3-28
hot water ref: Bravo Boiler Plant
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:151°F, designHotWaterPower:3MMBTU/h, designHotWaterFlow:0.5gal/min, designAirFlow:200cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 151
  design hot water power: 3
  design hot water flow: 0.5
  design air flow: 200

Bravo VAV 3-28 Damper Output
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: discharge
has tag: his
has tag: point
dis: Bravo VAV 3-28 Damper Output
equip ref: Bravo VAV 3-28
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:09.879-04:00 New_York, inScope, backgroundPoint}
  source point name: DAMPER_CMD
  data sync recovered: 2020-07-10T01:00:09.879-04:00

Bravo VAV 3-28 Discharge Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 3-28 Discharge Air Flow
equip ref: Bravo VAV 3-28
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:09.879-04:00 New_York, inScope, backgroundPoint}
  source point name: BOX_FLOW
  data sync recovered: 2020-07-10T01:00:09.879-04:00

Bravo VAV 3-28 Discharge Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: effective
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 3-28 Discharge Air Flow Setpoint
equip ref: Bravo VAV 3-28
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:10.995-04:00 New_York, inScope, backgroundPoint}
  source point name: FLOW_STPT
  data sync recovered: 2020-07-10T01:00:10.995-04:00

Bravo VAV 3-28 Heating Valve Output
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: heat
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Bravo VAV 3-28 Heating Valve Output
equip ref: Bravo VAV 3-28
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: %
custom: {sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:11.125-04:00 New_York, inScope, backgroundPoint}
  source point name: Htg
  data sync recovered: 2020-07-10T01:00:11.125-04:00

Bravo VAV 3-28 Supply Air Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Bravo VAV 3-28 Supply Air Temperature
equip ref: Bravo VAV 3-28
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:09.627-04:00 New_York, inScope, backgroundPoint}
  source point name: DisAirTemp
  data sync recovered: 2020-07-10T01:00:09.627-04:00

Bravo VAV 3-28 Zone Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Bravo VAV 3-28 Zone Air Temp Setpoint
equip ref: Bravo VAV 3-28
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:09.627-04:00 New_York, inScope, backgroundPoint}
  source point name: STAT_SETPOINT
  data sync recovered: 2020-07-10T01:00:09.627-04:00

Bravo VAV 3-28 Zone Temperature
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Bravo VAV 3-28 Zone Temperature
equip ref: Bravo VAV 3-28
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: °F
custom: {sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:13.145-04:00 New_York, inScope, backgroundPoint}
  source point name: SPACE_TEMP
  data sync recovered: 2020-07-10T01:00:13.145-04:00

Bravo VAV 3-3
type: vav
has tag: equip
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: vav
air ref: Bravo RTU-3
dis: Bravo VAV 3-3
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:150°F, designHotWaterPower:4.2MMBTU/h, designHotWaterFlow:0.75gal/min, designAirFlow:375cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 150
  design hot water power: 4.2
  design hot water flow: 0.75
  design air flow: 375

Bravo VAV 3-3 Supply Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 3-3 Supply Air Flow
equip ref: Bravo VAV 3-3
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {dateCreated:2020-04-03, dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, backgroundPoint}
  date created: 2020-04-03
  data sync recovered: 2020-07-10T01:00:09.752-04:00

Bravo VAV 3-3 Supply Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 3-3 Supply Air Flow Setpoint
equip ref: Bravo VAV 3-3
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {dateCreated:2020-04-03, dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, backgroundPoint}
  date created: 2020-04-03
  data sync recovered: 2020-07-10T01:00:10.374-04:00

Bravo VAV 3-4
type: vav
has tag: equip
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: vav
air ref: Bravo RTU-3
dis: Bravo VAV 3-4
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:155°F, designHotWaterPower:1.7MMBTU/h, designHotWaterFlow:0.5gal/min, designAirFlow:150cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 155
  design hot water power: 1.7
  design hot water flow: 0.5
  design air flow: 150

Bravo VAV 3-4 Supply Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 3-4 Supply Air Flow
equip ref: Bravo VAV 3-4
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {dateCreated:2020-04-03, dataSyncRecovered:2020-07-10T01:00:10.87-04:00 New_York, backgroundPoint}
  date created: 2020-04-03
  data sync recovered: 2020-07-10T01:00:10.87-04:00

Bravo VAV 3-4 Supply Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 3-4 Supply Air Flow Setpoint
equip ref: Bravo VAV 3-4
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {dateCreated:2020-04-03, dataSyncRecovered:2020-07-10T01:00:07.721-04:00 New_York, backgroundPoint}
  date created: 2020-04-03
  data sync recovered: 2020-07-10T01:00:07.721-04:00

Bravo VAV 3-5
type: vav
has tag: equip
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: vav
air ref: Bravo RTU-3
dis: Bravo VAV 3-5
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:153°F, designHotWaterPower:3.3MMBTU/h, designHotWaterFlow:0.75gal/min, designAirFlow:300cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 153
  design hot water power: 3.3
  design hot water flow: 0.75
  design air flow: 300

Bravo VAV 3-5 Supply Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 3-5 Supply Air Flow
equip ref: Bravo VAV 3-5
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {dateCreated:2020-04-03, dataSyncRecovered:2020-07-10T01:00:11.125-04:00 New_York, backgroundPoint}
  date created: 2020-04-03
  data sync recovered: 2020-07-10T01:00:11.125-04:00

Bravo VAV 3-5 Supply Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 3-5 Supply Air Flow Setpoint
equip ref: Bravo VAV 3-5
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {dateCreated:2020-04-03, dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, backgroundPoint}
  date created: 2020-04-03
  data sync recovered: 2020-07-10T01:00:09.752-04:00

Bravo VAV 3-6
type: vav
has tag: equip
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: vav
air ref: Bravo RTU-3
dis: Bravo VAV 3-6
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:152°F, designHotWaterPower:6.5MMBTU/h, designHotWaterFlow:1.25gal/min, designAirFlow:600cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 152
  design hot water power: 6.5
  design hot water flow: 1.25
  design air flow: 600

Bravo VAV 3-6 Supply Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 3-6 Supply Air Flow
equip ref: Bravo VAV 3-6
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {dateCreated:2020-04-03, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, backgroundPoint}
  date created: 2020-04-03
  data sync recovered: 2020-07-10T01:00:10.003-04:00

Bravo VAV 3-6 Supply Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 3-6 Supply Air Flow Setpoint
equip ref: Bravo VAV 3-6
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {dateCreated:2020-04-03, dataSyncRecovered:2020-07-10T01:00:07.598-04:00 New_York, backgroundPoint}
  date created: 2020-04-03
  data sync recovered: 2020-07-10T01:00:07.598-04:00

Bravo VAV 3-7
type: vav
has tag: equip
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: vav
air ref: Bravo RTU-3
dis: Bravo VAV 3-7
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:150°F, designHotWaterPower:7.6MMBTU/h, designHotWaterFlow:1.25gal/min, designAirFlow:700cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 150
  design hot water power: 7.6
  design hot water flow: 1.25
  design air flow: 700

Bravo VAV 3-7 Supply Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 3-7 Supply Air Flow
equip ref: Bravo VAV 3-7
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {dateCreated:2020-04-03, dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, backgroundPoint}
  date created: 2020-04-03
  data sync recovered: 2020-07-10T01:00:10.374-04:00

Bravo VAV 3-7 Supply Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 3-7 Supply Air Flow Setpoint
equip ref: Bravo VAV 3-7
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {dateCreated:2020-04-03, dataSyncRecovered:2020-07-10T01:00:10.249-04:00 New_York, backgroundPoint}
  date created: 2020-04-03
  data sync recovered: 2020-07-10T01:00:10.249-04:00

Bravo VAV 3-8
type: vav
has tag: equip
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: vav
air ref: Bravo RTU-3
dis: Bravo VAV 3-8
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:153°F, designHotWaterPower:6.5MMBTU/h, designHotWaterFlow:0.75gal/min, designAirFlow:300cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 153
  design hot water power: 6.5
  design hot water flow: 0.75
  design air flow: 300

Bravo VAV 3-8 Supply Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 3-8 Supply Air Flow
equip ref: Bravo VAV 3-8
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {dateCreated:2020-04-03, dataSyncRecovered:2020-07-10T01:00:07.598-04:00 New_York, backgroundPoint}
  date created: 2020-04-03
  data sync recovered: 2020-07-10T01:00:07.598-04:00

Bravo VAV 3-8 Supply Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 3-8 Supply Air Flow Setpoint
equip ref: Bravo VAV 3-8
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {dateCreated:2020-04-03, dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, backgroundPoint}
  date created: 2020-04-03
  data sync recovered: 2020-07-10T01:00:10.374-04:00

Bravo VAV 3-9
type: vav
has tag: equip
has tag: hotWaterHeating
has tag: hvac
has tag: singleDuct
has tag: vav
air ref: Bravo RTU-3
dis: Bravo VAV 3-9
site ref: Bravo
space ref: Bravo VAVs
custom: {tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:151°F, designHotWaterPower:23MMBTU/h, designHotWaterFlow:4gal/min, designAirFlow:2000cfm}
  design source: Drawings
  design hot water entering temp: 180
  design hot water leaving temp: 151
  design hot water power: 23
  design hot water flow: 4
  design air flow: 2000

Bravo VAV 3-9 Supply Air Flow
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Bravo VAV 3-9 Supply Air Flow
equip ref: Bravo VAV 3-9
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {dateCreated:2020-04-03, dataSyncRecovered:2020-07-10T01:00:09.879-04:00 New_York, backgroundPoint}
  date created: 2020-04-03
  data sync recovered: 2020-07-10T01:00:09.879-04:00

Bravo VAV 3-9 Supply Air Flow Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sp
dis: Bravo VAV 3-9 Supply Air Flow Setpoint
equip ref: Bravo VAV 3-9
kind: Number
site ref: Bravo
space ref: Bravo VAVs
tz: Chicago
unit: cfm
custom: {dateCreated:2020-04-03, dataSyncRecovered:2020-07-10T01:00:10.126-04:00 New_York, backgroundPoint}
  date created: 2020-04-03
  data sync recovered: 2020-07-10T01:00:10.126-04:00

Bravo VAVs
type: space
has tag: space
dis: Bravo VAVs
site ref: Bravo
custom: {equipType}

Fort Wayne, IN
type: weatherStation
has tag: weatherStation
dis: Fort Wayne, IN
geo city: Fort Wayne
geo coord: C(41.131,-85.129)
geo country: US
geo state: IN
tz: Indianapolis

Fort Wayne, IN Condition
type: his-point
type: weather-point
has tag: his
has tag: point
has tag: sensor
has tag: weather
has tag: weatherCond
dis: Fort Wayne, IN Condition
enum: unknown,clear,partlyCloudy,cloudy,showers,rain,thunderstorms,ice,flurries,snow
kind: Str
tz: Indianapolis
weather station ref: Fort Wayne, IN

Fort Wayne, IN Humidity
type: his-point
type: weather-point
has tag: air
has tag: his
has tag: humidity
has tag: point
has tag: sensor
has tag: weather
dis: Fort Wayne, IN Humidity
kind: Number
tz: Indianapolis
unit: %RH
weather station ref: Fort Wayne, IN

Fort Wayne, IN Sunrise
type: his-point
type: weather-point
has tag: daytime
has tag: his
has tag: point
has tag: sensor
has tag: weather
dis: Fort Wayne, IN Sunrise
kind: Bool
tz: Indianapolis
weather station ref: Fort Wayne, IN

Fort Wayne, IN Temp
type: his-point
type: weather-point
has tag: air
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: weather
dis: Fort Wayne, IN Temp
kind: Number
tz: Indianapolis
unit: °F
weather station ref: Fort Wayne, IN

Points Not Syncing
type: his-point
has tag: his
has tag: point
has tag: sensor
dis: Points Not Syncing
kind: Number
site ref: Bravo
tz: Chicago
custom: {diagnostics, dataSync, dataSyncRecovered:2020-07-14T01:00:05.167-04:00 New_York, backgroundPoint}
  data sync recovered: 2020-07-14T01:00:05.167-04:00