{predictionConf:0.31259757180034364, sourcePointName:ChwVlvOR_value, dataSyncRecovered:2020-07-10T01:00:10.249-04:00 New_York, inScope, backgroundPoint}
{predictionConf:0.28394372966813813, sourcePointName:MadOR_value, dataSyncRecovered:2020-07-10T01:00:09.879-04:00 New_York, inScope, backgroundPoint}
{predictionConf:0.7893816782198223, sourcePointName:DAT, dataSyncRecovered:2020-07-10T01:00:09.879-04:00 New_York, inScope, backgroundPoint}
{predictionConf:0.6720981954640639, sourcePointName:SpaceTemp, dataSyncRecovered:2020-07-10T01:00:09.627-04:00 New_York, inScope, backgroundPoint}
{precision:2, dataSyncRecovered:2020-07-10T01:00:11.125-04:00 New_York, backgroundPoint}
{sourcePointName:ChwVlvOR_value, dataSyncRecovered:2020-07-10T01:00:10.87-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:MadOR_value, dataSyncRecovered:2020-07-10T01:00:07.721-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:DAT, dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:SpaceTemp, dataSyncRecovered:2020-07-10T01:00:07.598-04:00 New_York, inScope, backgroundPoint}
{precision:2, dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, backgroundPoint}
{designSource:Drawings, designHotWaterPower:4200MMBTU/h, designMake:Bryan Boiler, designModel:RV-500W}
{sourcePointName:HwBlr1Sts, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:HwBlr2Sts, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, inScope, backgroundPoint}
Bravo Boiler Plant Domestic Hot Water Leaving Temperature Setpoint
{sourcePointName:HwSp, dataSyncRecovered:2020-07-10T01:00:10.87-04:00 New_York, inScope, backgroundPoint}
Bravo Boiler Plant Heating Hot Water Differential Pressure Setpoint
{sourcePointName:HWDifSP, dataSyncRecovered:2020-07-10T01:00:10.497-04:00 New_York, inScope, backgroundPoint}
Bravo Boiler Plant Heating Hot Water Return Temperature
{sourcePointName:HWRTEMP, dataSyncRecovered:2020-07-10T01:00:13.145-04:00 New_York, inScope, backgroundPoint}
Bravo Boiler Plant Heating Hot Water Supply Temperature
{sourcePointName:HWSTEMP, dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, inScope, backgroundPoint}
{poinTags:point and chilled and water and cmd and pump, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, backgroundPoint}
point and chilled and water and cmd and pump
Bravo CHWP-1 Chilled Water Pump VFD Speed
{dataSyncDownSince:2020-07-14T01:00:03.512-04:00 New_York, precision:2, dataSyncType:error, backgroundPoint}
{dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, backgroundPoint}
Bravo CHWP-2 Chilled Water Pump VFD Speed
{precision:2, dataSyncRecovered:2020-07-10T01:00:07.598-04:00 New_York, backgroundPoint}
Bravo Chilled Water Plant AHU Cooling Enable
{sourcePointName:AHUClgEnable, dataSyncRecovered:2020-07-10T01:00:11.125-04:00 New_York, backgroundPoint}
Bravo Chilled Water Plant AHU Heating Enable
{sourcePointName:AHUHtgEnable, dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, backgroundPoint}
Bravo Chilled Water Plant CV-1 Valve Signal (HHW)
{precision:2, dataSyncRecovered:2020-07-10T01:00:10.995-04:00 New_York, backgroundPoint}
Bravo Chilled Water Plant CV-2 Valve Signal (Bypass Valve)
{precision:2, dataSyncRecovered:2020-07-10T01:00:10.126-04:00 New_York, signal, backgroundPoint}
Bravo Chilled Water Plant CV-3 Valve Signal
{precision:0, dataSyncRecovered:2020-07-10T01:00:07.473-04:00 New_York, signal, backgroundPoint}
Bravo Chilled Water Plant CV-4 Valve Signal
{precision:0, dataSyncRecovered:2020-07-10T01:00:10.126-04:00 New_York, signal, backgroundPoint}
Bravo Chilled Water Plant Chilled Water Differential Pressure
{precision:2, dataSyncRecovered:2020-07-10T01:00:10.249-04:00 New_York, pointType:, backgroundPoint}
Bravo Chilled Water Plant Chilled Water Differential Pressure Setpoint
{predictionConf:0.3397244142906628, sourcePointName:ChwDifSP, dataSyncRecovered:2020-07-10T01:00:09.627-04:00 New_York, inScope, backgroundPoint}
Bravo Chilled Water Plant Chilled Water Entering Temperature
{predictionConf:0.787900067809321, sourcePointName:CHWRTEMP, dataSyncRecovered:2020-07-10T01:00:10.497-04:00 New_York, inScope, backgroundPoint}
Bravo Chilled Water Plant Chilled Water Leaving Temperature
{predictionConf:0.787900067809321, sourcePointName:ChwsTemp, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
Bravo Chilled Water Plant Chilled Water dT (Auto-computed)
{cache, dataSyncDownSince:2020-03-12T01:00:04.793-04:00 New_York, dataSyncType:error, backgroundPoint}
Bravo Chilled Water Plant Chiller Status
{predictionConf:0.15013386549340826, sourcePointName:RunSTATUS, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
Bravo Chilled Water Plant Efficiency (Auto-computed)
{cache, dataSyncRecovered:2020-07-14T01:00:05.167-04:00 New_York, backgroundPoint}
{designElecPower:180kW, designEfficiency:10.6EER, designSource:Drawings, designChilledWaterPower:160tonref, designChilledWaterLeavingTemp:44°F, designMake:Mcquay, designChilledWaterEnteringTemp:58°F, designChilledWaterDeltaPressure:18.61psi, designModel:AGS-160C, designChilledWaterFlow:275gal/min}
Bravo Chiller 1 Chilled Water Entering Temperature
{predictionConf:0.38428817764444545, sourcePointName:CH1_EntChwTemp, dataSyncRecovered:2020-07-10T01:00:10.87-04:00 New_York, inScope, backgroundPoint}
Bravo Chiller 1 Chilled Water Leaving Temperature
{predictionConf:0.34916172794461753, sourcePointName:CH1_LeavChwTemp, dataSyncRecovered:2020-07-10T01:00:09.879-04:00 New_York, inScope, backgroundPoint}
Bravo Chiller 1 Chilled Water dT (Auto-computed)
{predictionConf:0.42372423437084655, sourcePointName:CH1_CHW_SP, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, pointType:, inScope, backgroundPoint}
{act, precision:2, dataSyncRecovered:2020-07-10T01:00:10.995-04:00 New_York, backgroundPoint, capacity}
{predictionConf:0.2769995097894551, sourcePointName:CH1_Clr1Cmd, dataSyncRecovered:2020-07-10T01:00:10.87-04:00 New_York, inScope, backgroundPoint}
{predictionConf:0.33026119584467384, sourcePointName:CH1_ChlrSts, dataSyncRecovered:2020-07-10T01:00:10.995-04:00 New_York, inScope, backgroundPoint}
Bravo Chiller 2 Chilled Water Entering Temperature
{predictionConf:0.38428817764444545, sourcePointName:CH2_EntChwTemp, dataSyncRecovered:2020-07-10T01:00:10.497-04:00 New_York, inScope, backgroundPoint}
Bravo Chiller 2 Chilled Water Leaving Temperature
{predictionConf:0.34916172794461753, sourcePointName:CH2_LeavChwTemp, dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, inScope, backgroundPoint}
Bravo Chiller 2 Chilled Water dT (Auto-computed)
{predictionConf:0.42372423437084655, sourcePointName:CH2_CHW_SP, dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, pointType:, inScope, backgroundPoint}
{act, precision:2, dataSyncRecovered:2020-07-10T01:00:09.627-04:00 New_York, backgroundPoint, capacity}
{predictionConf:0.2769995097894551, sourcePointName:CH2_Clr1Cmd, dataSyncRecovered:2020-07-10T01:00:11.258-04:00 New_York, inScope, backgroundPoint}
{predictionConf:0.33026119584467384, sourcePointName:CH2_ChlrSts, dataSyncRecovered:2020-07-14T01:00:05.167-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:EFSS, dataSyncRecovered:2020-07-10T01:00:10.995-04:00 New_York, inScope, backgroundPoint}
{dataSyncDownSince:2020-03-11T13:56:25.929-04:00 New_York, sourcePointName:EFStatus, dataSyncType:error, pointType:, inScope, backgroundPoint}
{sourcePointName:EFSS, dataSyncRecovered:2020-07-10T01:00:13.145-04:00 New_York, inScope, backgroundPoint}
{dataSyncDownSince:2020-06-23T01:00:04.326-04:00 New_York, sourcePointName:EFStatus, dataSyncType:error, inScope, backgroundPoint}
{sourcePointName:EFSS, dataSyncRecovered:2020-07-10T01:00:11.258-04:00 New_York, inScope, backgroundPoint}
{dataSyncDownSince:2020-03-11T13:56:25.945-04:00 New_York, sourcePointName:EFStatus, dataSyncType:error, inScope, backgroundPoint}
{sourcePointName:EFSS, dataSyncRecovered:2020-07-10T01:00:07.473-04:00 New_York, inScope, backgroundPoint}
{dataSyncDownSince:2020-03-11T13:56:25.929-04:00 New_York, sourcePointName:EFStatus, dataSyncType:error, inScope, backgroundPoint}
{sourcePointName:EFSS, dataSyncRecovered:2020-07-10T01:00:10.497-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:EFSS, dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:EFSS, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:EFSS, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
{dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, backgroundPoint}
{dataSyncRecovered:2020-07-10T01:00:10.497-04:00 New_York, backgroundPoint}
{dataSyncRecovered:2020-07-10T01:00:13.145-04:00 New_York, backgroundPoint}
{dataSyncRecovered:2020-07-10T01:00:07.598-04:00 New_York, backgroundPoint}
{sourcePointName:EFSS, dataSyncRecovered:2020-07-10T01:00:09.627-04:00 New_York, inScope, backgroundPoint}
{dataSyncRecovered:2020-07-10T01:00:07.473-04:00 New_York, backgroundPoint}
{dataSyncRecovered:2020-07-10T01:00:11.258-04:00 New_York, backgroundPoint}
{dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, backgroundPoint}
{sourcePointName:EF23SS, dataSyncRecovered:2020-07-10T01:00:13.145-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:EF23Status, dataSyncRecovered:2020-07-10T01:00:09.879-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:EFSS, dataSyncRecovered:2020-07-10T01:00:09.879-04:00 New_York, inScope, backgroundPoint}
{dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, backgroundPoint}
{sourcePointName:EFSS, dataSyncRecovered:2020-07-10T01:00:10.126-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:EFStatus, dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:EFStatus, dataSyncRecovered:2020-07-10T01:00:07.473-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:EF28Status, dataSyncRecovered:2020-07-10T01:00:07.598-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:EFStatus, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:EFSS, dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:EFSS, dataSyncRecovered:2020-07-10T01:00:10.87-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:EFSS, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, inScope, backgroundPoint}
{dataSyncDownSince:2020-05-28T01:00:09.102-04:00 New_York, sourcePointName:EFStatus, dataSyncType:error, inScope, backgroundPoint}
{sourcePointName:EFSS, dataSyncRecovered:2020-07-10T01:00:07.598-04:00 New_York, inScope, backgroundPoint}
{dataSyncDownSince:2020-07-02T01:00:04.305-04:00 New_York, sourcePointName:EFStatus, dataSyncType:error, pointType:, inScope, backgroundPoint}
{sourcePointName:ChwVlv, dataSyncRecovered:2020-07-10T01:00:13.145-04:00 New_York, inScope, backgroundPoint}
{precision:0, dataSyncRecovered:2020-07-10T01:00:09.627-04:00 New_York, backgroundPoint}
{sourcePointName:SpcTemp, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
{precision:2, dataSyncRecovered:2020-07-10T01:00:10.87-04:00 New_York, backgroundPoint}
{sourcePointName:ChwVlv, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
{precision:0, dataSyncRecovered:2020-07-10T01:00:11.258-04:00 New_York, backgroundPoint}
{sourcePointName:SpcTemp, dataSyncRecovered:2020-07-10T01:00:10.995-04:00 New_York, inScope, backgroundPoint}
{precision:2, dataSyncRecovered:2020-07-10T01:00:10.126-04:00 New_York, backgroundPoint}
{sourcePointName:ChwVlv, dataSyncRecovered:2020-07-10T01:00:09.627-04:00 New_York, inScope, backgroundPoint}
{precision:0, dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, backgroundPoint}
{sourcePointName:SpcTemp, dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:ChwVlv, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, inScope, backgroundPoint}
{precision:0, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, backgroundPoint}
{precision:2, dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, backgroundPoint}
{dataSyncRecovered:2020-07-10T01:00:10.995-04:00 New_York, backgroundPoint, status}
{precision:2, dataSyncRecovered:2020-07-10T01:00:10.497-04:00 New_York, backgroundPoint}
{dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, backgroundPoint, status}
{precision:2, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, backgroundPoint}
{designDischargeAirFlow:15300cfm, steamHumidifier, designHotWaterLeavingTemp:65°F, designHotWaterPower:145MMBTU/h, designOutsideAirFlowMin:3500cfm, designDischargeFanAirDeltaPressure:7.04inH₂O, designSource:Drawings, designChilledWaterLeavingTemp:59°F, designChilledWaterPower:722.3MMBTU/h, designHotWaterFlow:24.1gal/min, designChilledWaterFlow:96.4gal/min, designReturnAirFlow:15300cfm, designHotWaterEnteringTemp:75°F, designOutsideAirFlow:15300cfm, designReturnFanPower:15hp, designChilledWaterEnteringTemp:44°F, designDischargeFanPower:40hp, designReturnFanAirDeltaPressure:1.66inH₂O}
{mode, dataSyncRecovered:2020-07-14T01:00:05.167-04:00 New_York, backgroundPoint}
{sourcePointName:CWV, dataSyncRecovered:2020-07-10T01:00:10.126-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:EAD, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
{cache, dataSyncDownSince:2020-04-09T01:00:02.664-04:00 New_York, dataSyncType:error, backgroundPoint}
Bravo RTU-1 Heating/Cooling Load (Auto-computed)
{sourcePointName:HUM_ENABLE, dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:HUM VLV, dataSyncRecovered:2020-07-10T01:00:10.87-04:00 New_York, inScope, backgroundPoint}
{max, dataSyncRecovered:2020-07-14T01:00:05.167-04:00 New_York, backgroundPoint}
Bravo RTU-1 Min Outdoor Air Flow Setpoint
{min, sourcePointName:MinOA_SP, dataSyncRecovered:2020-07-10T01:00:10.249-04:00 New_York, pointType:, inScope, backgroundPoint}
{min, sourcePointName:MIN OA CFM / 10, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
Bravo RTU-1 Minimum Outside Air Damper Output
{sourcePointName:Min OAD, dataSyncRecovered:2020-07-10T01:00:07.598-04:00 New_York, inScope, outsideMin, backgroundPoint}
{sourcePointName:MAT, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
Bravo RTU-1 Mixed Air Temperature Setpoint
{sourcePointName:MAT STPT, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:OAD, dataSyncRecovered:2020-07-10T01:00:10.249-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:OA CFM, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
Bravo RTU-1 Outside Air Percentage (Auto-computed)
{cache, dataSyncDownSince:2020-04-09T01:00:02.656-04:00 New_York, dataSyncType:error, backgroundPoint}
{dataSyncRecovered:2020-07-14T01:00:05.167-04:00 New_York, backgroundPoint}
{sourcePointName:RET/REL DAMPER, dataSyncRecovered:2020-07-10T01:00:11.125-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:RA CFM, dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:RAH, dataSyncRecovered:2020-07-10T01:00:09.627-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:RAT, dataSyncRecovered:2020-07-10T01:00:11.258-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:RF FAN STATUS, dataSyncRecovered:2020-07-10T01:00:10.995-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:ACT_OUTPUT_SPEED, dataSyncRecovered:2020-07-10T01:00:07.721-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:SA CFM, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:DAH, dataSyncRecovered:2020-07-10T01:00:09.879-04:00 New_York, inScope, backgroundPoint}
Bravo RTU-1 Supply Air Humidity Setpoint
{sourcePointName:Humidity SP, dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, inScope, backgroundPoint}
Bravo RTU-1 Supply Air Pressure Setpoint
{static, sourcePointName:Static Stpt, dataSyncRecovered:2020-07-10T01:00:13.145-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:DISCH STATIC, dataSyncRecovered:2020-07-10T01:00:09.879-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:DAT, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
Bravo RTU-1 Supply Air Temperature Setpoint
{sourcePointName:DAT STPT, dataSyncRecovered:2020-07-10T01:00:11.258-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:SF FAN STATUS, dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, inScope, backgroundPoint}
{designDischargeAirFlow:30000cfm, steamHumidifier, designHotWaterLeavingTemp:65°F, designHotWaterPower:288MMBTU/h, designOutsideAirFlowMin:6750cfm, designDischargeFanAirDeltaPressure:6.4inH₂O, designSource:Drawings, designChilledWaterLeavingTemp:59.2°F, designChilledWaterPower:1225.8MMBTU/h, designHotWaterFlow:48gal/min, designChilledWaterFlow:160.9gal/min, designReturnAirFlow:30000cfm, designHotWaterEnteringTemp:75°F, designOutsideAirFlow:30000cfm, designReturnFanPower:25hp, designChilledWaterEnteringTemp:44°F, designDischargeFanPower:50hp, designReturnFanAirDeltaPressure:1.62inH₂O}
Bravo RTU-2 Calculated Outdoor Air Flow Setpoint
{predictionConf:0.3970116854281743, sourcePointName:MinOA_SP, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
{predictionConf:0.5846394026860828, sourcePointName:CWV, dataSyncRecovered:2020-07-10T01:00:10.995-04:00 New_York, inScope, backgroundPoint}
{predictionConf:0.6232903565384572, sourcePointName:EAD, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
Bravo RTU-2 Heating/Cooling Load (Auto-computed)
{predictionConf:0.2169429859073283, sourcePointName:HUM_ENABLE, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
{predictionConf:0.7439557600414519, sourcePointName:HUM VLV, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
{predictionConf:0.2305698711556413, sourcePointName:MINOASTPT, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, inScope, outsideMin, backgroundPoint}
{predictionConf:0.5591032698291575, min, sourcePointName:MIN OA CFM / 10, dataSyncRecovered:2020-07-10T01:00:10.126-04:00 New_York, inScope, backgroundPoint}
Bravo RTU-2 Minimum Outside Air Damper Output
{predictionConf:0.7226466689139898, sourcePointName:Min OAD, dataSyncRecovered:2020-07-10T01:00:10.497-04:00 New_York, inScope, outsideMin, backgroundPoint}
{predictionConf:0.5092275130999935, sourcePointName:MAT, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
Bravo RTU-2 Mixed Air Temperature Setpoint
{predictionConf:0.41409123546331406, sourcePointName:MAT STPT, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
{predictionConf:0.7395401248861597, sourcePointName:OAD, dataSyncRecovered:2020-07-10T01:00:10.249-04:00 New_York, inScope, backgroundPoint}
{predictionConf:0.7870789837941534, sourcePointName:OA CFM, dataSyncRecovered:2020-07-10T01:00:11.125-04:00 New_York, inScope, backgroundPoint}
Bravo RTU-2 Outside Air Percentage (Auto-computed)
{predictionConf:0.3561100767369028, sourcePointName:RET/REL DAMPER, dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, inScope, backgroundPoint}
{predictionConf:0.8263008623409421, sourcePointName:RA CFM, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
{predictionConf:0.7016271134196499, sourcePointName:RAH, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
{predictionConf:0.5745623242771728, sourcePointName:RAT, dataSyncRecovered:2020-07-10T01:00:10.497-04:00 New_York, inScope, backgroundPoint}
{predictionConf:0.5721715629985896, sourcePointName:RF FAN STATUS, dataSyncRecovered:2020-07-10T01:00:10.497-04:00 New_York, inScope, backgroundPoint}
{predictionConf:0.13813130060214382, sourcePointName:ACT_OUTPUT_SPEED, dataSyncRecovered:2020-07-10T01:00:07.721-04:00 New_York, inScope, backgroundPoint}
{predictionConf:0.7841375570046363, sourcePointName:SA CFM, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
{predictionConf:0.7933659564917551, sourcePointName:DAH, dataSyncRecovered:2020-07-10T01:00:10.995-04:00 New_York, inScope, backgroundPoint}
Bravo RTU-2 Supply Air Humidity Setpoint
{predictionConf:0.7045004074770955, sourcePointName:Humidity SP, dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, inScope, backgroundPoint}
{predictionConf:0.3539915786588711, sourcePointName:DISCH STATIC, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, inScope, backgroundPoint}
Bravo RTU-2 Supply Air Static Pressure Setpoint
{predictionConf:0.48636472322277824, sourcePointName:Static Stpt, dataSyncRecovered:2020-07-10T01:00:13.145-04:00 New_York, inScope, backgroundPoint}
{predictionConf:0.5598774100147106, sourcePointName:DAT, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
Bravo RTU-2 Supply Air Temperature Setpoint
{predictionConf:0.6936845307741977, sourcePointName:DAT STPT, dataSyncRecovered:2020-07-10T01:00:09.879-04:00 New_York, inScope, backgroundPoint}
{predictionConf:0.6818756457191736, sourcePointName:SF FAN STATUS, dataSyncRecovered:2020-07-10T01:00:11.258-04:00 New_York, inScope, backgroundPoint}
{predictionConf:0.13813130060214382, sourcePointName:ACT_OUTPUT_SPEED, dataSyncRecovered:2020-07-10T01:00:10.87-04:00 New_York, inScope, backgroundPoint}
{designDischargeAirFlow:33600cfm, steamHumidifier, designHotWaterLeavingTemp:65°F, designHotWaterPower:318MMBTU/h, designOutsideAirFlowMin:7125cfm, designDischargeFanAirDeltaPressure:6.7inH₂O, designSource:Drawings, designChilledWaterLeavingTemp:58.9°F, designChilledWaterPower:1346.1MMBTU/h, designHotWaterFlow:53gal/min, designChilledWaterFlow:180.2gal/min, designReturnAirFlow:33600cfm, designHotWaterEnteringTemp:75°F, designOutsideAirFlow:33600cfm, designReturnFanPower:25hp, designChilledWaterEnteringTemp:44°F, designDischargeFanPower:60hp, designReturnFanAirDeltaPressure:1.63inH₂O}
{predictionConf:0.5846394026860828, sourcePointName:CWV, dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, inScope, backgroundPoint}
{predictionConf:0.6232903565384572, sourcePointName:EAD, dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, inScope, backgroundPoint}
Bravo RTU-3 Heating/Cooling Load (Auto-computed)
{predictionConf:0.2169429859073283, sourcePointName:HUM_ENABLE, dataSyncRecovered:2020-07-10T01:00:07.598-04:00 New_York, inScope, backgroundPoint}
{predictionConf:0.7439557600414519, sourcePointName:HUM VLV, dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, inScope, backgroundPoint}
{predictionConf:0.2305698711556413, sourcePointName:MINOASTPT, dataSyncRecovered:2020-07-10T01:00:10.126-04:00 New_York, inScope, outsideMin, backgroundPoint}
Bravo RTU-3 Minimum Outside Air Damper Output
{predictionConf:0.7226466689139898, sourcePointName:Min OAD, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, outsideMin, backgroundPoint}
Bravo RTU-3 Mixed Air Temperature Setpoint
{predictionConf:0.41409123546331406, sourcePointName:MAT STPT, dataSyncRecovered:2020-07-10T01:00:11.125-04:00 New_York, inScope, backgroundPoint}
{predictionConf:0.7395401248861597, sourcePointName:OAD, dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, inScope, backgroundPoint}
{predictionConf:0.7870789837941534, sourcePointName:OA CFM, dataSyncRecovered:2020-07-10T01:00:07.473-04:00 New_York, inScope, backgroundPoint}
Bravo RTU-3 Outside Air Percentage (Auto-computed)
{predictionConf:0.3561100767369028, sourcePointName:RET/REL DAMPER, dataSyncRecovered:2020-07-10T01:00:09.879-04:00 New_York, inScope, backgroundPoint}
{predictionConf:0.8263008623409421, sourcePointName:RA CFM, dataSyncRecovered:2020-07-10T01:00:13.145-04:00 New_York, inScope, backgroundPoint}
{predictionConf:0.7016271134196499, sourcePointName:RAH, dataSyncRecovered:2020-07-10T01:00:09.879-04:00 New_York, inScope, backgroundPoint}
{predictionConf:0.5745623242771728, sourcePointName:RAT, dataSyncRecovered:2020-07-10T01:00:10.126-04:00 New_York, inScope, backgroundPoint}
{predictionConf:0.3324288739189246, sourcePointName:RTDrvSpd, dataSyncRecovered:2020-07-10T01:00:07.721-04:00 New_York, inScope, backgroundPoint}
{predictionConf:0.7841375570046363, sourcePointName:SA CFM, dataSyncRecovered:2020-07-10T01:00:07.473-04:00 New_York, inScope, backgroundPoint}
{predictionConf:0.7933659564917551, sourcePointName:DAH, dataSyncRecovered:2020-07-10T01:00:07.598-04:00 New_York, inScope, backgroundPoint}
Bravo RTU-3 Supply Air Pressure Setpoint
{predictionConf:0.48636472322277824, static, sourcePointName:Static Stpt, dataSyncRecovered:2020-07-10T01:00:13.145-04:00 New_York, inScope, backgroundPoint}
{predictionConf:0.3539915786588711, sourcePointName:DISCH STATIC, dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, inScope, backgroundPoint}
{predictionConf:0.5598774100147106, sourcePointName:DAT, dataSyncRecovered:2020-07-10T01:00:10.87-04:00 New_York, inScope, backgroundPoint}
Bravo RTU-3 Supply Air Temperature Setpoint
{predictionConf:0.6936845307741977, sourcePointName:DAT STPT, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, inScope, backgroundPoint}
{predictionConf:0.6818756457191736, sourcePointName:SF FAN STATUS, dataSyncRecovered:2020-07-10T01:00:10.995-04:00 New_York, inScope, backgroundPoint}
{predictionConf:0.32036669663302475, sourcePointName:SPDrvSpd, dataSyncRecovered:2020-07-10T01:00:09.879-04:00 New_York, inScope, backgroundPoint}
{designDischargeAirFlow:15700cfm, steamHumidifier, designHotWaterLeavingTemp:65°F, designHotWaterPower:243MMBTU/h, designOutsideAirFlowMin:7125cfm, designDischargeFanAirDeltaPressure:4.76inH₂O, designSource:Drawings, designChilledWaterLeavingTemp:58.9°F, designChilledWaterPower:1028.7MMBTU/h, designHotWaterFlow:41gal/min, designChilledWaterFlow:137.8gal/min, designReturnAirFlow:25700cfm, designHotWaterEnteringTemp:75°F, designOutsideAirFlow:25700cfm, designReturnFanPower:20hp, designChilledWaterEnteringTemp:44°F, designDischargeFanPower:40hp, designReturnFanAirDeltaPressure:1.64inH₂O}
{sourcePointName:CWV, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, inScope, backgroundPoint}
Bravo RTU-4 Heating/Cooling Load (Auto-computed)
{sourcePointName:HUM VLV, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, inScope, backgroundPoint}
Bravo RTU-4 Min Outdoor Air Flow Setpoint
{min, sourcePointName:MinOA_SP, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, pointType:, inScope, backgroundPoint}
{min, sourcePointName:MIN OA CFM / 10, dataSyncRecovered:2020-07-10T01:00:10.87-04:00 New_York, inScope, backgroundPoint}
Bravo RTU-4 Minimum Outside Air Damper Output
{sourcePointName:Min OAD, dataSyncRecovered:2020-07-10T01:00:09.879-04:00 New_York, inScope, outsideMin, backgroundPoint}
{sourcePointName:MAT, dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, inScope, backgroundPoint}
Bravo RTU-4 Mixed Air Temperature Setpoint
{sourcePointName:MAT STPT, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:OAD, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:OA CFM, dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, inScope, backgroundPoint}
Bravo RTU-4 Outside Air Percentage (Auto-computed)
{sourcePointName:RET/REL DAMPER, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, pointType:, inScope, backgroundPoint}
{sourcePointName:RA CFM, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:RAH, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:RAT, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:RF FAN STATUS, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:ACT_OUTPUT_SPEED, dataSyncRecovered:2020-07-10T01:00:10.126-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:SA CFM, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:DAH, dataSyncRecovered:2020-07-10T01:00:07.598-04:00 New_York, inScope, backgroundPoint}
Bravo RTU-4 Supply Air Humidity Setpoint
{sourcePointName:Humidity SP, dataSyncRecovered:2020-07-10T01:00:13.145-04:00 New_York, inScope, backgroundPoint}
Bravo RTU-4 Supply Air Pressure Setpoint
{static, sourcePointName:Static Stpt, dataSyncRecovered:2020-07-10T01:00:07.598-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:DISCH STATIC, dataSyncRecovered:2020-07-10T01:00:07.473-04:00 New_York, inScope, backgroundPoint}
Bravo RTU-4 Supply Air Temperature Setpoint
{sourcePointName:DAT STPT, dataSyncRecovered:2020-07-10T01:00:11.125-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:SF FAN STATUS, dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, inScope, backgroundPoint}
{designSource:Drawings, designMake:Lattner, designSteamPower:1350MMBTU/h, designModel:WLF-40}
{sourcePointName:StmBlrAsts, dataSyncRecovered:2020-07-10T01:00:10.126-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:StmBlrBsts, dataSyncRecovered:2020-07-10T01:00:09.627-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:StmBlrCsts, dataSyncRecovered:2020-07-10T01:00:10.995-04:00 New_York, inScope, backgroundPoint}
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:152°F, designHotWaterPower:9.7MMBTU/h, designHotWaterFlow:1gal/min, designAirFlow:400cfm}
{sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:07.598-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, inScope, backgroundPoint}
Bravo VAV 1-1 Discharge Air Flow Setpoint
{sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:07.473-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:11.125-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:11.258-04:00 New_York, inScope, backgroundPoint}
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:149°F, designHotWaterPower:6.5MMBTU/h, designHotWaterFlow:0.75gal/min, designAirFlow:375cfm}
{sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:11.125-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:13.145-04:00 New_York, inScope, backgroundPoint}
Bravo VAV 1-10 Discharge Air Flow Setpoint
{sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:07.598-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:11.125-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:10.87-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:11.258-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:10.126-04:00 New_York, inScope, backgroundPoint}
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:152°F, designHotWaterPower:10.2MMBTU/h, designHotWaterFlow:1gal/min, designAirFlow:300cfm}
{sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:13.145-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:10.87-04:00 New_York, inScope, backgroundPoint}
Bravo VAV 1-11 Discharge Air Flow Setpoint
{sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:10.249-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:10.126-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:13.145-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:10.497-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:07.473-04:00 New_York, inScope, backgroundPoint}
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:152°F, designHotWaterPower:10.2MMBTU/h, designHotWaterFlow:1gal/min, designAirFlow:500cfm}
{sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:11.258-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:10.126-04:00 New_York, inScope, backgroundPoint}
Bravo VAV 1-12 Discharge Air Flow Setpoint
{sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:13.145-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:13.145-04:00 New_York, inScope, backgroundPoint}
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:149°F, designHotWaterPower:27MMBTU/h, designHotWaterFlow:3gal/min, designAirFlow:1000cfm}
{sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, inScope, backgroundPoint}
Bravo VAV 1-13 Discharge Air Flow Setpoint
{sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:07.473-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:07.598-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:10.87-04:00 New_York, inScope, backgroundPoint}
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:152°F, designHotWaterPower:4.5MMBTU/h, designHotWaterFlow:0.75gal/min, designAirFlow:250cfm}
{sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:09.879-04:00 New_York, inScope, backgroundPoint}
Bravo VAV 1-14 Discharge Air Flow Setpoint
{sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:10.995-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:07.721-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:10.249-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, inScope, backgroundPoint}
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:150°F, designHotWaterPower:6MMBTU/h, designHotWaterFlow:1gal/min, designAirFlow:400cfm}
{sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
Bravo VAV 1-15 Discharge Air Flow Setpoint
{sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:07.721-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, pointType:, inScope, backgroundPoint}
{sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:152°F, designHotWaterPower:4.1MMBTU/h, designHotWaterFlow:0.75gal/min, designAirFlow:300cfm}
{sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:10.497-04:00 New_York, inScope, backgroundPoint}
Bravo VAV 1-16 Discharge Air Flow Setpoint
{sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:10.249-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:07.598-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:10.249-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:10.249-04:00 New_York, inScope, backgroundPoint}
Bravo VAV 1-17 Discharge Air Flow Setpoint
{sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:11.258-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:10.497-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:13.145-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:07.721-04:00 New_York, inScope, backgroundPoint}
Bravo VAV 1-18 Discharge Air Flow Setpoint
{sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:10.126-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:10.126-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:150°F, designHotWaterPower:30.9MMBTU/h, designHotWaterFlow:1.45gal/min, designAirFlow:2400cfm}
{sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:09.879-04:00 New_York, inScope, backgroundPoint}
Bravo VAV 1-19 Discharge Air Flow Setpoint
{sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:09.627-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:11.258-04:00 New_York, inScope, backgroundPoint}
{predictionConf:0.6984488664169048, sourcePointName:Humidity, dataSyncRecovered:2020-07-10T01:00:10.87-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:10.87-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:09.627-04:00 New_York, inScope, backgroundPoint}
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:150°F, designHotWaterPower:17.5MMBTU/h, designHotWaterFlow:2gal/min, designAirFlow:500cfm}
{sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
Bravo VAV 1-2 Discharge Air Flow Setpoint
{sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, inScope, backgroundPoint}
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:151°F, designHotWaterPower:10.8MMBTU/h, designHotWaterFlow:0.28gal/min, designAirFlow:800cfm}
Bravo VAV 1-20 Discharge Air Flow Setpoint
{sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:13.145-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:10.87-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:09.879-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, inScope, backgroundPoint}
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:152°F, designHotWaterPower:83.5MMBTU/h, designHotWaterFlow:12gal/min, designAirFlow:3000cfm}
{sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:07.721-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:09.627-04:00 New_York, inScope, backgroundPoint}
Bravo VAV 1-3 Discharge Air Flow Setpoint
{sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:DisChgrHumid, dataSyncRecovered:2020-07-10T01:00:10.249-04:00 New_York, backgroundPoint}
{sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, inScope, backgroundPoint}
{predictionConf:0.7237593125289187, sourcePointName:SpaceHum, dataSyncRecovered:2020-07-10T01:00:10.249-04:00 New_York, inScope, backgroundPoint}
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:152°F, designHotWaterPower:3.8MMBTU/h, designHotWaterFlow:0.75gal/min, designAirFlow:300cfm}
Bravo VAV 1-4 Discharge Air Flow Setpoint
{sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:09.627-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:152°F, designHotWaterPower:10.5MMBTU/h, designHotWaterFlow:1.5gal/min, designAirFlow:450cfm}
{sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:10.995-04:00 New_York, inScope, backgroundPoint}
Bravo VAV 1-5 Discharge Air Flow Setpoint
{sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:10.249-04:00 New_York, inScope, backgroundPoint}
Bravo VAV 1-6 Discharge Air Flow Setpoint
{sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:10.745-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:10.995-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:DisChgrHumid, dataSyncRecovered:2020-07-10T01:00:07.598-04:00 New_York, backgroundPoint}
{sourcePointName:SpaceHum, dataSyncRecovered:2020-07-10T01:00:11.258-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:07.598-04:00 New_York, inScope, backgroundPoint}
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:152°F, designHotWaterPower:7.6MMBTU/h, designHotWaterFlow:1.25gal/min, designAirFlow:450cfm}
Bravo VAV 1-7 Discharge Air Flow Setpoint
{sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:10.87-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:10.995-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, inScope, backgroundPoint}
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:150°F, designHotWaterPower:4.8MMBTU/h, designHotWaterFlow:0.75gal/min, designAirFlow:300cfm}
Bravo VAV 1-8 Discharge Air Flow Setpoint
{sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:09.627-04:00 New_York, inScope, backgroundPoint}
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:149°F, designHotWaterPower:15.3MMBTU/h, designHotWaterFlow:1.75gal/min, designAirFlow:875cfm}
{sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:09.627-04:00 New_York, inScope, backgroundPoint}
Bravo VAV 1-9 Discharge Air Flow Setpoint
{sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:09.879-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:09.879-04:00 New_York, inScope, backgroundPoint}
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:149°F, designHotWaterPower:8.9MMBTU/h, designHotWaterFlow:1gal/min, designAirFlow:450cfm}
Bravo VAV 2-1 Discharge Air Flow Setpoint
{sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:10.995-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:10.497-04:00 New_York, inScope, backgroundPoint}
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:151°F, designHotWaterPower:4.3MMBTU/h, designHotWaterFlow:0.75gal/min, designAirFlow:175cfm}
{sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:10.995-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
Bravo VAV 2-10 Discharge Air Flow Setpoint
{sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:07.473-04:00 New_York, inScope, backgroundPoint}
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:149°F, designHotWaterPower:9.2MMBTU/h, designHotWaterFlow:1gal/min, designAirFlow:450cfm}
Bravo VAV 2-11 Discharge Air Flow Setpoint
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:152°F, designHotWaterPower:4.6MMBTU/h, designHotWaterFlow:0.75gal/min, designAirFlow:250cfm}
Bravo VAV 2-12 Discharge Air Flow Setpoint
{sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:10.497-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:09.627-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:10.126-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:07.473-04:00 New_York, inScope, backgroundPoint}
Bravo VAV 2-13 Discharge Air Flow Setpoint
{sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:10.126-04:00 New_York, inScope, backgroundPoint}
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:150°F, designHotWaterPower:24.2MMBTU/h, designHotWaterFlow:2.5gal/min, designAirFlow:1450cfm}
Bravo VAV 2-14 Discharge Air Flow Setpoint
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:149°F, designHotWaterPower:9.7MMBTU/h, designHotWaterFlow:1gal/min, designAirFlow:400cfm}
Bravo VAV 2-15 Discharge Air Flow Setpoint
{sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:07.721-04:00 New_York, inScope, backgroundPoint}
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:149°F, designHotWaterPower:9.2MMBTU/h, designHotWaterFlow:1gal/min, designAirFlow:400cfm}
Bravo VAV 2-16 Discharge Air Flow Setpoint
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:149°F, designHotWaterPower:8.9MMBTU/h, designHotWaterFlow:1gal/min, designAirFlow:400cfm}
{sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:11.125-04:00 New_York, inScope, backgroundPoint}
Bravo VAV 2-17 Discharge Air Flow Setpoint
{sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:09.879-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:07.721-04:00 New_York, inScope, backgroundPoint}
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:152°F, designHotWaterPower:15MMBTU/h, designHotWaterFlow:1.75gal/min, designAirFlow:550cfm}
Bravo VAV 2-18 Discharge Air Flow Setpoint
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:153°F, designHotWaterPower:6.2MMBTU/h, designHotWaterFlow:0.75gal/min, designAirFlow:350cfm}
{sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:11.258-04:00 New_York, inScope, backgroundPoint}
Bravo VAV 2-19 Discharge Air Flow Setpoint
{sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, inScope, backgroundPoint}
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:153°F, designHotWaterPower:9.6MMBTU/h, designHotWaterFlow:1.25gal/min, designAirFlow:650cfm}
{sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:10.497-04:00 New_York, inScope, backgroundPoint}
Bravo VAV 2-2 Discharge Air Flow Setpoint
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:152°F, designHotWaterPower:10.8MMBTU/h, designHotWaterFlow:1.25gal/min, designAirFlow:650cfm}
Bravo VAV 2-20 Discharge Air Flow Setpoint
{sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:10.249-04:00 New_York, inScope, backgroundPoint}
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:153°F, designHotWaterPower:10.4MMBTU/h, designHotWaterFlow:1.25gal/min, designAirFlow:650cfm}
{sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, inScope, backgroundPoint}
Bravo VAV 2-21 Discharge Air Flow Setpoint
Bravo VAV 2-22 Discharge Air Flow Setpoint
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:148°F, designHotWaterPower:6.2MMBTU/h, designHotWaterFlow:0.75gal/min, designAirFlow:350cfm}
Bravo VAV 2-23 Discharge Air Flow Setpoint
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:150°F, designHotWaterPower:15.4MMBTU/h, designHotWaterFlow:2.5gal/min, designAirFlow:1600cfm}
Bravo VAV 2-24 Discharge Air Flow Setpoint
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:153°F, designHotWaterPower:4.4MMBTU/h, designHotWaterFlow:0.75gal/min, designAirFlow:250cfm}
Bravo VAV 2-25 Discharge Air Flow Setpoint
{sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:10.995-04:00 New_York, inScope, backgroundPoint}
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:148°F, designHotWaterPower:4.2MMBTU/h, designHotWaterFlow:0.5gal/min, designAirFlow:300cfm}
Bravo VAV 2-26 Discharge Air Flow Setpoint
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:148°F, designHotWaterPower:18.6MMBTU/h, designHotWaterFlow:2gal/min, designAirFlow:1125cfm}
{sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:10.87-04:00 New_York, inScope, backgroundPoint}
Bravo VAV 2-27 Discharge Air Flow Setpoint
{sourcePointName:STAT_SETPOINT, dataSyncRecovered:2020-07-10T01:00:07.721-04:00 New_York, inScope, backgroundPoint}
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:149°F, designHotWaterPower:9.5MMBTU/h, designHotWaterFlow:1gal/min, designAirFlow:500cfm}
Bravo VAV 2-28 Discharge Air Flow Setpoint
{sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:10.497-04:00 New_York, inScope, backgroundPoint}
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:149°F, designHotWaterPower:9.8MMBTU/h, designHotWaterFlow:1gal/min, designAirFlow:500cfm}
Bravo VAV 2-29 Discharge Air Flow Setpoint
Bravo VAV 2-3 Discharge Air Flow Setpoint
{sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:11.258-04:00 New_York, inScope, backgroundPoint}
{sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:11.125-04:00 New_York, inScope, backgroundPoint}
Bravo VAV 2-30 Discharge Air Flow Setpoint
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:153°F, designHotWaterPower:18.6MMBTU/h, designHotWaterFlow:2gal/min, designAirFlow:650cfm}
Bravo VAV 2-31 Discharge Air Flow Setpoint
{sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:11.125-04:00 New_York, inScope, backgroundPoint}
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:149°F, designHotWaterPower:28.6MMBTU/h, designHotWaterFlow:3.5gal/min, designAirFlow:2150cfm}
{sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, inScope, backgroundPoint}
Bravo VAV 2-32 Discharge Air Flow Setpoint
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:148°F, designHotWaterPower:3.1MMBTU/h, designHotWaterFlow:0.5gal/min, designAirFlow:200cfm}
Bravo VAV 2-33 Discharge Air Flow Setpoint
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:149°F, designHotWaterPower:10.3MMBTU/h, designHotWaterFlow:1gal/min, designAirFlow:575cfm}
{sourcePointName:BOX_FLOW, dataSyncRecovered:2020-07-10T01:00:07.598-04:00 New_York, inScope, backgroundPoint}
Bravo VAV 2-34 Discharge Air Flow Setpoint
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:148°F, designHotWaterPower:3.1MMBTU/h, designHotWaterFlow:0.5gal/min, designAirFlow:250cfm}
Bravo VAV 2-35 Discharge Air Flow Setpoint
{sourcePointName:SPACE_TEMP, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, inScope, backgroundPoint}
Bravo VAV 2-36 Discharge Air Flow Setpoint
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:150°F, designHotWaterPower:10.5MMBTU/h, designHotWaterFlow:1.25gal/min, designAirFlow:500cfm}
Bravo VAV 2-37 Discharge Air Flow Setpoint
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:148°F, designHotWaterPower:4.9MMBTU/h, designHotWaterFlow:0.5gal/min, designAirFlow:250cfm}
Bravo VAV 2-38 Discharge Air Flow Setpoint
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:153°F, designHotWaterPower:9.5MMBTU/h, designHotWaterFlow:9.5gal/min, designAirFlow:475cfm}
Bravo VAV 2-39 Discharge Air Flow Setpoint
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:151°F, designHotWaterPower:2.9MMBTU/h, designHotWaterFlow:0.5gal/min, designAirFlow:150cfm}
Bravo VAV 2-4 Discharge Air Flow Setpoint
{sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:09.879-04:00 New_York, inScope, backgroundPoint}
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:153°F, designHotWaterPower:9.8MMBTU/h, designHotWaterFlow:1.25gal/min, designAirFlow:475cfm}
Bravo VAV 2-40 Discharge Air Flow Setpoint
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:153°F, designHotWaterPower:9.5MMBTU/h, designHotWaterFlow:1.25gal/min, designAirFlow:475cfm}
{sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:09.626-04:00 New_York, inScope, backgroundPoint}
Bravo VAV 2-41 Discharge Air Flow Setpoint
Bravo VAV 2-42 Discharge Air Flow Setpoint
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:141°F, designHotWaterPower:4.7MMBTU/h, designHotWaterFlow:0.75gal/min, designAirFlow:350cfm}
Bravo VAV 2-43 Discharge Air Flow Setpoint
{sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:07.473-04:00 New_York, inScope, backgroundPoint}
Bravo VAV 2-44 Discharge Air Flow Setpoint
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:150°F, designHotWaterPower:17.8MMBTU/h, designHotWaterFlow:1.75gal/min, designAirFlow:600cfm}
Bravo VAV 2-45 Discharge Air Flow Setpoint
Bravo VAV 2-46 Discharge Air Flow Setpoint
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:149°F, designHotWaterPower:25.9MMBTU/h, designHotWaterFlow:2.5gal/min, designAirFlow:1400cfm}
Bravo VAV 2-47 Discharge Air Flow Setpoint
Bravo VAV 2-48 Discharge Air Flow Setpoint
Bravo VAV 2-49 Discharge Air Flow Setpoint
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:151°F, designHotWaterPower:3.1MMBTU/h, designHotWaterFlow:0.5gal/min, designAirFlow:200cfm}
Bravo VAV 2-5 Discharge Air Flow Setpoint
Bravo VAV 2-50 Discharge Air Flow Setpoint
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:148°F, designHotWaterPower:4.7MMBTU/h, designHotWaterFlow:0.5gal/min, designAirFlow:350cfm}
Bravo VAV 2-6 Discharge Air Flow Setpoint
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:152°F, designHotWaterPower:10MMBTU/h, designHotWaterFlow:1.25gal/min, designAirFlow:650cfm}
Bravo VAV 2-7 Discharge Air Flow Setpoint
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:153°F, designHotWaterPower:4.1MMBTU/h, designHotWaterFlow:0.75gal/min, designAirFlow:300cfm}
Bravo VAV 2-8 Discharge Air Flow Setpoint
{sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:07.598-04:00 New_York, pointType:, inScope, backgroundPoint}
Bravo VAV 2-9 Discharge Air Flow Setpoint
{sourcePointName:Htg, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, inScope, backgroundPoint}
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:150°F, designHotWaterPower:14.1MMBTU/h, designHotWaterFlow:2.5gal/min, designAirFlow:1300cfm}
{sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-14T01:00:05.167-04:00 New_York, pointType:, inScope, backgroundPoint}
Bravo VAV 3-1 Discharge Air Flow Setpoint
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:151°F, designHotWaterPower:7.3MMBTU/h, designHotWaterFlow:0.75gal/min, designAirFlow:350cfm}
Bravo VAV 3-10 Discharge Air Flow Setpoint
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:150°F, designHotWaterPower:22.7MMBTU/h, designHotWaterFlow:2.25gal/min, designAirFlow:1100cfm}
Bravo VAV 3-11 Discharge Air Flow Setpoint
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:149°F, designHotWaterPower:9.8MMBTU/h, designHotWaterFlow:1.5gal/min, designAirFlow:1000cfm}
Bravo VAV 3-12 Discharge Air Flow Setpoint
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:151°F, designHotWaterPower:5.3MMBTU/h, designHotWaterFlow:0.75gal/min, designAirFlow:350cfm}
Bravo VAV 3-13 Discharge Air Flow Setpoint
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:149°F, designHotWaterPower:5.4MMBTU/h, designHotWaterFlow:1gal/min, designAirFlow:500cfm}
Bravo VAV 3-14 Discharge Air Flow Setpoint
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:147°F, designHotWaterPower:2.7MMBTU/h, designHotWaterFlow:0.5gal/min, designAirFlow:250cfm}
Bravo VAV 3-15 Discharge Air Flow Setpoint
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:153°F, designHotWaterPower:3.3MMBTU/h, designHotWaterFlow:0.75gal/min, designAirFlow:300cfm}
Bravo VAV 3-16 Discharge Air Flow Setpoint
Bravo VAV 3-17 Discharge Air Flow Setpoint
{sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:07.598-04:00 New_York, inScope, backgroundPoint}
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:150°F, designHotWaterPower:12.4MMBTU/h, designHotWaterFlow:1.5gal/min, designAirFlow:500cfm}
Bravo VAV 3-18 Discharge Air Flow Setpoint
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:155°F, designHotWaterPower:2.1MMBTU/h, designHotWaterFlow:0.5gal/min, designAirFlow:150cfm}
Bravo VAV 3-19 Discharge Air Flow Setpoint
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:149°F, designHotWaterPower:8.7MMBTU/h, designHotWaterFlow:1.5gal/min, designAirFlow:800cfm}
Bravo VAV 3-2 Discharge Air Flow Setpoint
Bravo VAV 3-20 Discharge Air Flow Setpoint
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:153°F, designHotWaterPower:6.5MMBTU/h, designHotWaterFlow:1gal/min, designAirFlow:300cfm}
Bravo VAV 3-21 Discharge Air Flow Setpoint
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:151°F, designHotWaterPower:29.2MMBTU/h, designHotWaterFlow:3.5gal/min, designAirFlow:1250cfm}
Bravo VAV 3-22 Discharge Air Flow Setpoint
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:151°F, designHotWaterPower:2.2MMBTU/h, designHotWaterFlow:0.5gal/min, designAirFlow:200cfm}
{sourcePointName:DAMPER_CMD, dataSyncRecovered:2020-07-10T01:00:10.62-04:00 New_York, pointType:, inScope, backgroundPoint}
Bravo VAV 3-23 Discharge Air Flow Setpoint
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:153°F, designHotWaterPower:6.4MMBTU/h, designHotWaterFlow:0.75gal/min, designAirFlow:300cfm}
Bravo VAV 3-24 Discharge Air Flow Setpoint
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:149°F, designHotWaterPower:16.6MMBTU/h, designHotWaterFlow:2gal/min, designAirFlow:500cfm}
Bravo VAV 3-25 Discharge Air Flow Setpoint
{sourcePointName:FLOW_STPT, dataSyncRecovered:2020-07-10T01:00:11.125-04:00 New_York, inScope, backgroundPoint}
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:152°F, designHotWaterPower:12.9MMBTU/h, designHotWaterFlow:1.5gal/min, designAirFlow:400cfm}
Bravo VAV 3-26 Discharge Air Flow Setpoint
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:153°F, designHotWaterPower:6MMBTU/h, designHotWaterFlow:0.75gal/min, designAirFlow:300cfm}
Bravo VAV 3-27 Discharge Air Flow Setpoint
{sourcePointName:DisAirTemp, dataSyncRecovered:2020-07-10T01:00:09.879-04:00 New_York, pointType:, inScope, backgroundPoint}
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:151°F, designHotWaterPower:3MMBTU/h, designHotWaterFlow:0.5gal/min, designAirFlow:200cfm}
Bravo VAV 3-28 Discharge Air Flow Setpoint
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:150°F, designHotWaterPower:4.2MMBTU/h, designHotWaterFlow:0.75gal/min, designAirFlow:375cfm}
{dateCreated:2020-04-03, dataSyncRecovered:2020-07-10T01:00:09.752-04:00 New_York, backgroundPoint}
{dateCreated:2020-04-03, dataSyncRecovered:2020-07-10T01:00:10.374-04:00 New_York, backgroundPoint}
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:155°F, designHotWaterPower:1.7MMBTU/h, designHotWaterFlow:0.5gal/min, designAirFlow:150cfm}
{dateCreated:2020-04-03, dataSyncRecovered:2020-07-10T01:00:10.87-04:00 New_York, backgroundPoint}
{dateCreated:2020-04-03, dataSyncRecovered:2020-07-10T01:00:07.721-04:00 New_York, backgroundPoint}
{dateCreated:2020-04-03, dataSyncRecovered:2020-07-10T01:00:11.125-04:00 New_York, backgroundPoint}
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:152°F, designHotWaterPower:6.5MMBTU/h, designHotWaterFlow:1.25gal/min, designAirFlow:600cfm}
{dateCreated:2020-04-03, dataSyncRecovered:2020-07-10T01:00:10.003-04:00 New_York, backgroundPoint}
{dateCreated:2020-04-03, dataSyncRecovered:2020-07-10T01:00:07.598-04:00 New_York, backgroundPoint}
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:150°F, designHotWaterPower:7.6MMBTU/h, designHotWaterFlow:1.25gal/min, designAirFlow:700cfm}
{dateCreated:2020-04-03, dataSyncRecovered:2020-07-10T01:00:10.249-04:00 New_York, backgroundPoint}
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:153°F, designHotWaterPower:6.5MMBTU/h, designHotWaterFlow:0.75gal/min, designAirFlow:300cfm}
{tu, designSource:Drawings, designHotWaterEnteringTemp:180°F, designHotWaterLeavingTemp:151°F, designHotWaterPower:23MMBTU/h, designHotWaterFlow:4gal/min, designAirFlow:2000cfm}
{dateCreated:2020-04-03, dataSyncRecovered:2020-07-10T01:00:09.879-04:00 New_York, backgroundPoint}
{dateCreated:2020-04-03, dataSyncRecovered:2020-07-10T01:00:10.126-04:00 New_York, backgroundPoint}
{diagnostics, dataSync, dataSyncRecovered:2020-07-14T01:00:05.167-04:00 New_York, backgroundPoint}